^{1}

^{2}

^{2}

^{1}

^{1}

^{2}

A mass of thermal energy from the combined cooling, heating, and power (CCHP) system will be wasted by the buildings with low ratio of heat to power demand. To further improve the using efficiency of the excess thermal energy, an active method, which adds the organic Rankine cycle (ORC) equipment in the CCHP system, is configured. A complementary configuration of this CCHP-ORC is also investigated. This paper presents a matrix modeling approach to establish a mathematical model of the CCHP-ORC system. The CCHP-ORC system can be viewed as a multiple input and multiple output (MIMO) model. Energy conversion of the system components is described as the efficiency matrices. Energy flow between the system components is described as dispatch matrices. Energy conversion and flow from the system input to output are modeled by a conversion matrix. The objective function and the constraints of the system are determined. The optimal operation strategies are obtained by solving the optimization problem of minimizing the evaluation criteria function. Comprehensive case studies are conducted based on a hypothetical CCHP-ORC system. The study results reveal that the effectiveness and economic efficiency of the proposed approaches outperform those obtained from conventional CCHP systems.

According to the statistical data from the Energy Information Administration of the U.S. Department of Energy, in many countries, building energy consumption accounts for about 36% of the total energy consumption, and nearly 30% of greenhouse gas (GHG) emissions [

A CCHP system is an integrated energy supply system, which can also be referred to as the trigeneration system [

Performance of the CCHP system depends on the system structure and the operation strategy. In [

Once the system structure is determined and implemented, the operation strategy is the crucial factor for the CCHP system design. There are two popular operation strategies [

Operation strategy design relies on the selection of evaluation criteria, which should be aligned with the stakeholders’ objectives. Energy savings and environmental impacts are two popular aspects when constructing evaluation criteria. Fumo

For an existing CCHP system, when the electricity to thermal energy requirement ratio of building users is exactly equal to the output ratio of the PGU, the maximum efficiency of the CCHP system is achieved [

In recent years, more attention has been put on the ORC system. A complementary structure of CCHP-ORC system is configured in [

When the structure of the CCHP-ORC system is configured, the operation strategy should be designed. Firstly, the mathematical model of the CCHP-ORC system should be established. From the perspective of control theory, the CCHP-ORC system can be treated as the connection between the energy input and the building users’ demand. We consider using transfer function in control theory to describe this input-output relation. Because the energy input includes fuel and electricity from the power grid, and the building users’ demand includes cooling, heating, and power, the CCHP-ORC system is a multiple input and multiple output (MIMO) system. In [

The main contribution of this paper is that a more intuitive and comprehensive approach, a matrix transfer function modeling approach (referred to as matrix modeling approach), is proposed to model the CCHP-ORC system. Based on the matrix modeled system, sequential quadratic programming (SPQ) algorithm is adopted to optimize the linear objective function, which is subjected to the nonlinear equalities and inequalities. The result of the optimization problem is the optimal flow and operation strategy for the CCHP-ORC.

This paper is organized as follows. The configuration and matrix modeling of the CCHP-ORC system are described in Section

In this section, an optimal CCHP-ORC structure and an intuitive matrix modeling of the CCHP-ORC system will be introduced. In order to make full use of energy and improve the flexibility of energy supply, the configuration of the CCHP-ORC system is presented in Figure

Structure diagram of a CCHP-ORC system.

In addition to traditional equipment, a complementary ORC and an electric chiller are added as important components which can not only utilize the excess thermal energy but also dynamically adjust the electricity to thermal energy output ratio of the entire system. In Figure

The energy conversion of the components in the CCHP-ORC system can be described using efficiency matrices, namely, coupling matrices. In this paper,

Consequently, the input-output relation of the ORC can be represented in the following matrix form:

Following the same procedure, efficiency matrices for the PGU, auxiliary boiler, heat recovery system, heating unit, electric chiller, and absorption chiller can be obtained as

Each efficiency matrix represents the performance of the energy conversion of each component in the CCHP-ORC system.

The dispatch matrices indicate the energy flow between the components in the system. Usually, the dispatch factors exist at the bifurcations of the system. For example in Figure

At the ORC side, we have

By following the similar procedure, the dispatch matrices for the PGU, the auxiliary boiler, electric chiller, heat recovery system, heating unit, and absorption chiller can be defined as

Similarly, in addition to (

The CCHP-ORC system modeled in a matrix form can be viewed as an input-out model. The conversion matrix of the CCHP-ORC system describes the relationship between the input and the output and represents the energy flow procedure of the system. From Figure

Then the conversion matrix of the CCHP-ORC system,

In order to obtain the conversion matrix

For the cooling part, we have

The heating demand is solely provided by the heating unit. Thus, we have

The conversion matrix of the CCHP-ORC system can be obtained from (

The main objective of this paper is to determine the dispatch factors and the system input to optimize the performance criteria objective function.

Having the whole system modeled in a matrix form, we can formulate the operation strategy design as an optimization problem. The objective function and associated constraints will be illustrated in the rest of this section.

As mentioned in Section

PEC is a direct and common indicator to reflect the operating efficiency of a CCHP-ORC system. PEC is defined as

In order to obtain the optimal energy flow and operation strategy for every hour, HTC is adopted as a key element in the operation strategy optimization. HTC of the CCHP-ORC system is defined as

Greenhouse gas emission control is an emerging topic in the CCHP system design. In a CCHP-ORC system equipped with fossil-fuel combustion units, CDE serves as an indicator of environment impacts and can be calculated as

To comprehensively evaluate the system performance, we define a performance evaluation criteria (EC) function as a weighted summation of the three above mentioned criteria. The most commonly used way to evaluate the performance of a CCHP-ORC system is to compare those factors with those of the SP system. Thus, the hourly EC function can be redefined as

Consequently, the annual

Formulating a complete optimization problem includes determining decision variables, designing objective function, and setting constraints. The whole procedure will be elaborated on this part.

As mention in Section

It can be readily observed from (

The system energy inputs include

By using the defined optimizer

In the sense of balance, (

Similarly, the system input

Then the nonlinear equality constraint in (

The inequality constraints include the bound of the decision variables, various capacities of system components, and thresholds of the components output. The decision variables can be separated into two parts: one consists of dispatch factors, and the other consists of system input. To facilitate the later derivation, we define

According to (

In this paper, we assume that no electricity would be sold back; thus the constraints for fuel and electricity input can be represented by

Inequalities in (

Each component in the CCHP-ORC system has a specific capacity, which is the output upper bound. Denote

The output upper bound of the PGU, heat recovery system, auxiliary boiler, electric chiller, absorption chiller, and heating unit can be denoted as

In addition, the lower bound of the ORC, PGU, heat recovery system, auxiliary boiler, electric chiller, absorption chiller, and heating unit can be denoted as

Based on the above discussions, the bounding conditions for component output can be represented by

Then from (

Therefore, (

The objective function integrates three aspects, i.e., PEC, HTC, and CDE, into it, and it is comprehensive. Three weights

In this section, a CCHP-ORC system is installed for a hypothetical office building in Wuhan, Hubei, China, because the CCHP-ORC system is more suitable to the commercial building and the office building with low ratio of heat to power demand [

Construction parameters of the office building.

Parameters | Values |
---|---|

Each floor area | 1200 m^{2} (30m × 40m) |

| |

Each floor height | 3.2 m |

| |

Glass area | 38% in each wall |

| |

Glazing heat transfer coefficient | 4.128 W/(m^{2}K) |

| |

Exterior wall heat transfer coefficient | 0.440 W/(m^{2}K) |

| |

Interior wall heat transfer coefficient | 0.716 W/(m^{2}K) |

| |

Floor heat transfer coefficient | 2.300 W/(m^{2}K) |

| |

Roof heat transfer coefficient | 0.368 W/(m^{2}K) |

| |

Electric equipment, lights, and people densities | According to Wuhan’s energy-saving design standard |

The hourly cooling, heating, and power requirements in one year of the hypothetical office building are shown in Figure

One-year energy consumption.

To ease the performance comparison, the hourly cooling, heating, and power requirements in representative days of spring, summer, autumn, and winter are shown in Figures

Hourly energy requirements in a spring day.

Hourly energy requirements in a summer day.

Hourly energy requirements in a autumn day.

Hourly energy requirements in a winter day.

From Figures

Table

System coefficients.

Symbol | Variable | Value |
---|---|---|

| Efficiency of PGU in CCHP-ORC system | 0.35 |

| ||

| Generation efficiency SP system | 0.40 |

| ||

| Efficiency of heating unit | 0.78 |

| ||

| Efficiency of auxiliary boiler | 0.78 |

| ||

| Efficiency of heat recovery system | 0.81 |

| ||

| Coefficient of performance of ORC | 0.17 |

| ||

| Coefficient of performance of absorption chiller | 0.72 |

| ||

| Coefficient of performance of electric chiller | 2.98 |

| ||

| Transmission efficiency of local grid | 0.92 |

| ||

| | 970 |

| ||

| | 218 |

| ||

| Carbon tax rates (yuan/kW h) | 0.00002 |

| ||

| Electricity rates (yuan/kW h) | 0.642 |

| ||

| Natural gas rates (yuan/kW h) | 0.375 |

| ||

| Unit price of PGU (yuan/kW h) | 6800 |

| ||

| Unit price of auxiliary boiler (yuan/kW h) | 300 |

| ||

| Unit price of heating unit (yuan/kW h) | 200 |

| ||

| Unit price of absorption chiller (yuan/kW h) | 1200 |

| ||

| Unit price of electric chiller (yuan/kW h) | 970 |

| ||

| Unit price of ORC (yuan/kW ) | 12000 |

| ||

| Facilities’ lives (year) | 20 |

| ||

| Coefficient of PEC | 0.6 |

| ||

| Coefficient of HTC | 0.3 |

| ||

| Coefficient of CDE | 0.1 |

SQP algorithms have been proved highly effective for solving general constrained problems with smooth objective and constraint functions [

The constructed optimization problem is solved in MATLAB by using fmincon.m. The computer used to solve this problem is configured with 2.6 GHz Intel Core i5-3230M processor and 4 GB 1067 MHz memory. Time elapsed for each step of optimization is about

The performance comparison of FEL, FTL, and the proposed optimal operation strategy is shown in Figures

Comparison of three strategies in a spring day.

Comparison of three strategies in a summer day.

Comparison of three strategies in an autumn day.

Comparison of three strategies in a winter day.

The reason for the proposed optimal operation strategy performing better than FEL and FTL strategies is that both FEL and FTL strategies are inevitably wasting energy. When operating at FEL mode, electricity for the building is firstly satisfied, and then if the thermal energy provided by PGU cannot meet the thermal demand, the auxiliary boiler will be activated; if the thermal supply exceeds the thermal demand, the excess thermal energy will be wasted. When operating at FTL mode, the thermal requirements are firstly satisfied, and then if the electricity provided by PGU cannot meet the electricity demand, additional electricity should be purchased from the power grid; if the electricity provided by PGU is sufficient, a certain amount of electricity will be wasted.

The CCHP-ORC system includes ORC component as a power generator to make full use of excess thermal energy, and its integration with CCHP system has good application prospects. According to the energy requirements in representative days shown in Figures

Hourly outputs of the EC and ORC in a spring day.

Hourly outputs of the EC and ORC in a summer day.

Hourly outputs of the EC and ORC in an autumn day.

Hourly outputs of the EC and ORC in a winter day.

From Figures

Substituting the primary energy consumptions, the daily total cost, and the carbon dioxide emission into (

Equipment’s capacities.

Items | PGU | ORC | Auxiliary | Electric | Absorption | Heating |
---|---|---|---|---|---|---|

boiler | chiller | chiller | coil | |||

CCHP (kW) | 100 | - | 200 | 450 | 450 | 220 |

| ||||||

CCHP-ORC (kW) | 80 | 20 | 100 | 450 | 450 | 220 |

In Table

The performance comparisons of the CCHP-ORC system and the CCHP system are shown in Table

Performance comparisons of the CCHP-ORC system and the CCHP system.

Representative days | PEC(kWh) | DTC(Yuan) | CDE(g) | |||
---|---|---|---|---|---|---|

CCHP | CCHP-ORC | CCHP | CCHP-ORC | CCHP | CCHP-ORC | |

Spring day | 3374.1 | 3230.9 | 1021.2 | 992.5 | 821740.0 | 790230.0 |

| ||||||

Summer day | 11909.0 | 11455.0 | 3077.7 | 2986.7 | 2956700.0 | 2856900.0 |

| ||||||

Autumn day | 2247.1 | 2214.3 | 762.5 | 758.3 | 548660.0 | 543260.0 |

| ||||||

Winter day | 2626.3 | 2618.6 | 869.9 | 817.0 | 648430.0 | 607230.0 |

If we assume that the price of ORC is about 100000 Yuan, from Table

A complementary configuration of the CCHP-ORC system is investigated to further improve the utilization efficiency of the excess thermal energy from the CCHP system. A comprehensive and systematic matrix modeling approach is proposed to describe the CCHP-ORC system. The matrix model includes efficiency matrices of system components, system conversion matrix, and dispatch factors. The optimal operation strategy is obtained by solving the optimization problem. Both economic and environmental factors are considered in the objective function of the optimal operation strategy design. The weights of economic and environmental factors can be changed according to different requirements. At last, an illustrative case study is conducted to show that the effectiveness and economic efficiency of the proposed approaches outperform those obtained from conventional CCHP systems.

The main challenges of applying this method to real system are that some uncertainties in the CCHP-ORC system exist; for example, a likely source of uncertainty in the heat exchanger components of the CCHP-ORC system is fouling. The efficiencies of heat exchanger components are changed. In real system, we should consider these uncertainties by adding an error of less than 5% of the nominal value of the parameters.

The main problem of the CCHP-ORC system is high investment cost of the ORC. However the unit price of the ORC will continually decline because of the technology maturing in recent years. Therefore the CCHP-ORC system will be more attractive and valuable. In addition, all calculation in this paper is based on an accurate load profile. While, in practical applications, accurate load profile does not exist, therefore, in future work, accurate load forecasting should be considered. In a further step, excess electricity sold back feature can be considered. In recent years, with the development of the renewable energy including solar energy, wind energy, and tide energy, more and more renewable energy should be incorporated into the CCHP system to make the trigeneration system more efficient.

Combined cooling, heating, and power

Carbon dioxide emission

Coefficient of performance

Daily total cost

Evaluation criteria

Following the electric load

Following the thermal load

Hourly total cost

Organic Rankine cycles

Primary energy consumption

Power generation unit

Separation production.

Cost

Electricity

Fuel

Facility life

Installed power

Thermal energy

Efficiency

Carbon conversion factor.

Absorption chiller

Annual value

Auxiliary boiler

Cooling

Carbon

Electricity

Electric chiller

Fuel

Local power grid

Heating

Hourly value

Recovered heat cooling

Recovered heat heating

Total consumption

Organic Rankine cycles

Parasitic

Power generation unit

Capacity of PGU

Recovered.

SP system.

All research data reported in this article are available. All of these data can be obtained free of charge. If you want to get these data, you can directly contact Yufang Chang; her email is changyf@hbut.edu.cn.

The authors declare that they have no conflicts of interest.

This work has been supported in part by the Green Industry Leading Program of Hubei University of Technology (CPYF2017003), the National Nature Science Fund of China (61601176) and the National Nature Science Fund of China (41601394).