International Journal of Distributed Sensor Networks

Volume 2013 (2013), Article ID 189840, 7 pages

http://dx.doi.org/10.1155/2013/189840

Research Article

Design of a Room Monitoring System for Wireless Sensor Networks

Sun-Kuk Noh,¹ Kuk-Se Kim,² and Yoo-Kang Ji³

¹Department of Photoelectronics, Chosun College of Science & Technology, Gwangju, Republic of Korea

²NANOOMTECH Co. Ltd., Gwangju, Republic of Korea

³Department of Information & Communication Engineering, Dongshin University, Naju, Jeonnam, Republic of Korea

Received 24 May 2013; Accepted 13 July 2013

Academic Editor: Tai-hoon Kim

Copyright © 2013 Sun-Kuk Noh et al. This is an open access article distributed under the Creative Commons Attribution License, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.

Abstract.

In wireless sensor networks (WSN) systems, various indoor environmental parameters can be monitored in real time by an RF wireless sensor module. A wireless sensor module with several sensors is developed for an indoor environment monitoring system. ZigBee is a wireless standard for personal area network (PAN) sensor monitoring and control, also known as IEEE 802.15.4. In this paper, we designed a wireless sensor module that had a ZigBee communication module and a sensor module for monitoring a room or an office environment using WSN. The sensor module has various enlargements for various types of sensors, for example, a humidity sensor, temperature sensor, and O₂ and CO₂ sensors. Using ZigBee technology of 2.4 GHz Industrial, Scientific, and Medical (ISM) band, we could monitor the information from terminal PC modules that are attached to the wall of an office or a room. A wireless sensor device was developed to circuit schematic using PowerPCB tool PADS and made it a printed circuit board (PCB). From the results of our tests, we confirmed that the designed wireless sensor module and room monitoring system can supply a comfortable environment for people by monitoring the indoor environment.

1. Introduction

In the near future, all electronic appliances at home will be networked: PCs, telephones, stereos, refrigerators, and even washing machines. Heating and air conditioning, previously controlled by a single, fixed, manual thermostat, can now be managed by an intelligent controller with remote access capabilities [1, 2]. Recently, the use of residential air conditioning has become widespread owing to increasing living standards and expectations for comfort. The control and monitoring of indoor atmospheric conditions represents an important task with the aim of ensuring suitable working and living spaces for people. However, comprehensive air quality monitoring, which includes monitoring humidity, temperature, O₂, CO₂, and flying dust particle density, is not easily monitored and controlled [3, 4]. In addition, several difficulties due to air pollution from industrial development, new house syndrome, atopic diseases, and swine flu complicate air quality monitoring [4]. In particular, humans require comfortable environments because the necessity of domestic air administration is enlarged [5]. Recent progress in wireless technologies has led to a renovation in home automation which makes it possible to upgrade environmental controls in rooms. One of the popular examples is the practical application of wireless sensor networks (WSN), which is now used in many areas, such as environmental monitoring, healthcare, home automation, and intelligent transportation systems. In particular, there are more opportunities to build wireless monitoring systems using ZigBee with the number of wireless sensor networks available. ZigBee is a wireless standard for personal area network (PAN) sensor monitoring and control, also known as IEEE 802.15.4 which is a communications standard designed for low-power short-range communications between wireless devices [6]. Many prototypes for home monitoring systems have been proposed [7–17].

In this study, we design a room monitoring system. A wireless sensor module with optimal communication conditions is designed, and it has a ZigBee communication module and a sensor module. A sensor module has various sensors that monitor temperature, humidity, O₂, CO₂, and atmospheric pressure. Indoor air quality in a room or an office can be monitored and efficiently controlled by a ZigBee module. We can monitor sensing information from terminal PC modules that are attached to the wall of an office or a room. A wireless sensor device is developed to circuit schematic using PowerPCB tool and PADS and make it a printed circuit board (PCB). From the results of our tests, we confirm that the designed wireless sensor module and room monitoring system can supply a comfortable environment for people by the monitoring indoor environment.

2. Room Environmental Monitoring Systems

The concept for the room environmental monitoring system is shown in Figure 1. Several sensors such as a temperature sensor, humidity sensor, CO₂ sensor, and an atmospheric pressure sensor were built on an RF transmitter board for monitoring the indoor environmental conditions. These input sensors were chosen in consideration of the parameters that maintain comfort for a human being.

Figure 1: Concept for the indoor environmental system.

The feasibility of the wireless sensor module application as a room monitoring system was tested. The wireless sensor module has only one transmitter and receiver; however, multiple sensors can be attached to the module. To simplify the system, the transmitter and receiver were separately designed and fabricated using a ZigBee chip. In the transmitter sensor module, most of analog sensors were added, so that typical commercialized sensors can be used conveniently. The sensor module, which transfers the sensor data to the receiver by an RF signal, has a very simple structure that includes a ZigBee chip, a commercial 2.4 GHz RF transmitter chip, and several normal analog or digital sensors on a PCB board. Thus, we can easily attach the wireless transmitter module to the wall of a room or at a convenient place. Figure 1 shows the system configuration used in this study. The environment of a room or an office was monitored.

Commercial discrete sensor devices can be built in a socket module for analog and digital sensors. The digital sensor data were converted to data packets before transmission to the receiver by the RF signal. The designed data format of the packet is shown in Figure 2. The packet was composed of an ms preamble, 3-bit sensor address, and 8-bit sensor data. In the designed system, a maximum of eight sensors were used because we limited the address length in the data packet.

Figure 2: Packet. (i) Length (1 byte): packet, (ii) data seq-no (1 byte): packet number, (iii) dest (2 byte): destination address, (iv) src (2 byte): source address, and (v) location value (1 byte): receive signal value.

The continuous data packet stream of the receiver that was transferred from the transmitter was filtered to recover the original sensor data and then transmitted to an 8051 microcontroller board through an RS-232 serial communication method.

2.1. ZigBee Communication Module

In this study, we designed and fabricated a ZigBee system as a communication module to form the USN environment. The ZigBee communication module is a Texas Instruments (TI), CC2431 2.4 GHz IEEE 802.15.4 RF chip. The CC2431 has 128 Kb of system flash memory on-chip and an internal 8051 core [19]. Figure 2 shows the ZigBee communication module.

The size of the ZigBee communication module is 38 mm × 38 mm, with an average output of 27 mA (RX) and 25 mA (TX) at 32 MHz and a receive range of 100 m ± 20 m. The Titanis 2.4 GHz Swivel SMA antenna is used [20].

The ZigBee communication module is composed by low electric power. Further, the module is designed efficiently to present the remaining battery life, internal temperature, and location with the contained battery monitor, temperature sensor, and internal location engine (see Figure 3).

Figure 3: ZigBee communication module (38 mm × 40 mm).

2.2. Sensor Module

In Figure 4, the integrated sensor module for efficient maintenance of comfortable indoor environment consisted of humidity, temperature, O₂, CO₂, and atmospheric pressure sensors. Table 1 shows the sensor range.

Table 1: Sensor range.

Sensor
Measurement
Range

SHT7x
Temperature
−40°C +123.8°C

Humidity
0~100% RH

SS1118
O₂
0~100%

GHFS410P1
CO₂
200~30,000 ppm

SMBA-1000
Atmospheric pressure
300~1100 mbar

(a) Front

(b) Back

Figure 4: Sensor module.

3. Developed Module Test

The test devices include a power supply, an oscilloscope, a spectrum analyzer, and a PC. Sensor data from each sensor are monitored from the client PC.

3.1. ZigBee Communication Module Operating Frequency Test

The IEEE 802.15.4 standard which is shown in Table 2 for wireless personal area networks (WPANs) specifies the physical (PHY) at the 868 MHz, 915 MHz, and 2.4 GHz Industrial, Scientific, and Medical (ISM) band. We selected the 2.4 GHz Industrial, Scientific, and Medical (ISM) band (see Figure 6) [6].

Table 2: IEEE 802.15.4 PHY.

Frequency band (GHz)
Parameters

Chip rate (kchip/s)
Modulation
Data rate (kbps)
Symbol
Transmission power
Receiver sensitivity

2.4
2000
O-QPSK
250
16-ary orthogonal
3 dBm
85 dBm

In Figure 5, we found that the number of channels is 16, the channel interval is 5 MHz, and the channel output power is not the same. In Table 3, we find that 2425 MHz was the best operating frequency.

Table 3: Test results for the ZigBee Gain.

Operating frequency (MHz)
Peak gain (dBi)
Average gain (dBi)
Efficiency (%)

2405
1.65
−3.15
48.52

2425
3.12
−1.64
68.61

2445
2.44
−2.09
61.91

2465
2.39
−2.08
62.04

2480
2.29
−2.24
59.84

Figure 5: ZigBee 2.4 GHz band.

Figure 6: ZigBee operating frequency range test.

3.2. ZigBee Communication Module Distance Test

ZigBee communication module distance test was used as a path loss. Path Loss is equation (1), and Table 4 is path loss exponents for indoor environments:

Table 4: Path loss exponents for indoor environments [18].

Room environment
Path loss exponents

Large open
2

Furnished
3

Densely furnished
4

Different floors
5

The PT is transmission power; SR is receiver sensitivity. The log-distance path loss model is another site general model and it is given by [21]

The is path loss exponent, is distance, and is reference distance close to transmitter.

According to (1) and Table 2, we find  dBm and show the distance with 2.4 GHz band using ~5 in Figure 7.

Figure 7: 2.4 GHz distance with  dBm.

In Figure 7, we find that distance is 11 m at , and in Figure 8, we select that it is reference maximum distance and measured at indoor office (10 m × 8 m).

(a)

(b)

Figure 8: The measurement of distance at our office.

In Figure 9, measurement result is closed to because our office is a densely furnished room.

Figure 9: 2.4 GHz path loss in our office.

3.3. Experimental Results

Figure 10 shows a test the monitoring system using the designed wireless sensor module.

Figure 10: Test of monitoring system of the designed wireless sensor module.

Figure 11 shows the monitored values of the sensor from an actual experiment using the designed sensor module in laboratory. -axis is second time.

(a) Temperature (blue, °C) and humidity (red, %RH)

(b) O₂ (0.001%)

(c) CO₂ (ppm)

(d) Atmospheric pressure (bar)

Figure 11: Experimental sensor data.

Figure 12 shows the designed wireless senor module and the designed room monitoring system.

(a) Wireless sensor module

(b) Room monitoring system

Figure 12: A designed room monitoring system.

4. Conclusions

In the past, only toxic gases were monitored for the safety of humans in a house; however, the monitoring of various room conditions allows for a comfortable life with modern technology. Comfort can be attained by complex monitoring and controlling of many parameters, including temperature, humidity, CO₂ concentration, O₂ concentration, and the density of fine particle dust. Thus, a wireless multisensor module for the monitoring of indoor room conditions is a very important home networking technology.

In this study, we designed a wireless sensor module that had a designed ZigBee communication module and a sensor module that uses WSN for monitoring a room environment. Most of the system components were designed and fabricated for system optimization. We utilized an integrated sensor module consisting of sensors that are used in industry to check the atmospheric pressure, O₂, CO₂ concentration, and an imported ZigBee communication system. Using ZigBee technology of 2.4 GHz Industrial, Scientific, and Medical (ISM) band in the IEEE 802.15.4 standard, we could monitored the information from terminal PC modules that are attached to the wall of an office or a room. A wireless sensor device was developed to circuit schematic using PowerPCB tool and PADS and made it a printed circuit board (PCB). From the results of our tests, we confirmed that the designed wireless sensor module and room monitoring system can supply a comfortable environment for people by monitoring indoor environment. Hereafter, we are going to study about the power consumption of this designed WSN monitoring system.

References

Z. Lin and S. Deng, “The outdoor air ventilation rate in high-rise residences employing room air conditioners,” Building and Environment, vol. 38, no. 12, pp. 1389–1399, 2003.

F. Calvino, M. La Gennusa, G. Rizzo, and G. Scaccianoce, “The control of indoor thermal comfort conditions: introducing a fuzzy adaptive controller,” Energy and Buildings, vol. 36, no. 2, pp. 97–102, 2004.

W. Y. Chung and J. W. Lim, “Patterning of thin tin oxide film with nano-size particle for two-dimensional micro-gas sensor array,” Current Applied Physics, vol. 3, no. 5, pp. 413–416, 2003.

D. Kolokotsa, K. Niachou, V. Geros, K. Kalaitzakis, G. S. Stavrakakis, and M. Santamouris, “Implementation of an integrated indoor environment and energy management system,” Energy and Buildings, vol. 37, no. 1, pp. 93–99, 2005.

W. Y. Chung and S. J. Oh, “Remote monitoring system with wireless sensors module for room environment,” Sensors and Actuators B, vol. 113, no. 1, pp. 64–70, 2006.

K. T. Le, “Designing a ZigBee-ready IEEE 802.15.4-compliant radio transceiver,” pp. 42–50, 2004, http://defenseelectronicsmag.com/site-files/defenseelectronicsmag.com/files/archive/rfdesign.com/mag/411rfdf4.pdf

C. Suh and Y. B. Ko, “Design and implementation of intelligent home control systems based on active sensor networks,” IEEE Transactions on Consumer Electronics, vol. 54, no. 3, pp. 1177–1184, 2008.

J. Han, H. Lee, and K. R. Park, “Remote-controllable and energy-saving room architecture based on ZigBee communication,” IEEE Transactions on Consumer Electronics, vol. 55, no. 1, pp. 264–268, 2009.

K. S. Kim, J. G. Lee, S. S. Ahn, and J. Lee, A Study on USN Multi-Modal Sensor Fusion Technique for Intelligent Air Conversions Digital Home Appliances, MITA, 2010.

K. S. Kim, J. Z. Song, C. Zhang, T. S. Yun, and S. K. Noh, A Study on Home Indoor Environment System JCICT & the 1st Yellow Sea International Conference on Ubiquitous Computing (YES-ICUC), 2011.

J. Zhang, G. Song, H. Wang, and T. Meng, “Design of a wireless sensor network based monitoring system for home automation,” in Proceedings of the International Conference on Future Computer Sciences and Application (ICFCSA '11), pp. 57–60, Hong Kong, China, June 2011.

H. Xianzhe, “Room temperature and humidity monitoring and energy-saving system,” in Proceedings of the 6th International Conference on Computer Science and Education (ICCSE '11), pp. 537–540, Singapore, August 2011.

M. M. Rahman, M. I. Abdullah, and M. S. Hossain, “Level based path selection technique in large WSN for hierarchical architecture,” International Journal of Advanced Science and Technology, vol. 32, pp. 33–44, 2011.

D. Gupta and A. K. Sharma, “On performance evaluation of WSN routing protocols for MICA and MICAz using different radio models,” International Journal of Energy, Information and Communications, vol. 2, no. 4, pp. 181–194, 2011.

S. Hwang and D. Yu, “Remote monitoring and controlling system based on ZigBee networks,” International Journal of Software Engineering and Its Applications, vol. 6, no. 3, pp. 35–42, 2012.

J. Yap and Y. H. Noh, “A ZigBee-based home control system using OSGi management platform,” International Journal of Smart Home, vol. 6, no. 4, pp. 15–28, 2012.

H. Zhang and Y. Liu, “Study and design of adaptive environment control system for mobile base stations,” in Proceedings of the International Conference on Control Engineering and Communication Technology (ICCECT '12), pp. 426–429, Liaoning, China, December 2012.

T. Lkhagvatseren and F. Hruska, “Path loss aspects of a wireless communication system for sensors,” International Journal of Computers and Communications, vol. 5, no. 1, 2011.

http://www.ti.com/product/cc2431

http://docs-europe.electrocomponents.com/webdocs/09d8/0900766b809d8a5d.pdf

T. S. Rappaport, Wireless Communications Principles and Practice, Prentice-Hall, Upper Saddle River, NJ, USA, 2nd edition, 2002.