International Journal of Chemical Engineering
Volume 2018 (2018), Article ID 4342938, 6 pages
https://doi.org/10.1155/2018/4342938

Research Article

Moringa oleifera Lam. and Its Potential Association with Aluminium Sulphate in the Process of Coagulation/Flocculation and Sedimentation of Surface Water

Karina Cardoso Valverde,¹ Priscila Ferri Coldebella,¹ Marcela Fernandes Silva,¹ Letícia Nishi,¹ Milene Carvalho Bongiovani,² and Rosângela Bergamasco¹

¹Departamento de Engenharia Química, Universidade Estadual de Maringá, Av. Colombo 5790, Bloco D-90, 87020-900 Maringá, PR, Brazil
²Universidade Federal do Mato Grosso, Av. Alexandre Ferronato, 1200, 78557-267 Sinop, MT, Brazil

Correspondence should be addressed to Karina Cardoso Valverde; karinacvalverde@gmail.com

Received 4 February 2018; Accepted 5 March 2018; Published 2 May 2018

Academic Editor: Julio Sánchez Poblete

Copyright © 2018 Karina Cardoso Valverde et al. This is an open access article distributed under the Creative Commons Attribution License, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.

Abstract.

The present study aims to optimize the operational conditions in surface water coagulation/flocculation and sedimentation step, besides evaluating the association between seeds of Moringa oleifera Lam. (M. oleifera) and the synthetic coagulant aluminium sulphate for surface water treatment. The assays were performed in Jar Test using surface water from Pirapó River basin, Maringá, PR. It was observed that the operational conditions affect the coagulation/flocculation and sedimentation process efficiency. Optimal operational conditions for coagulants association are as follows: rapid mixing velocity (RMV) of 105 rpm, rapid mixing times (RMT) of 1 min, slow mixing velocity (SMV) of 30 rpm, slow mixing times (SMT) of 15 min, and sedimentation time (ST) of 15 min; this enables an improvement in the process, contributing to a reduction in synthetic coagulant aluminium sulphate demand of up to 30%, combined with an increase in M. oleifera dosage, not affecting the coagulation/flocculation and sedimentation process efficiency, considering the water pH range between 7 and 9.

1. Introduction

Currently, millions of people are exposed to dangerous levels of chemical pollutants and biological contaminants in drinking water due to the inadequate handling of urban population and industrial or agricultural wastewaters [1]. Thus, it is necessary to carry out physical, chemical, and/or microbiological processes in order to remove the impurities present in water and coagulants have been widely used in this way in conventional processes of water treatment [2].

Aluminium sulphate (Al₂(SO₄)₃18H₂O) stands out as the most used synthetic coagulant in Brazil when it comes to water treatment of public supplies as a result of its high efficiency in suspended solids removal and low cost [3]. However, its effect is strongly dependent on pH, especially in the range from 5.5 to 8 [4], and at the end of the treatment there is the possibility of a high concentration of residual aluminium remaining in water [5], which can be associated with the acceleration of degenerative processes of Alzheimer’s disease [6–8]. There is also the problem of the reaction between aluminium and the natural alkalinity present in water, which leads to a pH reduction [9]. Therefore, it is interesting to propose alternatives to reduce the quantity of the synthetic coagulant, such as the utilization of natural coagulants in water treatment.

Natural coagulants are biodegradable and present low toxicity and low levels of residual sludge production [5, 10], besides being considered health-friendly [6, 11].

Seeds of Moringa oleifera Lam. (M. oleifera) stand out as a promising natural coagulant [7, 12–15] by being considered as a low-cost and safe alternative, besides having attested efficiency in water treatment [16].

Amagloh and Benang [17] assure that when seed powder of M. oleifera is added to turbid water, the proteins present in this coagulant produce positive charges by means of electrostatic attractions with negatively charged particles [18], such as mud, clay, bacteria, and other toxic particles present in water. The flocculation process occurs when the proteins get bound to the negative charges of the particles, producing flakes and bringing together the impurities present in the water. However, the coagulation mechanism is not yet well defined among researchers.

Investigations into the behavior of seeds of M. oleifera in conjunction with aluminium salts presented promising results [11, 13, 19], attesting that M. oleifera is a feasible coagulant as a partial replacement of synthetic coagulants [16]. Valverde et al. [4] observed that the association of seeds of M. oleifera and aluminium sulphate brings about an increase in apparent color and turbidity removal efficiency of surface water. Dalen et al. [20] mention that the association of coagulants can improve water sanitation in developing countries.

Considering the operational conditions in the coagulation/flocculation process, studies carried out by Cordeiro Cardoso et al. [21] demonstrated that rapid mix, slow mix, and sedimentation do influence color and turbidity removal during the process performed with seeds of M. oleifera. Since these parameters affect the global efficiency of impurity removal in surface water, they do not have to be simply adopted, but operational conditions from laboratory studies must be established for the water treatability [22].

Pritchard et al. [15] assert that rapid mixing of a few seconds is important after the addition of a coagulant so as to assure a uniform dispersion and also increase the opportunity of contact between the particles [18]. In this way, in order to ensure coagulation efficiency, the occurrence of a uniform and intense mixture of the coagulant in water is necessary so that the contact probability between coagulant and particles is excellent before the completion of the reactions.

According to Vijayaraghavan et al. [7], there is a shortage of comprehensive studies that compare natural and synthetic coagulants association efficiency. In this way, the general objective of this work is to optimize the operational conditions of coagulation/flocculation and sedimentation step, besides evaluating the efficiency of natural coagulant seeds of M. oleifera and synthetic coagulant aluminium sulphate association in surface water treatment, by means of the alteration of coagulants dosage and coagulation pH, using coagulation diagram tools.

2. Materials and Methods

Surface water collected at the Water Treatment Plant (Sanepar) of the city, coming from Pirapó River basin, Maringá city, Paraná state, Brazil, was characterized by means of the following quality parameters: apparent color and compounds with UV254 nm absorption (DR 5000 Hach spectrophotometer), turbidity (2100P Hach turbidimeter), total dissolved solids (TDS), and pH (Thermo Scientific Orion VSTAR92 Versa Star pH meter).

The coagulation/flocculation assays were carried out in Jar Test, Nova Ética, 218/LDB0 of six jars, with rotation regulator of mixer shafts, in duplicate, in 700 mL recipients of surface water.

2.1. Coagulants Preparation

For the preparation of synthetic coagulant standard solution, 1 g of aluminium sulphate hydrate (Vetec) was dissolved in distilled water and the volume was brought to 100 mL in order to obtain a 1% w·v⁻¹ solution.

In order to obtain M. oleifera powdered coagulant, 15 g of seeds ordered from Aracaju, SE, were manually peeled, ground in a blender (NL-41 Mondial), and dried in a forced air buffer (Digital Timer SX CR/42) at 40°C until constant weight was observed [17].

2.2. Operational Conditions of Coagulation/Flocculation and Sedimentation Process

In this step, coagulant dosages added during the assays were adapted from values cited in the literature, namely, 25 mg·L⁻¹ for aluminium sulphate [23, 24] and 50 mg·L⁻¹ for seeds of M. oleifera [25].

Operational conditions of coagulation/flocculation and sedimentation process used in the association of seeds of M. oleifera and aluminium sulphate coagulants are presented on Table 1. It is worth mentioning that these values are based on optimal operational conditions of seeds of M. oleifera, earlier studied by Madrona et al. [10] and Cordeiro Cardoso et al. [21], and of aluminium sulphate, obtained through information at Sanepar, thus adopting real operational conditions used at the Water Treatment Plant in Maringá city.

Table 1: Operational conditions of coagulation/flocculation and sedimentation process.

ASSAY
1
2
3
4
5
6
7
8
9
10
11
12
13
14
15
16
17
18
19
20
21
22
23
24
25
26
27

RMV (rpm)
100
105
110
100
105
110
100
105
110
100
105
110
100
105
110
100
105
110
100
105
110
100
105
110
100
105
110

RMT (min)
1
1
1
2
2
2
3
3
3
1
1
1
2
2
2
3
3
3
1
1
1
2
2
2
3
3
3

SMV (rpm)
15
15
15
15
15
15
15
15
15
30
30
30
30
30
30
30
30
30
45
45
45
45
45
45
45
45
45

SMT (min)
15
15
15
15
15
15
15
15
15
15
15
15
15
15
15
15
15
15
15
15
15
15
15
15
15
15
15

SMV: slow mixing velocity; RMV: rapid mixing velocity; SMT: slow mixing times; RMT: rapid mixing times.

2.3. Coagulation Diagrams

Coagulation diagrams developed on 3DField 3.5.3.0. software were created from coagulation pH variation and seeds of M. oleifera and aluminium sulphate association dosage by evaluating the removal efficiency of apparent color, turbidity, and compounds with UV254 nm absorption.

Surface water pH used in the assays was adjusted in the range between 4 and 10 with 0.1 mol·L⁻¹ and 1 mol·L⁻¹ sodium hydroxide (NaOH) and 0.1 mol·L⁻¹ and 1 mol·L⁻¹ hydrochloric acid (HCl).

For this step of the work, coagulants dosages specified in Table 2 were used, according to adaptations from the methodology proposed by Nwaiwu and Bello [19].

Table 2: Coagulants dosage in association.

Point
% coagulant (Al₂(SO₄)₃⋅18H₂O/
M. oleifera)
Coagulant dosage (mg⋅L⁻¹)

Al₂(SO₄)₃⋅18H₂O
Seeds of M. oleifera

1
0%/100%
0
50

2
10%/90%
2.5
45

3
20%/80%
5
40

4
30%/70%
7.5
35

5
40%/60%
10
30

6
50%/50%
12.5
25

7
60%/40%
15
20

8
70%/30%
17.5
15

9
80%/20%
20
10

10
90%/10%
22.5
5

11
100%/0%
25
0

2.4. Coagulation/Flocculation and Sedimentation Process Evaluation

After completing the coagulation/flocculation and sedimentation process, 15 mL of treated water was collected for results evaluation, which was carried out on the basis of percentage reduction in apparent color, turbidity, and compounds with UV254 nm absorption.

2.5. Statistical Analysis

For the purpose of comparing the results obtained in the coagulation/flocculation and sedimentation assays, Analysis of Variance (ANOVA) and multiple comparison of means, or Tukey’s Test, were carried out, using confidence interval of 95%, for significant values < 0.05, in order to verify significant differences by means of SISVAR version 5.3 statistical program [26].

In order to assess the removal efficiency of quality parameters after the water clarification process, a factorial delineation was used, whose factors were as follows: assays (27 variations for slow and rapid mixing velocity (SMV and RMV) and slow and rapid mixing times (SMT and RMT) and sedimentation times (four ST), with two replications [18].

3. Results and Discussions

Table 3 presents the characterization of surface water.

Table 3: Characterization of surface water.

Quality parameter
Apparent color
Turbidity

TDS
pH

Surface water
406 uH
73.9 NTU
0.285 cm⁻¹
115.33 mg⋅L⁻¹
7.817

3.1. Operational Conditions: Optimization Step of the Coagulation/Flocculation and Sedimentation Process

By evaluating the results obtained by means of Tukey’s Test, it is possible to observe that there was no significant statistical difference concerning operational conditions presented in Table 4.

Table 4: Values ​​of removal efficiency for the best operating conditions in association of seeds of M. oleifera and aluminium sulphate.

Parameters
Removal efficiency (%)

RMV
(rpm)
RMT
(min)
SMV
(rpm)
SMT
(min)
ST
(min)
Apparent color
Turbidity

105
1
30
15
15–45
92.3–93.6
91.0–92.0
75.5–76.3

110
1
30
15
45
90.9
90.0
72.4

100
2
30
15
30–45
91.2–92.5
92.2–92.9
74.3–75.2

105
3
30
15
45–60
93.8–95.4
92.8 – 94.1
77.2

110
3
30
15
60
92.9
92.6
79.0

110
1
45
15
60
92.8
91.2
76.1

105
2
45
15
45–60
93.1–93.3
92.9–93.3
75.3–75.8

100
3
45
15
45
91.0
91.0
74.0

105
3
45
15
45–60
92.9–93.2
92.9–93.0
78.6

SMV: slow mixing velocity; RMV: rapid mixing velocity; SMT: slow mixing times; RMT: rapid mixing times; ST: sedimentation times.

Earlier studies [2, 4] have shown results of apparent color and turbidity removal with 60 min and 120 min sedimentation time (ST), using saline and aqueous extract of M. oleifera, respectively, as the sole coagulant in the coagulation/flocculation and sedimentation process. The elapsed time required for sedimentation when using M. oleifera powdered seed as the sole coagulant is higher than that of M. oleifera and aluminium sulphate association [8, 19]. Bongiovani et al. [27] confirm that the utilization of a polymer along with seeds of M. oleifera improves removal efficiency of quality parameters and it increases the size of flocs, thus diminishing significantly the overall sedimentation time.

Several results are presented in Table 4. However, ST lies in the range from 30 min to 60 min. Since 15 min is the standard elapsed time used at Water Treatment Plants [27], optimal operational conditions for seeds of M. oleifera and aluminium sulphate association are as follows: rapid mixing velocity (RMV) of 105 rpm, rapid mixing time (RMT) of 1 min, slow mixing velocity (SMV) of 30 rpm, slow mixing time (SMT) of 15 min, and sedimentation time (ST) of 15 min.

Figures 1, 2, and 3 present assay results for 15 min ST concerning efficiency removal of apparent color, turbidity, and compounds with UV254 nm absorption.

Figure 1: Removal efficiency of M. oleifera and aluminium sulphate for apparent color.

Figure 2: Removal efficiency of M. oleifera and aluminium sulphate for turbidity.

Figure 3: Removal efficiency of M. oleifera and aluminium sulphate for compounds with UV254 nm absorption.

By evaluating the results obtained for the three quality parameters studied, one can conclude that the optimal operational conditions for seeds of M. oleifera and aluminium sulphate association are: RMV of 105 rpm, RMT of 1 min, SMV of 30 rpm, SMT of 15 min, and ST of 15 min.

3.2. Coagulation Diagrams Construction Step

Coagulation diagrams are constructed from removal efficiency of the quality parameters evaluated, considering that the best results are identified by dark-colored regions.

Figures 4, 5, and 6 show coagulation diagrams that evaluate removal efficiency of apparent color, turbidity, and compounds with UV254 nm absorption, respectively.

Figure 4: Coagulation diagrams with curves of apparent color removal in percentage (%).

Figure 5: Coagulation diagrams with curves of turbidity removal in percentage (%).

Figure 6: Coagulation diagrams with curves of compounds with absorption removal in percentage (%).

As for coagulants association, in a general way, it is possible to observe in the coagulation diagrams that as the aluminium sulphate dosage increases, the coagulation effect is enhanced.

Valverde et al. [4] ascertained that the association of natural and synthetic coagulants enables an increase in the removal efficiency of apparent color and turbidity of the water under scrutiny, thus corroborating the study of Dalen et al. [20], which suggests that aluminium sulphate and powdered M. oleifera present better synergic characteristics than the ones described in the utilization of M. oleifera as the sole coagulant. This occurrence can be evidenced in the coagulation diagrams presented.

Considering the water pH range between 7 and 9, it can be asserted that coagulation addition with dosages higher than 17.5 mgL⁻¹ aluminium sulphate/15 mgL⁻¹ seeds of M. oleifera (point 8) would be interesting for the attainment of removal efficiency of about 75.0% for color and turbidity and 70.0% for compounds with UV254 nm absorption.

It is possible to achieve a 30% reduction in the consumption of synthetic coagulant aluminium sulphate combined with an increase in M. oleifera dosage without affecting the efficiency of the process. Therefore, research in this area must continue in order to obtain water that meets the required potability standard.

4. Conclusions

It was observed that the operational conditions affect the efficiency of the coagulation/flocculation and sedimentation process. Coagulant aluminium sulphate, applied in combination with seeds of M. oleifera, enables an improvement in sedimentation time of the overall process, so that 15 min are enough. Optimal operational conditions for coagulants association are as follows: RMV of 105 rpm, RMT of 1 min, SMV of 30 rpm, and SMT of 15 min.

For the water pH range between 7 and 9, the association of natural and synthetic coagulants with dosages higher than 17.5 mg·L⁻¹ aluminium sulphate/15 mg·L⁻¹ seeds of M. oleifera presents synergic characteristics, and removal efficiency of about 75.0% for color and turbidity and of 70.0% for compounds with UV254 nm absorption is obtained.

The use of seeds of M. oleifera contributes to a reduction of up to 30% in the required demand of aluminium sulphate, without affecting the efficiency of coagulation/flocculation and sedimentation process, besides being an interesting environmental option nowadays.

Data Availability

The data used to support the findings of this study are available from the corresponding author upon request.

Conflicts of Interest

The authors declare that there are no conflicts of interest.

Acknowledgments

The authors would like to acknowledge Universidade Federal de Sergipe (UFS) for seeds of M. oleifera seeds and Sanepar for samples of surface water. They would also like to acknowledge CAPES for financial support in the form of the scholarships received.

References

WHO, World Health Organization, Water Quality and Health Strategy: 2013-2020, 2013.

G. S. Madrona, G. B. Serpelloni, A. M. Salcedo Vieira, L. Nishi, K. C. Cardoso, and R. Bergamasco, “Study of the effect of Saline solution on the extraction of the Moringa oleifera seed's active component for water treatment,” Water, Air, & Soil Pollution, vol. 211, no. 1-4, pp. 409–415, 2010.

P. A. Lo Monaco, A. T. Matos, I. C. Ribeiro, F. d. Nascimento, and A. P. Sarmento, “Utilização de Extrato de Sementes de Moringa como Agente Coagulante no Tratamento de Água para Abastecimento e Águas Residuárias,” Ambi-Agua, vol. 5, no. 3, pp. 222–231, 2010.

K. C. Valverde, L. C. K. Moraes, M. C. Bongiovani, F. P. Camacho, and R. Bergamasco, “Coagulation diagram using the Moringa oleifera Lam and the aluminium sulphate, aiming the removal of color and turbidity of water,” Acta Scientiarum - Technology, vol. 35, no. 3, pp. 485–489, 2013.

S. Kawamura, “Effectiveness of natural polyelectrolytes in water treatment,” Journal - American Water Works Association, vol. 83, no. 10, pp. 88–91, 1991.

T. Okuda, A. U. Baes, W. Nishijima, and M. Okada, “Improvement of extraction method of coagulation active components from Moringa oleifera seed,” Water Research, vol. 33, no. 15, pp. 3373–3378, 1999.

G. Vijayaraghavan, T. Sivakumar, and A. Vimal Kumar, “Application of plant based coagulants for waste water treatment,” International Journal of Advanced Engineering Research and Studies, vol. 1, no. 1, pp. 88–92, 2011.

K. Ravikumar and A. K. Sheeja, “Water clarification using Moringa oleifera seed coagulant,” in Proceedings of the 2012 International Conference on Green Technologies, ICGT 2012, pp. 64–70, India, December 2012.

M. R. Gidde and A. R. Bhalerao, “Optimisation of Physical Parameters of Coagulation-Flocculation Process in Water Treatment, JERAD,” Journal of Environmental Research and Development, vol. 6, no. 1, pp. 99–110, 2011.

G. S. Madrona, I. G. Branco, V. J. Seolin, B. D. A. A. Filho, M. R. Fagundes-Klen, and R. Bergamasco, “Evaluation of extracts of moringa oleifera lam seeds obtained with nacl and their effects on water treatment,” Acta Scientiarum - Technology, vol. 34, no. 3, pp. 289–293, 2012.

J. R. Rodríguez-Núñez, D. I. Sánchez-Machado, J. López-Cervantes, J. A. Núñez-Gastélum, R. G. Sánchez-Duarte, and M. A. Correa-Murrieta, “Moringa oleifera Seed Extract in the Clarification of Surface Waters,” International Journal of Engineering Pedagogy, vol. 2, no. 11, pp. 17–21, 2012.

A. Ndabigengesere and K. S. Narasiah, “Influence of operating parameters on turbidity removal by coagulation with moringa oleifera seeds,” Environmental Technology (United Kingdom), vol. 17, no. 10, pp. 1103–1112, 1996.

J. K. Abaliwano, K. A. Ghebremichael, and G. L. Amy, “Application of the purified Moringa oleifera coagulant for surface water treatment, watermill work,” WaterMill Work. Paper Serie, vol. 5, pp. 1–19, 2008.

E. N. Ali, S. A. Muyibi, H. M. Salleh, M. Z. Alam, and M. R. Salleh, “Production of Natural Coagulant from Moringa Oleifera Seed for Application in Treatment of Low Turbidity Water,” Journal of Water Resource and Protection, vol. 02, no. 03, pp. 259–266, 2010.

M. Pritchard, T. Craven, T. Mkandawire, A. S. Edmondson, and J. G. O'Neill, “A comparison between Moringa oleifera and chemical coagulants in the purification of drinking water - An alternative sustainable solution for developing countries,” Physics and Chemistry of the Earth, vol. 35, no. 13-14, pp. 798–805, 2010.

M. Awad, H. Wang, and F. Li, “Preliminary study on combined use of Moringa seeds extract and PAC for water treatment,” Research Journal of Recent Sciences, vol. 2, no. 8, pp. 52–55, 2013.

F. K. Amagloh and A. Benang, “Effectiveness of Moringa oleifera seed as coagulant for water purification,” African Journal of Agricultural Research, vol. 4, no. 2, pp. 119–123, 2009.

K. Cardoso Valverde, P. Ferri Coldebella, and R. Bergamasco, “Otimização das condições de operação no processo de clarificação de água superficial por meio da associação dos coagulantes moringa oleifera lam e cloreto férrico,” Periódico Eletrônico Fórum Ambiental da Alta Paulista, vol. 9, no. 11, pp. 46–54, 2013.

N. E. Nwaiwu and A. A. Bello, “Effect of Moringa oleifera-alum Ratios on Surface Water Treatment in North East Nigeria,” Research Journal of Applied Sciences, Engineering and Technology, vol. 3, no. 6, pp. 505–512, 2011.

M. Dalen, J. Pam, A. Izang, and R. Ekele, “Synergy Between Moringa oleifera Seed Powder And Alum In The Purification of Domestic Water,” The Scientific World Journal, vol. 4, no. 4, 2010.

K. Cordeiro Cardoso, R. Bergamasco, E. Sala Cossich, and L. C. Konradt Moraes, “Otimização dos tempos de mistura e decantação no processo de coagulação/floculação da água bruta por meio da Moringa oleifera Lam,” Acta Scientiarum. Technology, vol. 30, no. 2, 2008.

M. de Julio, I. Volski, D. A. Fioravante, O. Selhorst Filho, and F. I. Oroski, “Avaliação da Viabilidade Técnica do Emprego da Tecnologia de Filtração Direta no Tratamento da Água Bruta Afluente à ETA do Município de Ponta Grossa, PR,” Ciência & Engenharia, vol. 18, no. 1, pp. 21–30, 2009.

A. Baghvand, A. D. Zand, N. Mehrdadi, and A. Karbassi, “Optimizing coagulation process for low to high turbidity waters using aluminum and iron salts,” American Journal of Environmental Sciences, vol. 6, no. 5, pp. 442–448, 2010.

H. F. Makki, A. F. Al-Alawy, N. N. Abdul-Razaq, and M. A. Mohammed, “Using Aluminum Refuse as a Coagulant in the Coagulation and Flocculation Processes,” Iraqi Journal of Chemical and Petroleum Engineering, vol. 11, no. 3, pp. 15–22, 2010.

R. Joshua and V. Vasu, “Characteristics of Stored Rain Water and its Treatment Technology Using Moringa seeds,” International Journal of Life science and Pharma Research, vol. 2, no. 1, pp. 154–175, 2013.

D. F. Ferreira, “Sisvar: a computer statistical analysis system,” Ciência e Agrotecnologia, vol. 35, no. 6, pp. 1039–1042, 2011.

M. C. Bongiovani, F. P. Camacho, L. Nishi et al., “Improvement of the coagulation/flocculation process using a combination of Moringa oleifera Lam with anionic polymer in water treatment,” Environmental Technology (United Kingdom), vol. 35, no. 17, pp. 2227–2236, 2014.