ISRN Renewable EnergyVolume 2011 (2011), Article ID 484893, 11 pagesdoi:10.5402/2011/484893

Research Article

Suitable Glazing Selection for Glass-Curtain Walls in Tropical Climates of India

M. C. Singh and S. N. Garg

Centre for Energy Studies, Indian Institute of Technology (Hauz Khas), New Delhi 110016, India

Received 24 June 2011; Accepted 21 July 2011

Academic Editors: H. Boyer and G. Li

Copyright © 2011 M. C. Singh and S. N. Garg. This is an open access article distributed under the Creative Commons Attribution License, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.

Abstract.

How a glass-curtain wall affects the heating and cooling load of a building is analysed. The study includes five types of glazings, which include double-glazed clear glass, double-glazed low-e, and double-glazed solar control. The analysis is for three climates: composite (New Delhi), hot and dry (Jodhpur), and warm and humid (Chennai). An office building is chosen for analysis. The study includes effect of glazed area, orientation, and that of climates, on annual energy consumption. It was found that energy consumption increases linearly with the glazed area and minimum energy consumption is for north orientation. For types of climates considered in this study, a glass-curtain wall, made of solar control glazing (reflective), consumes 6–8% less energy than the standard window.

1. Introduction

In Indian metropolitan cities, a new trend in building construction is coming up: having front façade completely glazed. Mainly, it is from aesthetic point of view, although large glazed area provides more natural light and thereby reduces artificial light requirement. A façade, having 90% of glazed area and 10% of frame area, is usually called a glass-curtain wall. Bouden [1] has analysed impact of glass-curtain walls on energy consumption for an office building in Tunisian climate. Seven different glass curtain walls, in four different orientations, with five different percentages of glazed areas ranging from 20% to 90%, have been analysed. He has found that a glass-curtain wall made of one clear glass and other reflecting glass shows lower energy consumption as compared to a standard size window (20% of area, single glazed clear glass). Bansal et al. [2] have determined glazed area, enough to keep a building thermally comfortable for 3 winter climates of India. They have assumed direct gain through the glazed area absorbed by the building parts as follows: 60% of the radiation by the floor and 8% by the ceiling and each of the four walls. It has been found that for an uninsulated building (no insulation in walls/roof), 30% glazed area of south wall is sufficient for Delhi’s composite climate. For insulated buildings, optimum glazed areas are: 10%, 20%, and 30% for New Delhi, Srinagar, and Leh, respectively. Hamdani and Ahmad [3] have analysed the effect of window parameters on inside temperature of the building for climate of Baghdad in Iraq. Saridar and Elkadi [4] have analysed the effect of different window configurations on daylighting energy consumption in an office building at Beirut. A school building has been analysed in terms of energy consumption in Israel by [5], and it was found that the energy consumption can be reduced up to 50% for high-performance school building. Johnson et al. [6, 7] have studied the annual energy consumption in an office building by using the different types of windows for different climates of USA. Energy performance of a building is influenced by the window size and its orientation [8, 9]. Energy efficient glazings reduce the heating and cooling load of the buildings, allow natural daylight [10, 11], and provide human thermal comfort [12]. The heating demands of the buildings can be reduced by using the low-e windows and insulation on walls and roof. Those buildings which have high internal gains and relatively large-glazed façade in south show the lower demands of heating. Similarly, the cooling load of the buildings can be reduced by using the solar control windows, and the requisite orientation in which it is minimum can be found [13, 14].

In India, large numbers of office buildings are constructed with front façade completely glazed. How glass-curtain wall affects heating/cooling load of a building is not known. In this work, the analysis has been carried out for a well-insulated office building. Effect of climatic conditions, glazings types, glazed areas, and orientations on annual energy consumption has been analysed.

2. Input Data

Ten-year weather data (1991–2000) which include monthly mean hourly values of global solar radiation, diffuse solar radiation, relative humidity, and ambient temperature has been procured from India Meteorological Department (IMD), Pune, and this measured data conforms to international standards. IMD Pune acts as the regional radiation center for Asia and maintains the international standards for measurement of surface climate data.

A well-insulated office building with dimensions of 12 m × 8 m × 3 m has been investigated. The insulation specifications are taken as per Energy Conservation Building Code of India (ECBC-2006) [15]: U-values of its walls and roof are 0.352 W/m²K and 0.409 W/m²K, respectively. Walls have been constructed with 220 mm of brick with 13 mm of cement plaster on both sides. Roof has13 mm of cement plaster as innermost surface, 100 mm of RCC (Reinforced Cement Concrete), 75 mm of mudphuska (a mixture of soil and rice husk), and 25 mm of broken tiles as the outermost surface. Insulation layer of expended polystyrene has been provided on both walls as well as roof, immediately after the innermost layer of plaster (82 mm for walls and 70 mm for roof). Details of walls and roof construction are shown in Figure 1. Thermal properties of building materials have been taken as per Bureau of Indian standards (BIS) [16]. Working schedule has been assumed from 8 am to 6 pm, with Sunday as holiday. Internal gains from occupants, lighting, and appliances during working hours taken are: person 65 W; computer with monitor 140 W; lighting density 10.8 W/m² [15]. The temperature has been controlled at 20°C in winter and 25°C in summer during working periods and at 18°C and 30°C, respectively, at other times. The ventilation rate considered is 1 ACH (air changes per hour) during the working hours and 0.5 ACH at other times. This study includes three climatic conditions of India: composite (New Delhi, 28°35'N, 77°12'E), hot and dry (Jodhpur, 26°18'N, 73°01'E), and warm and humid (Chennai, 13°00'N, 80°11'E). The climatic data of these locations is shown in Figure 2. It includes monthly mean values of global radiation on horizontal surface, ambient air temperature, relative humidity, and wind speed. In most part of India (except few places at high altitudes), winter is mild and exists for two months only (December and January) and mild heating is required. For air-conditioned buildings, cooling is required for about 8 months, March to October. So this study is mainly from cooling point of view. The emphasis is on the selection of glazing types and their optimum orientation, from cooling point of view. New types of glass and coating are coming up in the market. With the increasing glazed area, the cooling load, in summer, always increases. In winter, it may lead to overheating which necessitates cooling.

(a)

(b)

Figure 1: Construction details of (a) walls and (b) roof.

(a)

(b)

(c)

(d)

Figure 2: Climatic data (monthly mean values) for three stations, (a) solar radiation, (b) ambient temperature, (c) relative humidity, and (d) wind speed.

3. Methodology

Energy performance of the building has been investigated by using TRNSYS 16 [17]. TRNSYS Type 56 is a transient simulation module used for thermal analysis of buildings. The TRNSYS project model has three main features: weather data reader, solar radiation processor, and TRNBuild. Weather data reader reads the data from standard file format such as TMY2 (Typical Meteorological Year version-2) and then links it with the radiation processor. The solar radiation processor calculates the radiation on inclined surfaces. In TRNBuild, user can create input data for buildings. This data includes building envelope details such as walls, roof, floor, window, and operational behavior of the building such as heating and cooling schedules. Building has been treated as an isolated single zone. Hourly simulations have been conducted over one year period, for each of the 3 locations. This study includes five different types of windows (including low-e and solar control), six different glazed areas ranging from 20% to 90% (expressed as percentage of wall area). Table 1 describes the important properties of these five different glazings. Energy performance of each glazing has been analysed for four different orientations. Energy consumption of glass-curtain walls have been compared to an opaque wall with conventional glazed area (20%, double glazed clear glass window).

Table 1: Different kinds of glass-curtain walls used in this study. The values of both U and g have been computed by WINDOW 5.0.

S. no.
Glazing type
Description
Identity
U (W/m²K )
SHGC* (g-value)

1
Double glazed, clear glass window
6 mm clear glass + 12 mm air space + 6 mm clear glass
Clear-clear
2.95
0.73

2
Double glazed, low-e window
6 mm low-e glass + 12 mm air space + 6 mm clear glass
Low-e1-clear
1.80
0.68

3
Double glazed, low-e window
6 mm low-e glass + 12 mm air space+ 6 mm clear glass
Low-e2-clear
1.74
0.54

4
Double glazed, solar control (absorptive) window
6 mm solar control (absorptive) glass + 12 mm air space + 6 mm clear glass
Solar control-abs
2.80
0.24

5
Double glazed, solar control (reflective) window
6 mm solar control (reflective) glass + 12 mm air space + 6 mm clear glass
Solar control-ref
1.95
0.10

*Solar heat gain coefficient.

4. Results and Discussion

The analysis has been carried out for each of the five types of glazings, by taking the effect of glazed area, orientation, and climate on annual cooling and heating load.

4.1. Effect of Glazed Area

Effect of glazed area on building’s cooling and heating load for all types of glazings and for all orientations is shown in Table 2(a) for Delhi, Table 2(b) for Jodhpur, and Table 2(c) for Chennai. These three tables are exhaustive in the sense that all the details are shown here. Results are shown in unit floor area.

Table 2: Effect of glazed area on annual heating/cooling load (kWh/m²yr) of a building. (a) Delhi. (b) Jodhpur. (c) Chennai.

(a)

Glazed area (%)
Clear-clear
Low-e1-clear
Low-e2-clear
Sol.control-abs
Sol.control-ref

Heatingload
Coolingload
Totalload
Heatingload
Coolingload
Totalload
Heatingload
Coolingload
Totalload
Heating load
Cooling load
Totalload
Heatingload
Coolingload
Totalload

North

20
2.3
95.7
98.0
1.9
94.7
96.6
2.1
91.3
93.4
3.0
86.0
89.0
2.8
81.9
84.7

35
2.2
108.2
110.4
1.6
107.2
108.8
1.9
100.3
102.2
3.3
90.5
93.8
3.2
84.8
88.0

50
2.4
119.6
122.0
1.5
117.1
118.6
1.8
109.1
110.9
3.9
94.9
98.8
3.6
86.4
90.0

65
2.4
132.2
134.6
1.3
130.1
131.4
1.7
118.4
120.1
4.3
101.2
105.5
3.9
89.5
93.4

80
2.6
143.3
145.9
1.3
140.6
141.9
1.7
125.6
127.3
5.0
105.2
110.2
4.3
90.7
95.0

90
2.7
150.8
153.5
1.2
148.0
149.2
1.7
131.3
133.0
5.2
108.7
113.9
4.5
92.6
97.1

South

20
0.3
106.2
106.5
0.3
104.0
104.3
0.5
97.2
97.7
1.7
88.6
90.3
2.3
82.9
85.2

35
0.1
129.3
129.4
0.1
126.8
126.9
0.1
114.0
114.1
1.3
95.7
97.0
2.2
86.1
88.3

50
0.0
153.3
153.3
0.0
150.6
150.6
0.1
130.6
130.7
1.1
102.7
103.8
2.1
88.4
90.5

65
0.0
180.0
180.0
0.0
176.3
176.3
0.0
150.3
150.3
1.0
111.0
112.0
2.0
92.4
94.4

80
0.0
203.0
203.0
0.0
200.5
200.5
0.0
167.6
167.6
1.0
118.9
119.9
2.0
95.2
97.2

90
0.0
218.9
218.9
0.0
217.1
217.1
0.0
180.2
180.2
1.0
124.8
125.8
2.0
98.0
100.0

East

20
1.3
98.5
99.8
1.2
96.7
97.9
1.5
92.4
93.9
2.4
85.6
88.0
2.6
81.8
84.4

35
0.8
112.9
113.7
0.7
110.8
111.5
1.0
103.0
104.0
2.3
90.9
93.2
2.7
84.1
86.8

50
0.6
128.1
128.7
0.4
125.0
125.4
0.7
113.2
113.9
2.3
95.8
98.1
2.8
85.7
88.5

65
0.5
142.1
142.6
0.3
138.9
139.2
0.5
124.1
124.6
2.2
101.2
103.4
2.9
88.0
90.9

80
0.4
157.1
157.5
0.2
154.2
154.4
0.4
135.7
136.1
2.2
106.9
109.1
2.8
91.0
93.8

90
0.4
167.4
167.8
0.2
163.0
163.2
0.3
142.1
142.4
2.3
109.9
112.2
3.0
91.9
94.9

West

20
1.6
97.2
98.8
1.5
95.9
97.4
1.7
91.9
93.6
2.6
85.2
87.8
2.7
81.7
84.4

35
1.2
110.9
112.1
1.0
109.4
110.4
1.3
101.5
102.8
2.6
90.5
93.1
2.9
84.1
87.0

50
0.9
124.9
125.8
0.7
123.0
123.7
1.0
112.2
113.2
2.7
95.0
97.7
3.0
86.0
89.0

65
0.8
138.9
139.7
0.5
136.1
136.6
0.8
122.2
123.0
2.8
101.0
103.8
3.1
88.5
91.6

80
0.7
153.8
154.5
0.4
151.4
151.8
0.6
133.3
133.9
2.8
106.7
109.5
3.2
90.8
94.0

90
0.6
163.1
163.7
0.3
160.2
160.5
0.6
139.6
140.2
2.9
109.9
112.8
3.3
91.8
95.1

(b)

Glazed area (%)
Clear-clear
Low-e1-clear
Low-e2-clear
Sol.control-abs
Sol.control-ref

Heatingload
Cooling load
Totalload
Heatingload
Coolingload
Totalload
Heatingload
Coolingload
Totalload
Heating load
Cooling load
Total load
Heating load
Cooling load
Totalload

North

20
0.3
105.2
105.5
0.2
104.5
104.7
0.3
100.3
100.6
0.5
95.1
95.6
0.5
90.7
91.2

35
0.3
118.2
118.5
0.2
117.6
117.8
0.2
110.1
110.3
0.7
99.5
100.2
0.6
92.8
93.4

50
0.4
131.3
131.7
0.2
128.7
128.9
0.2
118.8
119.0
0.9
104.6
105.5
0.8
94.8
95.6

65
0.4
143.8
144.2
0.1
142.3
142.4
0.2
129.1
129.3
1.0
110.4
111.4
0.8
97.8
98.6

80
0.4
156.7
157.1
0.1
153.2
153.3
0.2
137.8
138.0
1.3
115.5
116.8
1.0
99.9
100.9

90
0.5
164.1
164.6
0.1
162.1
162.2
0.2
143.6
143.8
1.4
119.0
120.4
1.1
101.5
102.6

South

20
0.0
118.9
118.9
0.0
116.8
116.8
0.0
109.0
109.1
0.2
97.9
98.1
0.3
91.8
92.1

35
0.0
146.3
146.3
0.0
143.0
143.0
0.0
128.3
128.3
0.1
106.5
106.6
0.3
95.1
95.4

50
0.0
173.3
173.3
0.0
168.9
168.9
0.0
147.6
147.6
0.1
114.3
114.4
0.3
98.1
98.4

65
0.0
200.1
200.1
0.0
196.6
196.6
0.0
168.0
168.0
0.0
124.9
124.9
0.2
102.7
102.9

80
0.0
225.0
225.0
0.0
222.1
222.1
0.0
187.5
187.5
0.0
134.0
134.0
0.2
105.4
105.6

90
0.0
242.7
242.7
0.0
239.8
239.8
0.0
200.8
200.8
0.0
140.6
140.6
0.2
108.6
108.8

East

20
0.1
108.8
108.9
0.1
106.7
106.8
0.1
102.2
102.3
0.3
94.7
95.0
0.4
90.1
90.5

35
0.0
124.9
124.9
0.0
122.4
122.4
0.0
113.7
113.8
0.3
100.2
100.5
0.4
92.5
92.9

50
0.0
141.2
141.2
0.0
138.1
138.1
0.0
125.5
125.6
0.2
105.4
105.6
0.4
94.8
95.2

65
0.0
158.1
158.1
0.0
154.1
154.1
0.0
138.0
138.0
0.2
111.4
111.6
0.4
97.1
97.5

80
0.0
175.9
175.9
0.0
172.2
172.2
0.0
151.2
151.2
0.2
118.1
118.3
0.4
100.2
100.6

90
0.0
185.3
185.3
0.0
181.9
181.9
0.0
158.4
158.4
0.2
121.2
121.4
0.4
101.3
101.7

West

20
0.2
108.2
108.4
0.2
106.6
106.8
0.2
102.2
102.4
0.4
95.5
95.9
0.5
90.4
90.9

35
0.1
125.1
125.2
0.1
122.3
122.4
0.2
113.9
114.1
0.4
100.1
100.5
0.5
92.9
93.4

50
0.1
141.0
141.1
0.1
137.8
137.9
0.1
126.2
126.3
0.5
105.3
105.8
0.6
95.9
96.5

65
0.1
158.9
159.0
0.1
155.0
155.1
0.1
138.0
138.1
0.5
111.7
112.2
0.6
98.3
98.9

80
0.1
176.1
176.2
0.0
171.6
171.6
0.1
150.9
151.0
0.5
118.8
119.3
0.6
101.4
102.0

90
0.1
186.4
186.5
0.0
181.7
181.7
0.1
160.3
160.4
0.5
122.5
123.0
0.7
102.2
102.9

(c)

Glazed area (%)
Clear-clear
Low-e1-clear
Low-e2-clear
Sol.control-abs
Sol.control-ref

Heatingload
Coolingload
Totalload
Heatingload
Coolingload
Total load
Heating load
Cooling load
Totalload
Heating load
Cooling load
Totalload
Heating load
Cooling load
Total load

North

20
0.0
124.7
124.7
0.0
123.3
123.3
0.0
118.4
118.4
0.0
111.2
111.2
0.0
106.4
106.4

35
0.0
140.8
140.8
0.0
138.1
138.1
0.0
129.8
129.8
0.0
117.5
117.5
0.0
109.2
109.2

50
0.0
155.6
155.6
0.0
152.1
152.1
0.0
140.4
140.4
0.0
122.8
122.8
0.0
111.0
111.0

65
0.0
172.0
172.0
0.0
168.2
168.2
0.0
152.8
152.8
0.0
130.2
130.2
0.0
115.1
115.1

80
0.0
185.1
185.1
0.0
181.3
181.3
0.0
162.7
162.7
0.0
135.8
135.8
0.0
117.0
117.0

90
0.0
195.0
195.0
0.0
191.1
191.1
0.0
170.1
170.1
0.0
140.2
140.2
0.0
119.4
119.4

South

20
0.0
132.5
132.5
0.0
130.3
130.3
0.0
123.9
123.9
0.0
114.1
114.1
0.0
107.3
107.3

35
0.0
154.4
154.4
0.0
151.0
151.0
0.0
139.6
139.6
0.0
122.2
122.2
0.0
110.9
110.9

50
0.0
175.3
175.3
0.0
171.3
171.3
0.0
154.3
154.3
0.0
129.5
129.5
0.0
114.0
114.0

65
0.0
198.1
198.1
0.0
193.4
193.4
0.0
171.2
171.2
0.0
139.3
139.3
0.0
118.8
118.8

80
0.0
217.3
217.3
0.0
212.5
212.5
0.0
185.7
185.7
0.0
146.6
146.6
0.0
121.5
121.5

90
0.0
230.8
230.8
0.0
226.3
226.3
0.0
196.2
196.2
0.0
152.4
152.4
0.0
124.5
124.5

East

20
0.0
124.9
124.9
0.0
123.0
123.0
0.0
118.1
118.1
0.0
110.5
110.5
0.0
105.8
105.8

35
0.0
141.0
141.0
0.0
138.5
138.5
0.0
130.0
130.0
0.0
116.3
116.3
0.0
108.2
108.2

50
0.0
157.3
157.3
0.0
153.6
153.6
0.0
141.5
141.5
0.0
122.2
122.2
0.0
110.3
110.3

65
0.0
173.6
173.6
0.0
169.6
169.6
0.0
153.6
153.6
0.0
127.9
127.9
0.0
113.0
113.0

80
0.0
190.7
190.7
0.0
186.4
186.4
0.0
166.1
166.1
0.0
134.9
134.9
0.0
116.5
116.5

90
0.0
200.5
200.5
0.0
195.9
195.9
0.0
173.7
173.7
0.0
138.3
138.3
0.0
117.5
117.5

West

20
0.0
125.0
125.0
0.0
123.5
123.5
0.0
118.6
118.6
0.0
110.7
110.7
0.0
105.9
105.9

35
0.0
141.9
141.9
0.0
139.3
139.3
0.0
130.8
130.8
0.0
116.8
116.8
0.0
108.7
108.7

50
0.0
158.2
158.2
0.0
154.4
154.4
0.0
142.4
142.4
0.0
122.8
122.8
0.0
110.8
110.8

65
0.0
174.6
174.6
0.0
170.3
170.3
0.0
154.6
154.6
0.0
128.9
128.9
0.0
113.7
113.7

80
0.0
191.8
191.8
0.0
187.0
187.0
0.0
167.2
167.2
0.0
136.5
136.5
0.0
117.2
117.2

90
0.0
202.0
202.0
0.0
197.2
197.2
0.0
174.6
174.6
0.0
140.3
140.3
0.0
118.6
118.6

4.2. Delhi

Table 2(a) shows that as glazed area increases, the energy consumption also increases, and this is already a well-known fact. In what proportion the energy consumption increases with the glazed area depends upon building type, glazing type, glazing orientation, and climate type, and this is the subject matter of the present study. For this station and for south orientation, the results are shown in graphical form in Figure 3(a). This figure shows that energy consumption varies almost linearly with the glazed area (a straight line can be passed through tops of the bars for the same glazing). For 10% increment in glazed area, the corresponding increase in energy consumption is 15.3 kWh/m²yr for clear-clear glazing, 15.1 kWh/m²yr for low-e1-clear glazing, 10.9 kWh/m²yr for low-e2-clear glazing, 4.5 kWh/m²yr for solar control (absorptive), and 2.1 kWh/m²yr for solar control (reflective) glazing. The highest increment in energy consumption is for clear-clear glazing, and the lowest increment is for solar control (reflective) glazing.

(a)

(b)

(c)

Figure 3: Effect of glazed area on annual energy consumption. Five types of glazings are considered.

4.3. Jodhpur

Results for this station are shown in Table 2(b) and Figure 3(b). Here, for 10% increase in glazed area, the corresponding increase in annual energy consumption is 18.3 kWh/m²yr for clear-clear glazing, 17.5 kWh/m²yr for low-e1-clear glazing, 12.8 kWh/m²yr for low-e2-clear glazing, 5.7 kWh/m²yr for solar control (absorptive) glazing, and 2.2 kWh/m²yr for solar control (reflective) glazing.

4.4. Chennai

Table 2(c) and Figure 3(c) show the effect of glazed area on annual energy consumption for this station. If the glazed area is increased by 10%, the increase in annual energy consumption is 14.6 kWh/m²yr for clear-clear glazing, 13.8 kWh/m²yr for low-e1-clear glazing, and 10.5 kWh/m²yr for low-e2-clear glazing, 5.4 kWh/m²yr for solar control (absorptive) glazing, and 2.4 kWh/m²yr for solar control (reflective) glazing.

4.5. Overheating in Winter

For Delhi station, when glazed area exceeds 20% value, building gets overheated even in winter and it requires cooling, subsequently. This holds true particularly for those glazings whose g-values are greater than 0.5. Such glazings let in solar radiation excessively, and this results in overheating. For such curtain walls, on annual bases also, there is high requirement of heating/cooling energy. For Delhi station, the results are shown in Table 3, and here, the glass-curtain forms the south façade of the building. For the reference case, when the glazed area is 20% only (clear-clear glazing), during winter, there is no overheating, and, hence, cooling energy requirement is almost nil. A small amount of heating, 0.3 kWh/m²yr, is required. For same case, during summer, the cooling energy requirement is 106.2 kWh/m²yr. But if the glazed area becomes 90% and the type of glazing remains the same (clear-clear), there is overheating in winter (resulting in cooling load of 27.7 kWh/m²yr). This also results in increased cooling load in summer (191.2 kWh/m²yr). Overheating in winter occurs for both types of low-e windows. Only for both types of solar control glazings, overheating in winter is very low or negligible: being 2.5 kWh/m²yr for solar control (absorptive) glazing and 0.1 kWh/m²yr for reflective type solar control glazing. During summer, low-e glazings (both types) show low summer cooling load as compared to clear-clear glazing. The reduction in summer cooling load is very significant for both types of solar control glazings: being 122.3 kWh/m²yr for absorptive and 97.9 kWh/m²yr for reflective, respectively.

Table 3: Some glass-curtain walls results in overheating in winter. Delhi station, south orientation.

Glazing type
Glazed area (%)
Annual energy consumption (kWh/m²yr)

Summer
Winter
Annual

Cooling
Heating
Cooling

Clear-clear ( reference)
20
106.2
0.3
0.0
106.5

Clear-clear
90
191.2
0.0
27.7
218.9

Low-e1-clear
90
187.6
0.0
29.5
217.1

Low-e2-clear
90
161.4
0.0
18.8
180.2

Solar control-abs
90
122.3
1.0
2.5
125.8

Solar control-ref
90
97.9
2.0
0.1
100.0

4.6. Effect of Orientation

Effect of orientation of glass-curtain wall on annual energy consumption is shown in Table 4. It is seen that south orientation corresponds to maximum annual heating/cooling load and it is minimum for north orientation. This fact holds good for all the stations. Building load for east and west orientation are almost equal (within 2% variation) for all types of glazings and for all climates. Also energy requirement in east and west direction is slightly more (about 1-2%) than north orientation. The reason is that: the beam radiation on east or west glazing is significant and has almost equal value, while it is almost nil on north glazing. Figure 4 shows the results for Delhi station. Here, annual building load for 20% glazed area (reference case, clear-clear) is normalized, so that the comparison of other glazing types with the reference case becomes simple. In south orientation and with respect to reference case, a clear-clear glass-curtain wall results in 106% more energy requirement. Increased energy requirement for other glass-curtain walls are 104% for low-e1, 69% for low-e2, 18% for solar control (absorptive), and −6% for solar control (reflective). The same trend is noticed for the other two stations also, Jodhpur and Chennai.

Table 4: Effect of orientation of glass-curtain walls on building energy consumption.

Station
Annual energy consumption (kWh/m²yr)

Glazing type
Glazed area (%)
North
South
East
West

Delhi
Clear-clear (reference)
20
98.0
106.5
99.8
98.8

Clear-clear
90
153.5
218.9
167.8
163.7

Low-e1-clear
90
149.2
217.1
163.2
160.5

Low-e2-clear
90
133.0
180.2
142.4
140.2

Sol.control-abs
90
113.9
125.8
112.2
112.8

Sol.control-ref
90
97.1
100.0
94.9
95.1

Jodhpur
Clear-clear (reference)
20
105.5
118.9
108.9
108.4

Clear-clear
90
164.6
242.7
185.3
186.5

Low-e1-clear
90
162.2
239.8
181.9
181.7

Low-e2-clear
90
143.8
200.8
158.4
160.4

Sol.control-abs
90
120.4
140.6
121.4
123.0

Sol.control-ref
90
102.6
108.8
101.7
102.9

Chennai
Clear-clear (reference)
20
124.7
132.5
124.9
125.0

Clear-clear
90
195.0
230.8
200.5
202.0

Low-e1-clear
90
191.1
226.3
195.9
197.2

Low-e2-clear
90
170.1
196.2
173.7
174.6

Sol.contro-abs
90
140.2
152.4
138.3
140.3

Sol.contro-ref
90
119.4
124.5
117.5
118.6

Figure 4: Effect of orientation on annual energy consumption. Four types of glass-curtain walls (90% glazed area) are compared with reference case (20% glazed area, clear-clear).

4.7. Effect of Climate

Effect of climate on comparison of glass-curtain wall with the reference case is shown in Figure 5. For each climate (or station), the annual energy consumption in the reference case is normalized to 100 kWh/m²yr in order to make the comparison simple. For composite climate of Delhi and with respect to reference case, a glass-curtain wall, made of clear-clear glazing, low-e1 glazing, low-e2 glazing, and solar control (absorptive) glazing shows 106%, 104%, 69%, and 18% more energy consumption respectively, while glass-curtain wall made of solar control (reflective) glazing shows 6% less energy consumption. For dessert climate of Jodhpur, the corresponding values (in the same sequence) are 104%, 102%, 69%, 18%, and −8%, respectively. For coastal climate of Chennai, the corresponding values are 74%, 71%, 48%, 15%, and −6%, respectively. This shows that for composite climate, low-e1 glass-curtain wall consumes 104% more energy, while the same curtain wall, for coastal climate, consumes only 71% more energy. So climate has significant effect on this comparison. It is also evident that, for all three climates, curtain wall made of solar control glazing (reflective) consumes 6%–8% less energy than the reference case.

Figure 5: Effect of climate on comparison of glass-curtain walls with reference case.

5. Conclusions

As the glazed area increases, the annual energy consumption increases. It is seen that this energy consumption increases almost linearly with glazed area, for all types of glazings, for all climates, and for all orientations. For Delhi station with south orientation, 10% increment in glazed area leads to more energy consumption of 15.3 kWh/m²yr for clear-clear glazing (highest increase) and 2.1 kWh/m²yr for solar control (reflective) glazing (lowest increase).

Glass-curtail wall, with south orientation, results in maximum heating/cooling load of a building, irrespective of the types of the glazings and the climates. Minimum energy consumption is for north oriented glass-curtain wall. For Jodhpur and for double glazed low-e1 glass-curtain wall, it is 239.8 kWh/m²yr for south orientation and 162.2 kWh/m²yr for north orientation.

Climate has significant effect on comparison of glass-curtain wall with the reference case (south orientation). A glass-curtain wall made of low-e1 glazing, with respect to to the reference case, consumes 103.9% more energy for the composite climate of Delhi and 71% more energy for coastal climate of Chennai.

Out of five glazings analysed, a glass-curtain wall made of solar control glazing (reflective) results in almost equal annual heating/cooling load of the building as the reference case (clear-clear, 20% glazed area). It holds true for all orientations and for all climatic conditions analysed. For south orientation and for 3 climates analysed, the glass-curtain wall consumes 6%–8% less energy than the reference case.

Acknowledgment

The first author is grateful to the Council for Scientific and Industrial Research (CSIR), New Delhi, for financial assistance.

References

C. Bouden, “Influence of glass curtain walls on the building thermal energy consumption under Tunisian climatic conditions: the case of administrative buildings,” Renewable Energy, vol. 32, no. 1, pp. 141–156, 2007.

N. K. Bansal, S. N. Garg, N. Lugani, and M. S. Bhandari, “Determination of glazing area in direct gain systems for three different climatic zones,” Solar Energy, vol. 53, no. 1, pp. 81–90, 1994.

N. I. Al-Hamdani and A. I. Ahmad, “Effect of window parameters on indoor thermal environment of buildings,” Solar and Wind Technology, vol. 4, no. 1, pp. 71–75, 1987.

S. Saridar and H. Elkadi, “The impact of applying recent façade technology on daylighting performance in buildings in eastern Mediterranean,” Building and Environment, vol. 37, no. 11, pp. 1205–1212, 2002.

Y. V. Perez and I. G. Capeluto, “Climatic considerations in school building design in the hot-humid climate for reducing energy consumption,” Applied Energy, vol. 86, no. 3, pp. 340–348, 2009.

R. Johnson, S. Selkowitz, F. Winkelmann, and M. Zentner, “Glazing optimization study for energy efficiency in commercial office buildings,” Tech. Rep. LBL–12764, pp. 1–10, Lawrence Berkeley National Laboratory, 1981.

R. Johnson, S. Selkowitz, and R. Sullivan, “How fenestration can significantly affect energy use in commercial buildings,” Tech. Rep. LBL–17330, pp. 1–14, Lawrence Berkeley National Laboratory, 1984.

H. Bulow-Hube, “The effect of glazing type and size on annual heating and cooling demand for Swedish offices,” in Proceedings of the Renewable Energy Technologies in Cold Climates, pp. 188–193, Montreal, Canada, 1998, Conference-46.

M. L. Persson, A. Roos, and M. Wall, “Influence of window size on the energy balance of low energy houses,” Energy and Buildings, vol. 38, no. 3, pp. 181–188, 2006.

M. Bojić and F. Yik, “Application of advanced glazing to high-rise residential buildings in Hong Kong,” Building and Environment, vol. 42, no. 2, pp. 820–828, 2007.

M. M. Aboulnaga, “Towards green buildings: glass as a building element-the use and misuse in the gulf region,” Renewable Energy, vol. 31, no. 5, pp. 631–653, 2006.

M. C. Singh, S. N. Garg, and R. Jha, “Different glazing systems and their impact on human thermal comfort-Indian scenario,” Building and Environment, vol. 43, no. 10, pp. 1596–1602, 2008.

T. Frank, “Climate change impacts on building heating and cooling energy demand in Switzerland,” Energy and Buildings, vol. 37, no. 11, pp. 1175–1185, 2005.

I. Singh, Heat transfer in fenestration systems and energy savings: buildings in India, Ph.D. thesis, Centre for Energy Studies, Indian Institute of Technology, New Delhi, India, 2002.

Energy Conservation Building Code in India, Bureau of Energy Efficiency, New Delhi, India, 2006.

SP: 41 (S&T), Hand Book of Functional Requirements of Buildings, Bureau of Indian Standards (BIS), New Delhi, India, 1987.

TRNSYS, “A transient system simulation program,” Tech. Rep. W E-53706, pp. 1–82, Solar Energy laboratory, University of Wisconsin, Madison, Wis, USA, 2004.