Advances in Civil Engineering
Volume 2018 (2018), Article ID 2028065, 9 pages
https://doi.org/10.1155/2018/2028065

Research Article

Development and Performance Evaluation of Light Shelves Using Width-Adjustable Reflectors

Heangwoo Lee,¹ Seonghyun Park,² and Janghoo Seo³

¹The Graduate School of Techno Design, Kookmin University, Seoul 02707, Republic of Korea
²Department of Architecture, Graduated School, Kookmin University, Seoul 02707, Republic of Korea
³School of Architecture, Kookmin University, Seoul 02707, Republic of Korea

Correspondence should be addressed to Janghoo Seo; seojh@kookmin.ac.kr

Received 11 December 2017; Accepted 29 January 2018; Published 1 April 2018

Academic Editor: Geun Y. Yun

Copyright © 2018 Heangwoo Lee et al. This is an open access article distributed under the Creative Commons Attribution License, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.

Abstract.

In recent years, there has been an increase in the consumption of energy for lighting purposes, which has led to an increase in the number of studies being conducted on this subject. Most studies have focused on light shelves, which are daylighting systems used for reducing the lighting energy required for the interiors of buildings. However, the existing light shelves cannot actively deal with external environmental factors, which often lead to an infringement of the right to light during the night when the performance of the light shelf deteriorates. Therefore, in this study, we propose a light shelf with a width-adjustable reflector and verify its validity using a testbed. The reflector of the proposed light shelf system is modularized so that the length can be adjusted in stages. The optimum width of the light shelf is calculated in terms of the energy reduction and uniformity ratio improvement, and the obtained optimum width is varied depending on the season. We find that the width-adjustable reflector can save 20% and 21.6% more lighting energy than light shelves with fixed reflector widths of 0.3 m and 0.6 m, respectively.

1. Introduction

According to the 2010 report of the International Energy Agency (IEA), which is an international energy organization based in the United States, the consumption of lighting energy in the building sector is 18% of the total energy consumption in this sector. The lighting energy consumption in the building sector is expected to increase continuously. Therefore, an increasing number of studies are focusing on the use of light shelves to reduce the lighting energy consumption of buildings [1–5]. A light shelf is a daylighting system installed on windows, which introduces external natural light into the interiors of a building. The daylight performance of a light shelf significantly deteriorates at night and during the day when the external illumination is low. This infringes on the right to light because the light shelf blocks the external view. The possible infringement of the right because of the installation of a light shelf may be less significant when compared to awning devices, such as a louver. When the installation height of the light shelf is low, natural light is brought deeper indoors, which helps to improve the lighting performance. Studies on light shelves have shown that the most appropriate distance for a light shelf from the bottom surface in an indoor environment is 1,800 mm [6, 7]; therefore, it is necessary to consider the possibility of an infringement of the right to light when designing and installing a light shelf. In addition, an external light shelf has outstanding daylight performance [6], but it is an external projection (i.e., a device attached to the outside of a building). Thus, the light shelf can be damaged by strong winds when used in high-rise buildings [8]. In winters, the light shelf may cause [9] an increase in the consumption of heating energy by blocking incoming solar radiation from the outside. These problems can hinder the development of the light shelf industry; therefore, research is essential for solving such problems by controlling the area where natural lighting is provided using a light shelf. Hence, in this study, we propose a light shelf with a width-adjustable reflector and conduct a performance evaluation based on a full-scale testbed to verify the feasibility and effectiveness of this light shelf; we also establish the basic data for a light shelf design.

1.1. Concept of a Light Shelf and Literature Review

A light shelf is a daylighting system that introduces external natural light into the building interiors by reflecting the light from the light shelf’s reflector and the indoor ceiling surface (Figure 1). Also, a light shelf improves the problems of glare or illumination imbalance by blocking the direct introduction of external natural light into the interior space. The variables for determining the performance of a light shelf include the height, width, angle, and material of the light shelf; appropriate variable control is required to maximize the performance of the light shelf.

Figure 1: Concept of a variable light shelf.

In Table 1, we review and summarize previous research on light shelves [8, 10–22]. Based on these studies, we chose the angle of the light shelf as the variable to be applied for the operation of a light shelf in response to the external environment. This is because the amount and position of natural light brought into the indoor space change according to the angle of the light shelf, and it is easy to improve the lighting performance of the light shelf by observing these changes (Figure 2). In addition, the widths of the light shelves examined in previous research were fixed at a certain value for performance evaluation. Thus, a light shelf with a width-adjustable reflector was proposed in this study to distinguish it from the light shelves used in the previous studies.

Table 1: Details of previous studies on light shelves.

Title of study
Year
Light shelf variables

Width
Width adjustability

Effectiveness of a perforated light shelf for energy saving [8]
2017
Fixed at a certain value
Not considered

Performance evaluation of light shelves [10]
2017
Fixed at a certain value
Not considered

Daylighting performance improvement of a light shelf using diffused reflection [11]
2017
Fixed at a certain value
Not considered

Study on movable light shelf system with location-awareness technology for lighting energy saving [12]
2017
Fixed at a certain value
Not considered

Investigating the influence of light shelf geometry parameters on daylight performance and visual comfort, a case study of educational space in Tehran, Iran [13]
2016
Fixed at a certain value
Not considered

Evaluating daylight performance of light shelves combined with external blinds in south-facing classrooms in Athens, Greece [14]
2016
Fixed at a certain value
Not considered

Dynamic internal light shelf for tropical daylighting in high-rise office buildings [15]
2016
Fixed at a certain value
Not considered

The effects of direct sunlight on light shelf performance under tropical sky [16]
2015
Fixed at a certain value
Not considered

New static light shelf system design of clerestory windows for Hong Kong [17]
2014
Fixed at a certain value
Not considered

Maximizing the light shelf performance through interaction between light shelf geometries and a curved ceiling [18]
2010
Fixed at a certain value
Not considered

Optimizing performance of the light shelf by modifying ceiling geometry in highly luminous climates [19]
2008
Fixed at a certain value
Not considered

Indoor daylight climate—influence of light shelf and model reflectance on light shelf performance in Madrid for hours with unit sunshine fraction [20]
2002
Fixed at a certain value
Not considered

Advanced optical daylighting systems: light shelves and light pipes [21]
1997
Fixed at a certain value
Not considered

The development of coefficients of utilization for light shelves [22]
1993
Fixed at a certain value
Not considered

(a)

(b)

(c)

Figure 2: Inflow of light corresponding to three angles of the light shelf. (a) Light shelf angle: 0°, (b) light shelf angle: 10°, and (c) light shelf angle: 30°.

1.2. Optimum Indoor Illumination Standard

In this study, a 1 : 1 scale testbed was used to evaluate the performance of the light shelf. The performance was evaluated by obtaining the lighting usage depending on the variables of the light shelf for maintaining the optimum illumination for an indoor space. An optimum indoor illumination standard was used as the index for evaluating the performance of the light shelf in this study, and the optimum indoor illumination standards suggested in the United States, Japan, and Korea were reviewed (Table 2) [23–25]. In this study, the optimum indoor illumination standard for the light shelf performance evaluation was set to 500 lx based on the review of the aforementioned optimum indoor illumination standards.

Table 2: Recommended illumination levels.

Task grade
Recommended levels of illumination
Minimum allowed illumination (lx)
Standard allowed illumination (lx)
Maximum allowed illumination (lx)

General
IES (USA)
500
750
1000

JIS Z 9110 (Japan)
300
500
750

KS A 3011 (Republic of Korea)
300
400
600

Simple
IES (USA)
200
300
500

JIS Z 9110 (Japan)
150
200
300

KS A 3011 (Republic of Korea)
150
200
300

2. Method

2.1. Light Shelf with a Width-Adjustable Reflector

To design a light shelf with a width-adjustable reflector, we stacked reflectors on top of one another; a width-adjustable reflector helps to actively cope with diverse external environments (Figure 3). The width of the light shelf reflector could be adjusted in stages. A light shelf with a width-adjustable reflector can minimize the problems associated with existing light shelves having fixed reflector widths. The common problem areas are damage caused by wind pressure and the possible infringement of the right to light. Also, adjusting the width of the light shelf reflector can resolve the problem of receiving reduced solar radiation because of the shading of the light shelf during winter.

(a)

(b)

Figure 3: Schematic of a light shelf with a width-adjustable reflector. (a) Adjustment of the width of the light shelf at the minimum and maximum lengths (stages 1, 2, 3, and 6). (b) Width adjustment for each light shelf stage (stages 1, 2, 3, and 6).

We proposed a manual system and an automated system for designing the light shelf with a width-adjustable reflector. In the automated system, the control was carried out based on the following procedures. First, at night and before an occupant entered the room, the width of the light shelf reflector was maintained at its minimum; each light shelf reflector module was maintained in stacks. Minimizing the width of the light shelf reduced the possibility of an infringement of the right to light if the light shelf was unable to function. Maintaining a minimum width also helps to reduce the damage caused by external environmental factors such as wind pressure. Second, when an occupant entered the room, the angle of the light shelf was controlled and its width was maintained at the minimum length. When the illumination sensors directly linked with the lighting detected an illumination of 500 lx during the angle control, the light shelf control was stopped. However, when the illumination sensors linked with the indoor lighting detected an illumination less than 500 lx despite the angle control, the width of the light shelf reflector was controlled. Third, the width of the light shelf was increased in stages, and the angle was controlled at each stage. We controlled the angle so that the illumination sensors linked with the indoor lighting could detect an illumination of 500 lx through a repeated control process. When the illumination sensors could not detect 500 lx despite repeating the control process, reoperation and lighting control were performed so that the length and angle could be adjusted to obtain a value close to 500 lx.

2.2. Performance Evaluation Environment Setting

In this study, a testbed was established for evaluating the performance of the light shelf using a width-adjustable reflector; the testbed had a width of 4.9 m, a depth of 6.6 m, and a height of 2.5 m, as shown in Table 3. The window where the light shelf was installed had a width of 2.2 m and a height of 1.8 m. The glass used for the window was a pair glass with 80% transmissivity. In addition, an artificial climate chamber equipped with an artificial sunlight radiation device was installed for the external environment of the testbed. Using the artificial sunlight radiation device, we could produce an external light environment for each season by adjusting the amount of light, height, and angle of the light source. The sunlight radiation device used in this study was an artificial light source, which may be slightly different from the actual light source. However, the artificial light source was effective; it had an A grade in terms of illuminance uniformity according to the ASTM E927-85 standards. Using the artificial light source, we could establish the same external light environments for different performance evaluations. Indoor lighting was installed at four locations following the four point method of IES [23]. For each lighting, we used LED-type lighting that is capable of eight-stage dimming control.

Table 3: Setting of testbed.

Room size, material
(i) 4.9 m (W) × 6.6 m (D), 2.5 m (ceiling height)

(ii) Ceiling: reflexibility 86%, wall: reflexibility 46%, floor: reflexibility 25%

Window size, material
(i) 2.2 m (W) × 1.8 m (H)

(ii) 12 mm pair glass (3CL + 6A + 3CL)

(iii) Transmissivity: 80%

Lighting
(i) 8 level dimming (LED type) 4 locations

(ii) Dimension (mm): 600 × 600

(iii) Dimming range: 10–100%

(iv) Electricity consumption based on the level of dimming lighting control: lv 1 (12 W), lv 2 (18 W), lv 3 (22 W), lv 4 (28 W), lv 5 (34 W), lv 6 (39 W), lv 7 (43 W), lv 8 (51 W)

Illuminance sensor
(i) Sensing element: silicon photo sensor with filter

(ii) Detection range: 0–200,000 lx

(iii) Precision: ±3%

External illuminance
Winter: 30,000 lx, middle season: 60,000 lx, summer: 80,000 lx

Solar altitude
Winter: 23.5°, middle season: 52.5°, summer: 76.5°

Direction (culmination time)
South (south-central time)

Energy consumption monitoring system
(i) Model: SPM–141

(ii) Measurement capacity: single phase

(iii) Margin of error: within 2.0%

Overview of the testbed and artificial sunlight source

For the performance evaluation of this study, 10 illumination sensors were arranged (Figure 4) to measure the indoor illumination distribution depending on the installation of the light shelf. The illumination sensor was installed at 1.1 m intervals based on the size of the space. The height of the illumination sensor was 850 mm from the floor to the working surface.

Figure 4: Plan and section of testbed and the location of the illumination sensor.

2.3. Performance Evaluation Method

To evaluate the performance of a light shelf fitted with a width-adjustable reflector, we first verified the validity of the light shelf having a width-adjustable reflector—we called this “Case 3.” For performance evaluation, the widths of the fixed light shelf were set as 0.3 m and 0.6 m; these values were determined based on previous studies related to light shelves [6, 26–30]. The lighting energy consumption and uniformity ratio of Case 3 were calculated and compared with those of the light shelves with fixed reflector widths of 0.3 m (“Case 1”) and 0.6 m (“Case 2”); the results are presented in Table 4. The reflector width for Case 3 could be adjusted in six stages at 0.1 m intervals (from 0.1 m to 0.6 m), as shown in Figure 5. In addition, the type of light shelf proposed in this study was an outdoor type light shelf, which was set according to the standards of an outdoor type of light shelf. A profile with a size of 20 mm × 20 mm was used to manufacture the light shelf with a width-adjustable reflector. Second, to calculate the lighting electricity consumption depending on the variables of the light shelf, the illumination sensors 2, 4, 7, and 9 were linked with the lightings 1, 2, 3, and 4, respectively. If a measured illumination value was less than 500 lx for the illumination sensors 2, 4, 7, and 9, dimming lighting control was carried out in sequence from the lighting that was linked with the illumination sensor having the lowest illumination value. The lighting control was stopped when 500 lx was reached during the dimming lighting control. The lighting energy consumption at the end was calculated and used as the index for performance evaluation. In this study, the lighting energy consumption values were calculated for summer, middle season, and winter based on a one-hour period and in the southern direction. In addition, it was necessary to allow a certain time to carry out the generalized performance evaluation of the light shelf. However, because of the mechanical characteristics of the artificial sunlight radiation device, performance evaluation was carried out only for the southern direction in this study. Therefore, a one-hour period was applied for performance evaluation. Third, the uniformity ratio of illumination was deduced in this study based on the values of illumination sensor number 1–number 10, which were measured for each case. The variables for the light shelf and uniformity ratio of illumination were calculated as the ratio of minimum illumination to the average illumination. Fourth, to conduct the performance evaluation depending on the variables of the light shelf, the optimum width and optimum angle of the light shelf were calculated based on the season. We selected the optimum width and optimum angle values for the lowest lighting electricity consumption. However, when the lighting energy consumptions were identical, we selected the value with a higher uniformity ratio. Fifth, we specified the light shelf variables for the performance evaluation, as shown in Table 5.

Table 4: Three cases for evaluating light shelf performance.

Control of light shelf variables

Angle control
Width control

Case 1
−10°, 0°, 10°, 20°, 30°
0.3 m fixed

Case 2
0.6 m fixed

Case 3
0.1 m–0.6 m (width is adjustable in stages at intervals of 0.1 m)

(a)

(b)

Figure 5: Testbed for a light shelf with a width-adjustable reflector.

Table 5: Setting of light shelf variables for performance evaluation.

Height
1800 mm

Angle range
−10°, 0°, 10°, 20°, 30°

Reflectivity
Specular reflection film (reflexibility 85%)

Type
Exterior type

3. Results and Discussion

3.1. Performance Evaluation Result

In this study, we proposed a light shelf with a width-adjustable reflector (Case 3). To verify the validity of the suggested light shelf, its lighting energy reduction performance and uniformity ratio were calculated. We compared these results with Case 1 (0.3 m reflector) and Case 2 (0.6 m reflector). The following results were obtained.

First, the optimum width of the light shelf varied depending on the season, as shown in Table 6. For summer, the lighting electricity consumption values for maintaining the value of the illumination sensor linked with the indoor lighting at 500 lx were 0.120 and 0.114 kWh for Case 1 and Case 2, respectively. Also, in middle season, the lighting energy consumption values for Case 1 and Case 2 were 0.102 and 0.114 kWh, respectively.

Table 6: Performance evaluation results for light shelves with reflector widths of 0.3 m and 0.6 m.

Seasons
Light shelf
Illumination sensor (lx)
Uniformity ratio
Lighting dimming control: lighting number (dimming level)
Electricity consumption (kWh)

Width (m)
Angle
Minimum
Average

Summer
0.3
−10°
71.7
222.3
0.322
1 (8)→3 (8)→2 (3)
0.124

0°
76.1
236.5
0.322
1 (8)→3 (8)→2 (3)
0.124

10°
79.1
243.8
0.324
1 (8)→3 (8)→2 (2)
0.120

20°
86.3
246.2
0.350
1 (8)→3 (8)→2 (2)
0.120

30°
88.4
250.8
0.352
1 (8)→3 (8)→2 (2)
0.120

0.6
−10°
72.9
241.5
0.302
1 (8)→3 (8)→2 (2)
0.120

0°
76.1
260.1
0.293
1 (8)→3 (8)→2 (2)
0.120

10°
78.8
271.7
0.290
1 (8)→3 (8)→2 (2)
0.120

20°
96.3
289.2
0.333
1 (8)→3 (8)→2 (1)
0.114

30°
101.9
299.0
0.341
1 (8)→3 (8)→2 (1)
0.114

Middle season
0.3
−10°
81.9
286.1
0.286
1 (8)→3 (8)→2 (2)
0.120

0°
86.6
295.6
0.293
1 (8)→3 (8)→2 (1)
0.114

10°
91.0
299.0
0.304
1 (8)→3 (8)→2 (1)
0.114

20°
99.3
308.6
0.322
1 (8)→3 (8)
0.102

30°
107.4
310.3
0.346
1 (8)→3 (8)
0.102

0.6
−10°
70.8
276.8
0.256
1 (8)→3 (8)→2 (2)
0.120

0°
77.2
295.7
0.261
1 (8)→3 (8)→2 (1)
0.114

10°
85.9
307.3
0.280
1 (8)→3 (8)→2 (1)
0.114

20°
92.3
315.2
0.293
1 (8)→3 (8)→2 (1)
0.114

30°
94.4
310.5
0.304
1 (8)→3 (8)→2 (1)
0.114

Winter
0.3
−10°
157.3
558.9
0.281
1 (8)→3 (1)
0.063

0°
160.7
581.8
0.276
1 (8)→3 (1)
0.063

10°
164.1
595.4
0.276
1 (8)→3 (1)
0.063

20°
166.2
601.7
0.276
1 (8)→3 (1)
0.063

30°
180.1
593.6
0.303
1 (8)→3 (1)
0.063

0.6
−10°
139.8
532.4
0.263
1 (8)→3 (1)
0.063

0°
145.1
556.3
0.261
1 (8)→3 (1)
0.063

10°
150.5
582.6
0.258
1 (8)→3 (1)
0.063

20°
156.7
607.5
0.258
1 (8)→3 (1)
0.063

30°
164.4
616.7
0.267
1 (8)→3 (1)
0.063

Second, the optimum angle for Case 1 and Case 2 based on the electricity consumption and uniformity ratio was 30° for summer, middle season, and winter (Table 7). Based on the optimum angle, the lighting electricity consumption values for Case 1 and Case 2 were 0.285 and 0.291 kWh, respectively, for summer, middle season, and winter.

Table 7: Optimum angle and total electricity consumption for the light shelves with reflector widths of 0.3 m and 0.6 m.

Width (m)
Summer
Middle season
Winter
Electricity consumption (kWh)

Optimum angle
Electricity consumption (kWh)
Optimum angle
Electricity consumption (kWh)
Optimum angle
Electricity consumption (kWh)

0.3
30°
0.120
30°
0.102
30°
0.063
0.285

0.6
30°
0.114
30°
0.114
30°
0.063
0.291

Third, for the uniformity ratio, the light shelf in Case 1 showed a higher value than that in Case 2, regardless of the season.

Fourth, for Case 3, the obtained optimum widths were 0.6 m, 0.2 m, and 0.1 m for summer, middle season, and winter, respectively (Table 8). As mentioned earlier, the selection of the optimum length of the light shelf for each season was based on the lowest lighting energy consumption. In particular, Figure 6 represents the introduction of external natural light into the interior space using the light shelf. An increase in the width of the light shelf during winter decreased the amount of natural light that was directly introduced into the interior space. Also, a decrease in the width of the light shelf reflector helped reduce the lighting energy because the solar altitude is low in winter. For Case 3, the lighting electricity consumption obtained by controlling the angle of the light shelf based on the optimum width of the light shelf was 0.228 kWh. To conserve space, we present only the results for the reflector widths with the lowest electricity consumption for each season.

Table 8: Performance evaluation results for a light shelf with a width-adjustable reflector.

Season
Light shelf
Illumination sensor (lx)
Uniformity ratio
Lighting dimming control: lighting number (dimming level)
Electricity consumption (kWh)

Optimum width (m)
Angle
Minimum
Average

Summer
0.6
−10°
72.1
230.7
0.312
1 (8)→3 (8)→2 (2)
0.124

0°
76.1
243.8
0.312
1 (8)→3 (8)→2 (2)
0.124

10°
83.3
259.8
0.321
1 (8)→3 (8)→2 (2)
0.124

20°
89.1
276.1
0.323
1 (8)→3 (8)→2 (1)
0.114

30°
96.0
281.9
0.341
1 (8)→3 (8)→2 (1)
0.114

Middle season
0.2
−10°
88.8
280.6
0.316
1 (8)→3 (8)→2 (2)
0.124

0°
90.2
286.3
0.315
1 (8)→3 (8)→2 (2)
0.124

10°
92.9
293.5
0.316
1 (8)→3 (8)→2 (1)
0.114

20°
93.8
296.0
0.317
1 (8)→3 (8)→2 (1)
0.114

30°
98.0
299.9
0.327
1 (8)→3 (8)
0.102

Winter
0.1
−10°
177.2
625.55
0.283
1 (8)→3 (2)
0.069

0°
177.6
640.24
0.277
1 (8)→3 (2)
0.069

10°
182.4
656.49
0.278
1 (8)
0.012

20°
189.2
677.52
0.279
1 (8)
0.012

30°
194.3
672.78
0.289
1 (8)
0.012

Total electricity consumption (kWh):
0.228

(a)

(b)

Figure 6: Introduction of light depending on the width of the light shelf for winter. (a) Light shelf with a 0.3 m width. (b) Light shelf with a 0.6 m width.

3.2. Discussion

In this study, the lighting electricity consumption and uniformity ratio were calculated depending on the width of the light shelf. We found that the obtained optimum width of the light shelf varied based on the lighting energy reduction and uniformity ratio, which depended on the season. This result verified Case 3, which used a light shelf with a width-adjustable reflector. Case 3 could save 20% and 21.6% more lighting energy as compared to Case 1 (using 0.3 m reflector) and Case 2 (using 0.6 m reflector), respectively (Figure 7). It seems much possible to save lighting energy in an efficient manner in Case 3 by adjusting the light shelf width in response to external light environments. This will also resolve the possible infringement of the right to light caused by previous types of fixed-width light shelves attached to skylights. Especially, previous types of light shelves tended to increase lighting energy consumption during winter because even though natural light can be brought deep into the indoors because of low solar altitude during winter, the light shelf actually interrupts or blocks natural light. However, when the light shelf width is adjustable, as suggested in this study, it minimizes the reflective area of the light shelf during winter and increases the amount of light brought from the outside; therefore, Case 3 can save 80.9% more lighting energy as compared to Case 1 and Case 2. Also, Case 3 minimizes the reflective area during winter and is advantageous in saving heating energy by securing solar radiation; therefore, it is considered an advanced form of light shelf compared to previous light shelves.

Figure 7: Lighting electricity consumption for Case 1, Case 2, and Case 3.

In this study, we evaluated the performance of different kinds of light shelves by focusing on the reduction in energy consumption by using a light shelf with a width-adjustable reflector. The adjustment of the light shelf width helps reduce the damage caused by the weather and minimizes the possibility of an infringement of the right to light. However, this study has its limitations. The performance of the light shelf was evaluation in an artificial environment and under specific conditions, which might be different from real-life situations. Also, the economic and technical factors involved in adjusting the width of the light shelf were not considered. Further studies are required to examine these areas. In particular, this study includes the mechanism used with previous light shelves to control the angle and width. Further studies are required to evaluate the technical aspects for improving the implementation of such mechanism. Additional studies are also required to evaluate the economic performance of the proposed light shelf.

4. Conclusion

In this study, a light shelf with a width-adjustable reflector was proposed for efficient control and daylight performance improvement in response to changes in the external environment. To verify the validity, the performance was evaluated based on a testbed.

For the light shelf with a width-adjustable reflector proposed in this study, the reflector was modularized so that its length could be adjusted. In particular, the light shelf with a width-adjustable reflector can actively respond to the external environmental changes by minimizing the width when the efficiency of the light shelf decreases (e.g., at night); this can reduce the problems associated with the existing light shelves. The optimum width of the light shelf varied with the lighting energy reduction and uniformity ratio depending on the season. This was resolved by adjusting the width of the reflector.

We found that Case 3 (proposed in this study) could save 20% and 21.6% more lighting energy as compared to Case 1 and Case 2, respectively. In particular, Case 3 minimized the reflective area of the light shelf during winter, and could save 80.9% more lighting energy as compared to Case 1 and Case 2.

In this study, we helped resolve the problems associated with existing light shelves, and lighting energy could be saved by improving the daylight performance. This study has its limitations. The economic and technical examinations for controlling the light shelf width were not considered, and the study was conducted in an artificial environment. Future studies need to address these limitations and resolve related energy issues in the building sector.

Conflicts of Interest

The authors declare that they have no conflicts of interest.

Acknowledgments

This work was supported by the National Research Foundation of Korea (NRF) grant funded by the Korean government (NRF-2015R1C1A1A01052784).

References

A. D. Galasiu, G. R. Newsham, C. Suvagau, and D. M. Sander, “Energy saving lighting control systems for open-plan offices: a field study,” Leukos, vol. 4, no. 1, pp. 7–29, 2007.

D. K. Tiller, X. Guo, G. P. Henze, and C. E. Waters, “The application of sensor networks to lighting control,” Leukos, vol. 5, no. 4, pp. 313–325, 2009.

X. Guo, D. K. Tiller, G. P. Henze, and C. E. Waters, “Analytical methods for application to sensor networks for lighting control,” Leukos, vol. 5, no. 4, pp. 297–311, 2009.

G. Lowry, “Energy saving claims for lighting controls in commercial buildings,” Energy and Buildings, vol. 133, pp. 489–497, 2016.

L. Xu, Y. Pan, Y. Yao, D. Cai, Z. Huang, and N. Linder, “Lighting energy efficiency in offices under different control strategies,” Energy and Buildings, vol. 138, pp. 127–139, 2017.

H. W. Lee, D. S. Kim, and Y. S. Kim, “Simulation study on the performance evaluation of light shelf focused on the depth of space and the dimensions and angles of light shelf,” Journal of the Architectural Institute of Korea Planning & Design, vol. 29, no. 3, pp. 335–344, 2013.

G. Yun, D. W. Sho, and K. S. Kim, “A study on visual environment evaluation of residential space using the radiance program,” Journal of the Architectural Institute of Korea Planning & Design, vol. 27, no. 2, pp. 227–234, 2011.

H. W. Lee, K. S. Kim, J. H. Seo, and Y. S. Kim, “Effectiveness of a perforated light shelf for energy saving,” Energy and Buildings, vol. 144, pp. 144–151, 2017.

G. M. Jeon, H. W. Lee, J. H. Seo, and Y. S. Kim, “Performance evaluation of light shelf based on light environment and air conditioner environment,” KIEAE Journal, vol. 16, no. 5, pp. 47–55, 2016.

G. A. Warrier and B. Raphael, “Performance evaluation of light shelves,” Energy and Buildings, vol. 140, pp. 19–27, 2017.

H. Lee, G. Jeon, J. Seo, and Y. Kim, “Daylighting performance improvement of a light shelf using diffused reflection,” Indoor and Built Environment, vol. 26, no. 5, pp. 717–726, 2017.

H. Lee, S. Kim, J. Seo, and Y. Kim, “Study on movable light shelf system with location-awareness technology for lighting energy saving,” Indoor and Built Environment, vol. 26, no. 6, pp. 796–812, 2017.

M. H. Moazzeni and Z. Ghiabaklou, “Investigating the influence of light shelf geometry parameters on daylight performance and visual comfort, a case study of educational space in Tehran, Iran,” Buildings, vol. 6, no. 3, p. 26, 2016.

A. Meresi, “Evaluating daylight performance of light shelves combined with external blinds in south-facing classrooms in Athens, Greece,” Energy and Buildings, vol. 116, pp. 190–205, 2016.

Y. W. Lim and C. Y. S. Heng, “Dynamic internal light shelf for tropical daylighting in high-rise office buildings,” Building and Environment, vol. 106, pp. 155–166, 2016.

Y. W. Lim and M. H. Ahmad, “The effects of direct sunlight on light shelf performance under tropical sky,” Indoor and Built Environment, vol. 24, no. 6, pp. 788–802, 2015.

P. Xue, C. M. Mak, and H. D. Cheung, “New static lightshelf system design of clerestory windows for Hong Kong,” Building and Environment, vol. 72, pp. 368–376, 2014.

A. A. Freewan, “Maximizing the lightshelf performance by interaction between lightshelf geometries and a curved ceiling,” Energy Conversion and Management, vol. 51, no. 8, pp. 1600–1604, 2010.

A. A. Freewan, L. Shao, and S. Riffat, “Optimizing performance of the lightshelf by modifying ceiling geometry in highly luminous climates,” Solar Energy, vol. 82, no. 4, pp. 343–353, 2008.

S. T. Claros and A. Soler, “Indoor daylight climate–influence of light shelf and model reflectance on light shelf performance in Madrid for hours with unit sunshine fraction,” Building and Environment, vol. 37, no. 6, pp. 587–598, 2002.

L. O. Beltran, E. S. Lee, and S. E. Selkowitz, “Advanced optical daylighting systems: light shelves and light pipes,” Journal of the Illuminating Engineering Society, vol. 26, no. 2, pp. 91–106, 1997.

R. M. N. Saraiji and R. G. Mistrick, “The development of coefficients of utilization for light shelves,” Journal of the Illuminating Engineering Society, vol. 22, no. 1, pp. 139–162, 1993.

Illuminating Engineering Society, The Lighting Handbook, Illuminating Engineering Society (IES), New York, NY, USA, 10th edition, 2011.

JISZ 9110, Recommended Levels of Illumination, Japanese Industrial Standards Committee, Tokyo, Japan, 2010.

KSA 3011-2013, Recommended Levels of Illumination, The Korean Standards Association (KSA), Seoul, Republic of Korea, 1998.

K. Kim, H. Shim, H. Lee, J. Seo, and Y. Kim, “Development of rolling type light shelf with adjustable reflectivity,” KIEAE Journal, vol. 16, no. 5, pp. 57–64, 2016.

Y. S. Cho, B. S. Kim, and J. S. Lee, “Analysis on the indoor daylight performance and optimum size selection of a light shelf using lightscape,” Journal of the Architectural Institute of Korea Planning & Design, vol. 20, no. 6, pp. 231–238, 2004.

D. Y. Heo, H. W. Lee, and Y. S. Kim, “A study on performance evaluation of lighting performance of internal light shelf according to the reflectivity,” Information, vol. 18, no. 5, pp. 2117–2122, 2015.

H. Y. Ahn, H. W. Lee, and Y. S. Kim, “A study on light shelf system based on it in housing space,” KIEAE Journal, vol. 13, no. 1, pp. 133–140, 2013.

S. Oh, H. Lee, Y. Kim, and J. Seo, “Research on lighting performance evaluation for different curvature reflection rate in residential space,” Korean Journal of Air-Conditioning and Refrigeration Engineering, vol. 27, no. 6, pp. 328–336, 2015.