Journal of Applied Mathematics

Volume 2013 (2013), Article ID 879078, 9 pages

http://dx.doi.org/10.1155/2013/879078

Research Article

Applying Hybrid PSO to Optimize Directional Overcurrent Relay Coordination in Variable Network Topologies

Ming-Ta Yang¹ and An Liu2,3

¹Department of Electrical Engineering, St. John’s University, 499, Section 4, Tam King Road, Tamsui District, New Taipei 25135, Taiwan

²Department of Computer Science and Information Engineering, St. John’s University, 499, Section 4, Tam King Road, Tamsui District, New Taipei 25135, Taiwan

³Graduate Institute of Computer and Communication Engineering, National Taipei University of Technology, No. 1, Section 3, Chunghsiao E. Road, Taipei 10608, Taiwan

Received 4 December 2012; Revised 20 January 2013; Accepted 25 January 2013

Academic Editor: Frank Werner

Copyright © 2013 Ming-Ta Yang and An Liu. This is an open access article distributed under the Creative Commons Attribution License, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.

Abstract.

In power systems, determining the values of time dial setting (TDS) and the plug setting (PS) for directional overcurrent relays (DOCRs) is an extremely constrained optimization problem that has been previously described and solved as a nonlinear programming problem. Optimization coordination problems of near-end faults and far-end faults occurring simultaneously in circuits with various topologies, including fixed and variable network topologies, are considered in this study. The aim of this study was to apply the Nelder-Mead (NM) simplex search method and particle swarm optimization (PSO) to solve this optimization problem. The proposed NM-PSO method has the advantage of NM algorithm, with a quicker movement toward optimal solution, as well as the advantage of PSO algorithm in the ability to obtain globally optimal solution. Neither a conventional PSO nor the proposed NM-PSO method is capable of dealing with constrained optimization problems. Therefore, we use the gradient-based repair method embedded in a conventional PSO and the proposed NM-PSO. This study used an IEEE 8-bus test system as a case study to compare the convergence performance of the proposed NM-PSO method and a conventional PSO approach. The results demonstrate that a robust and optimal solution can be obtained efficiently by implementing the proposal.

1. Introduction

The aim of relay coordination in power systems is to quickly isolate fault areas to preserve service throughout most of the power systems. Protection relays play a primary role in the coordination of power system protection, covering five basic facets: reliability, selectivity, speed of operation, simplicity, and economic feasibility. Engineers must consider these five aspects as a group to overcome the problem of power system protection. During the past 40 years, the technology used in the creation and use of relays for power system protection has seen tremendous progress. Directional overcurrent relays (DOCRs) have been applied to the design of economical alternatives for the primary or backup protection of power systems. Most work on protection coordination is geared toward determining the values of time dial setting (TDS) and plug setting (PS) of the DOCRs [1].

Many studies on optimization have addressed the coordination of DOCRs. Since Urdaneta et al. [2] first introduced a methodology based on optimization principles, these techniques have been widely investigated to deal with the problem of optimal coordination of DOCRs in interconnected power networks. Urdaneta et al. [2] applied an iterative approach, the Gauss-Seidel method, to solve steady-state fixed configurations DOCRs optimization problems, and decomposition technique and hierarchical coordination procedure were adopted to find DOCRs optimal settings under steady-state multiple configurations. This study applies linear programming technique to determine the DOCRs optimal settings. TDS are calculated given the PS; then new PS are computed after the TDS are found, and this process is repeated until convergence is achieved. Birla et al. [3] adopted the sequential quadratic programming method to simultaneously optimize all TDS and PS for each DOCR of the system. The constraints based on the near-end faults for small systems were considered, when the objective function optimal values were calculated. However, constraints based on both the near-end and the far-end faults of large interconnection systems were taken into account. Noghabi et al. [4] introduced the concept of robust coordination for the DOCRs coordination problem and considered simultaneously a large number of coordination constraints corresponding to a set of network topologies, and an efficient genetic algorithm (GA) method combined with linear programming (LP) is proposed to solve the optimization problem. Noghabi et al. [5] applied the interval analysis technique to drastically reduce the number of coordination constraints when solving the DOCRs coordination problem of a large interconnection system. Abyaneh et al. [6] adopted the theory of optimization technique [7] and considered the relays whose characteristics are linearly and nonlinearly proportional to TDS when solving the DOCRs optimal setting problem. Bedekar and Bhide [8] treated the DOCRs coordination optimal problem as a nonlinear programming problem. They first applied GA to find an initial guess of the solution and then used nonlinear programming technique to determine the globally optimal solution.

Particle swarm optimization (PSO) theory was introduced by Eberhart and Kennedy in 1995 as a means to handle nonlinear optimization problems [9], which has now been expanded to include a wide range of applications related to optimization. Del Valle et al. [10] presented an extensive discussion on the basic concepts, variants, and applications of PSO in power systems. The PSO technique can be applied to power system problems such as reactive power and voltage control, economic dispatch, power system reliability and security, generation expansion problem, state estimation, load flow and optimal power flow, short-term load forecasting, and capacitor placement. Wu [11] proposed a hybrid real-coded genetic algorithm with a PSO algorithm and a hybrid artificial immune algorithm with a PSO algorithm to solve global optimization problems with 13 constraints. Kao et al. [12] proposed a new hybrid algorithm based on two main swarm intelligence approaches, the ant colony optimization (ACO) and the PSO to solve capacitated vehicle-routing combinatorial optimization problems. Zhang et al. [13] proposed an improved PSO algorithm to solve a bilevel multiobjective programming problem (BLMPP) in the upper level and the lower level interactively and repeatedly until the accurate Pareto optimal solutions of the original problem were found.

There are other literatures that applied the modified PSO approach for the DOCRs optimal coordination problem. Mansour et al. [14] proposed a repair algorithm which enabled the PSO algorithm to solve a constrained optimization coordination problem that has been solved as an LP problem. Zeineldin et al. [15] proposed a modified PSO algorithm which treated the DOCRs coordination problem as a mixed integer nonlinear programming problem and determined both the optimal discrete PS and continuous TDS. This proposal is far more superior to the original PSO algorithm and the general algebraic modeling system solvers in finding a near-optimal solution for the coordination problem.

This study is an attempt to supplement the findings of these earlier studies. It is similar to the previous studies discussed above, in that the focus is on the protection coordination of DOCRs using the PSO algorithm. However, this study differs from the previous works in its approach to assess nonlinear programming for the TDS and PS for DOCRs. Little research has been done on the simultaneous consideration of the TDS and PS for the coordination optimization of DOCRs. In addition to near-end faults, this study incorporates far-end faults into the objective function and takes into account a large number of coordination constraints in the optimal coordination problem. Due to the changeability of system topology, various network topologies were included in this study. As a result, the DOCRs coordination problem is a complex optimization problem with many nonlinear constraints, and a hybrid PSO method is applied to determine the optimal relay settings. This study shows that the proposed hybrid PSO method not only is efficient but also improves the convergence of conventional PSO.

2. Formulation of the DOCRs Coordination Issue

The principal aim of the coordination problem of DOCRs is to determine the TDS and PS of each relay. Then the optimal operating times of the primary relays can be minimized, for the protection coordination pairs of primary/backup relays coordination constraints to be satisfied. Therefore, the optimization objective function can be described as follows:

where and are the number of primary relays responding to near-end and far-end faults, respectively. The variables and indicate the operating time of primary relays for near-end and far-end faults.

2.1. Coordination Criteria

The coordination constraints between the primary and the backup relays are as follows:

where and reveal the operation time of the backup relay for the near-end and far-end faults, respectively. CTI is the minimum coordination time interval between backup and primary relay; the aim of the time interval is to ensure that circuit breakers clear the fault as directed. There are several factors influencing the operating time of relays, including CT error, the dc offset component of fault current, and relay overtravel. Therefore, typical CTI ranges from 0.2 to 0.5 s. In this study, a CTI of 0.2 s was selected.

2.2. Relay Characteristics

The nonlinear relay characteristics function based on standard IEEE C37.112-1996 can be stated as follows:

The constants 28.2, 0.1217, and 2 in (3) define the shape of the extremely inverse trip characteristics.

2.3. Bounds on the TDS and PS of Relays

The time dial setting is the adjustable delay of the th relay. In this study, the values range from 0.1000 to 1.1000:

is the pickup current setting of the th relay. As usual the value of can be determined by

In (5), the “2” of 2 times maximum value of load current represents safety factor, and the “2” of times minimum value of fault current represents dependability. In this study, the values range from 10 to 1000, for each relay. The PS is equal to divided by the CT ratio. The current transformer (CT) ratio for each relay is 500 : 1.

Consider,

is the short circuit current passing through the th relay.

2.4. Variable Network Topology Constraints

When line(s) outage occur(s), loading change or equipment is maintained; modifying network topology can improve power quality, ensuring that power supply is not affected or the duration of power failure is shortened. Once the network topology changes, the original TDS and PS values of DOCRs’ settings in the system are no longer suitable for the protection coordination under the new network topology. Among the literature, only [4, 5] deal with the impact of changes in the network topology on protection coordination. Adopting the original parameter settings at this point leads to miscoordination of DOCRs. Therefore, it is necessary to investigate new sets of coordination constraints corresponding to various network topologies.

In consideration of changes in network topology, (2) are revised as

where is the set of all topologies, when a single line outage occurs in the main topology.

3. Hybrid Nelder-Mead Method and Particle Swarm Optimization

The advantage of the PSO method [9] is that it belongs to the class of global search procedures; however, numerous particles are required, and the convergence can be very slow. To compensate for problems such as these, this study adopts PSO as the basic structure and uses the Nelder-Mead (NM) simplex search method [16] to form a hybrid Nelder-Mead simplex search method and particle swarm optimization. This method avoids falling easily into the local best solution with the added feature of the NM search method, which increases the rate of movement in the correct direction. This hybrid optimization method can lead to relatively rapid convergence to find a feasible and optimal solution. The following case study makes it is even clearer that the proposed NM-PSO method is superior to conventional PSO methods. This is an important contribution of this study. A conventional PSO method is incapable of dealing with constrained optimization problems. Therefore, the proposed NM-PSO method must be combined with a gradient-based repair method [17, 18] to overcome NLP problems with constraints.

Next, we introduce the algorithm procedure of the proposed NM-PSO. Assuming that the question to be solved is in dimensions, we first produce particles (N > n + 1, according to the experimental results of the case study) to form a swarm. For every particle that violates the constraints, we use the gradient repair method to direct infeasible solutions toward feasible regions, and in most cases, the repair method is successful in doing this. Next we arrange the calculation results of the objective function in the order of good to bad and divide the particles into three groups, that is, n particles, the (n + 1)th particle, and particles. We calculate the top particles and the (n + 1)th particle using the NM simplex method. The (n + 1)th particle is quickly modified to move in the correct direction, which is the key to the proposed algorithm. Through the calculation of a simple NM algorithm, the probability of finding the preferable optimal solution is increased. Subsequently, we employ the PSO method to adjust all of the particles, which (of course) include the best particles using the NM simplex method. This procedure for adjusting the particles involves the selection of the global best particle, selection of the neighborhood best particle, and finally the velocity updates. Thus, the global best particle of the population is determined. The entire NM-PSO optimal process is repeated until the termination condition is fulfilled. The details of the theory of the proposed NM-PSO algorithm are shown in [18, 19].

4. Simulation Results

An IEEE 8-bus test system was used to test and demonstrate the proposed method for solving a new problem formulated for the optimal protection coordination of relays. The 8-bus system comprises 7 lines, 2 transformers, and 14 DOCRs, as shown in Figure 1. The system parameters are stated in [4]. At bus 4, there is a link to another network modeled by a short circuit capacity of 400 MVA. However, the network topology is usually assumed to be fixed. In practice, the system may be operated in different topologies due to transmission lines outage. In order to take all the various network topologies into account, a large number of coordination constraints must be met. This study considers a variable network topology under steady-state rather than under transient-state as discussed in [20]. Additional constraints, such as the miscoordination caused by large transient currents in the backup relays of protection relay pairs resulting from the tripping of nearby relays, are not considered in this study.

Figure 1: One-line diagram for an IEEE 8-bus test system.

It is assumed that all of the DOCRs have IEEE standard inverse-time characteristics as mentioned above in (3). When the values of TDS and PS of DOCRs need to be solved simultaneously, the relay coordination problem can be formulated as a nonlinear programming problem. 20 particles are used to solve an n-dimensional problem in this study. Therefore, the population size in the NM-PSO method is 20 × n + 1, and the population size in the PSO method is 20 × n, where is the number of the PS and TDS for the 14 DOCRs.

A Matlab 7 program is developed to implement the NM-PSO algorithm and a conventional PSO algorithm and is executed on a PC with an Intel Core i5 3.1 GHz CPU and 4 GB RAM.

4.1. Fixed Network Topology

In this study, the minimization of the objective function and coordination constraints are based on the consideration of simultaneous near-end fault and far-end fault occurrence. In this subsection, we consider the fixed network topology to solve the coordination optimization problem using a conventional PSO and the proposed NM-PSO.

Table 1 demonstrates the primary/backup relay pairs and corresponding near-end and far-end fault currents passing through them for the test system. There are 34 inequality constraints corresponding to each relay pair.

Table 1: Primary/backup relay pairs and the fault currents in a fixed network topology.

P/B relay pairs
Near-end fault current (A)
Far-end fault current (A)

Primary relay no.
Backup relay no.
Primary relay
Backup relay
Primary relay
Backup relay

1
6
3230
3230
995
995

8
9
6080
1160
2990
553

8
7
6080
1880
2990
78*

2
1
5910
993
3550
393

9
10
2480
2480
1160
1160

2
7
5910
1880
3550
746

3
2
3550
3550
2240
2240

10
11
3880
2340
2480
1140

6
5
6100
1200
3230
626

6
14
6100
1870
3230
78#

13
8
2980
2980
986
986

14
9
5190
1160
1870
151#

7
5
5210
1200
1890
181#

14
1
5190
993
1870
986*

7
13
5210
985
1890
994*

4
3
3780
2240
2400
1050

11
12
3700
3700
2340
2340

5
4
2400
2400
1200
1200

12
13
5890
985
3700
433

12
14
5890
1870
3700
821

through DOCRs fault current flow reverse direction. #Passing through DOCRs fault current fall below their pickup current.

To find the optimal value of the object function, the program is run 10 times independently for each algorithm with 300 iterations in each run, and the best results of each run are recorded. Figure 2 shows the convergence characteristics in finding the best values. The proposed NM-PSO method converges to the optimal object function value in 5.5514 s in approximately 52 iterations, whereas a conventional PSO method converges to the optimal object function value in 6.1328 s. Due to the added feature of the proposed NM search method which increases the rate of movement in the correct direction, a globally optimal solution is more likely reached than a locally optimal solution. The result of an example case of 20 particles shows that the output of the proposed NM-PSO method converges rapidly to a feasible and optimal solution.

Figure 2: Convergence characteristics of a conventional PSO and the proposed NM-PSO in a fixed network topology.

The optimal values of the PS and TDS for both the proposed NM-PSO method and a conventional PSO method, considering fixed network topology are presented in Table 2. The operating times of primary/backup relay pairs for near-end and far-end faults are shown in Table 3. The constraint values are larger or equal to 0.2 in the column of Table 3. This means that all the coordination constraints have satisfied the coordination criteria.

Table 2: Results of a conventional PSO and the proposed NM-PSO in a fixed network topology.

Relay no.
PSO
NM-PSO

PS
TDS
PS
TDS

1
0.4644
0.2171
0.4911
0.1854

2
1.0728
0.5065
1.1621
0.4096

3
0.5681
0.6440
0.7506
0.3810

4
0.4553
0.7807
0.6156
0.5056

5
0.4861
0.2293
0.6632
0.1491

6
1.1828
0.2348
0.4056
1.0842

7
0.5468
0.5244
0.7574
0.2783

8
0.5518
0.7422
0.7954
0.3902

9
0.6187
0.1462
0.4075
0.2891

10
0.3648
1.0287
1.0075
0.2176

11
0.4392
1.0460
0.7999
0.3419

12
0.7757
0.9921
1.1674
0.4226

13
0.4754
0.2358
0.6585
0.1000

14
0.5058
0.6784
0.594
0.4299

Obj-Fun
6.1328
5.5514

Table 3: Operation times of primary/backup relay pairs in a fixed network topology (with near-end faults and far-end faults) using the proposed NM-PSO method.

Near-end fault
Far-end fault

Backup relay
Primary relay
Constraint

value (sec)
Backup relay
Primary relay
Constraint

value (sec)

No.
Operating time (sec)
No.
Operating time (sec)

No.
Operating time (sec)
No.
Operating time (sec)

6
0.2583
1
0.0583
0.2000
6
3.6456
1
0.3792
3.2664

9
0.3337
8
0.1335
0.2002
9
1.8970
8
0.2701
1.6270

7
0.3799
8
0.1335
0.2464

1
0.3800
2
0.1799
0.2001
1
3.3115
2
0.3954
2.9161

10
0.2830
9
0.0830
0.2000
10
0.8607
9
0.3337
0.5270

7
0.3799
2
0.1799
0.2000
7
2.3585
2
0.3954
1.9631

2
0.3954
3
0.1954
0.2000
2
0.9306
3
0.3752
0.5554

11
0.3895
10
0.1895
0.2000
11
1.2643
10
0.2830
0.9813

5
0.3046
6
0.0914
0.2132
5
1.1760
6
0.2583
0.9177

14
0.4390
6
0.0914
0.3476

8
0.2713
13
0.0713
0.2000
8
1.8682
13
0.4391
1.4291

9
0.3337
14
0.1281
0.2056

5
0.3046
7
0.1045
0.2001

1
0.3807
14
0.1281
0.2526

13
0.4391
7
0.1045
0.3346

3
0.3752
4
0.1752
0.2000
3
1.5123
4
0.2949
1.2174

12
0.4316
11
0.2316
0.2000
12
0.9111
11
0.3895
0.5217

4
0.2949
5
0.0949
0.2000
4
0.9170
5
0.3046
0.6124

13
0.4391
12
0.2389
0.2002
13
2.8975
12
0.4316
2.4659

14
0.4390
12
0.2389
0.2000
14
2.0881
12
0.4316
1.6565

×: both the primary protection and the backup protection are unavailable because the current flowing through the DOCRs is either too small or in the wrong direction.

4.2. Variable Network Topologies

When modifications are required in the network topology due to changes in load demand or emergency conditions, continued use of the TDS and PS values of DOCRs as system settings planned according to fixed network topology will lead to miscoordination. For example, in Figure 2, when Line 65 was removed, the network topology changed in response. The new relationship of primary/backup relay pairs and new fault current at this point is shown in Table 4. Under this condition, Table 5 shows the operating time of primary/backup relay pairs and constraint values between them. In this table, there are some constraint values that do not satisfy the coordination criteria.

Table 4: Primary/backup relay pairs and the fault currents after the removal of Line 65.

P/B relay pairs
Near-end fault current (A)
Far-end fault current (A)

Primary relay no.
Backup relay no.
Primary relay
Backup relay
Primary relay
Backup relay

1
6
2990
2990
940
940

8
9
6130
1320
3130
1080

8
7
6130
1780
3130
433

2
1
5760
939
4320
705

9
10
1430
1430
1320
1320

2
7
5760
1780
4320
1340

3
2
4320
4320
3520
3520

10
11
1540
0
1430
0

6
14
5480
2440
2990
433

13
8
3130
3130
1290
1290

14
9
5290
1320
2450
1130

14
1
5290
939
2450
1290*

7
13
4320
1290
1780
939*

4
3
5060
3520
4000
2790

through DOCRs fault current flow reverse direction.

Table 5: Operation times of primary/backup relay pairs after the removal of Line 65 (near-end faults).

Backup relay
Primary relay
Constraint value (sec)

No.
Operating time (sec)
No.
Operating time (sec)

6
0.2982
1
0.0636
0.2346

9
0.2576
8
0.1328
0.1248

7
0.4212
8
0.1328
0.2884

1
0.4254
2
0.1866
0.2388

10
0.6050
9
0.2204
0.3847

7
0.4212
2
0.1866
0.2346

2
0.2853
3
0.1572
0.1281

14
0.2903
6
0.1066
0.1837

8
0.2542
13
0.0673
0.1869

9
0.2576
14
0.1264
0.1312

1
0.4254
14
0.1264
0.2990

13
0.2625
7
0.1233
0.1392

3
0.1974
4
0.1397
0.0577

Using an IEEE 8-bus test system, consideration of single line outage leads to seven different network topologies. The near-end faults and far-end faults in these seven circumstances result in a total of 136 primary/backup relay pairs that must satisfy coordination constraints. To find the optimal values of the PS and TDS for both the proposed NM-PSO method and a conventional PSO method, the program is run 10 times independently for each algorithm with 300 iterations in each run, and the best result of each run is recorded in Table 6. Figure 3 shows the convergence characteristics in finding the best values. As stated previously, the proposed NM-PSO method converges to an optimal solution faster than a conventional PSO method because the proposed NM-PSO method has a higher rate of movement in the correct direction and converges to a globally optimal solution more likely than a locally optimal solution. Although faster convergence and better optimal values can be obtained by increasing the number of particles, the complexity of the optimization process will also increase. The statistical results for 10 independent runs are shown in Table 7. Together Tables 6 and 7 demonstrate the superiority of NM-PSO. The operating times of primary/backup relay pairs with constraint values between them are examined, and the results are listed in Table 8. The fact that the results conform to requirements demonstrates the robustness of the proposed NM-PSO algorithm in dealing with large numbers of coordination constraints.

Table 6: Results of a conventional PSO and the proposed NM-PSO in variable network topologies.

Relay no.
PSO
NM-PSO

PS
TDS
PS
TDS

1
0.7999
0.4297
0.5527
0.8140

2
0.8892
1.0540
1.1418
0.7155

3
0.7498
0.7342
0.7524
0.7288

4
1.1999
0.2423
1.1897
0.2440

5
0.7921
0.2679
0.9099
0.2056

6
0.6497
1.0998
0.7380
0.9772

7
0.7674
0.6715
0.6342
0.8892

8
0.8868
0.7033
0.7692
0.8726

9
0.4900
0.6088
0.7801
0.2616

10
1.0138
0.3585
0.9784
0.3580

11
0.6267
1.0189
0.5887
1.0794

12
1.1804
0.7422
1.0699
0.8652

13
0.5661
0.8237
0.6198
0.7069

14
0.7781
0.6595
0.6128
0.9878

Obj-Fun
65.0723
64.6398

Table 7: 10 independent runs of a conventional PSO and the proposed NM-PSO in variable network topologies.

10 independent runs
PSO
NM-PSO

1
65.0723
64.6398

2
66.6168
65.6285

3
65.2207
65.6045

4
67.0376
65.6308

5
66.0238
65.5951

6
67.0316
64.7014

7
66.9528
65.5822

8
66.7907
64.8591

9
66.7058
65.3773

10
66.1551
65.0092

Mean
66.3607
65.2628

Standard deviations
0.72601
0.41393

Table 8: Operation times of primary/backup relay pairs after the removal of Line 65 (near-end faults) using the proposed NM-PSO method.

Backup relay
Primary relay
Constraint value (sec)

No.
Operating time (sec)
No.
Operating time (sec)

6
0.5452
1
0.2968
0.2484

9
0.7377
8
0.2034
0.5343

7
0.9302
8
0.2034
0.7267

1
2.2755
2
0.2873
1.9883

10
1.3815
9
0.6249
0.7566

7
0.9302
2
0.2873
0.6429

2
0.4457
3
0.2457
0.2000

14
0.5666
6
0.2445
0.3221

8
0.4834
13
0.2834
0.2000

9
0.7377
14
0.2140
0.5237

1
2.2755
14
0.2140
2.0616

13
1.3070
7
0.2441
1.0630

3
0.3261
4
0.1261
0.2000

Figure 3: Convergence characteristics of a conventional PSO and the proposed NM-PSO in variable network topologies.

5. Conclusions

In this paper, the coordination optimization problem is represented by a nonlinear relay characteristic function and a range of nonlinear coordination constraints. A detailed formulation of the optimal DOCRs coordination problem in variable network topologies is presented. This study proposes an NM-PSO method to find an optimal solution for the complex optimization problem such that a large number of coordination constraints corresponding to various network topologies are satisfied simultaneously. The proposed method has the advantages of NM and PSO methods but none of their individual drawbacks and finds the optimal solution more accurately and efficiently. It has been shown that the proposed NM-PSO method outperforms a conventional PSO method.

Abbreviations

: | The number of primary relays responding to near-end faults
: | The number of primary relays responding to far-end faults
: | The operating time of primary relays for near-end faults
: | The operating time of primary relays for far-end faults
: | The operation time of the backup relay for the near-end faults
: | The operation time of the backup relay for the far-end faults
: | The coordination time interval
: | The time dial setting of the th relay
: | The pickup current setting of the th relay
: | The plug setting
ratio: | The current transformer ratio
: | The short circuit current passing through the th relay.

References

P. M. Anderson, Power System Protection, McGraw-Hill, New York, NY, USA, 1999.

A. J. Urdaneta, R. Nadira, and L. G. Perez Jimenez, “Optimal coordination of directional overcurrent relays in interconnected power systems,” IEEE Transactions on Power Delivery, vol. 3, pp. 903–911, 1988.

D. Birla, R. P. Maheshwari, and H. O. Gupta, “A new nonlinear directional overcurrent relay coordination technique, and banes and boons of near-end faults based approach,” IEEE Transactions on Power Delivery, vol. 21, no. 3, pp. 1176–1182, 2006.

A. S. Noghabi, J. Sadeh, and H. R. Mashhadi, “Considering different network topologies in optimal overcurrent relay coordination using a hybrid GA,” IEEE Transactions on Power Delivery, vol. 24, no. 4, pp. 1857–1863, 2009.

A. S. Noghabi, H. R. Mashhadi, and J. Sadeh, “Optimal coordination of directional overcurrent relays considering different network topologies using interval linear programming,” IEEE Transactions on Power Delivery, vol. 25, no. 3, pp. 1348–1354, 2010.

H. A. Abyaneh, M. Al-Dabbagh, H. K. Karegar, S. H. H. Sadeghi, and R. A. J. Khan, “A new optimal approach for coordination of overcurrent relays in interconnected power systems,” IEEE Transactions on Power Delivery, vol. 18, no. 2, pp. 430–435, 2003.

S. S. Rao, Optimization: Theory and Applications, Halsted Press, New York, NY, USA, 1984.

P. P. Bedekar and S. R. Bhide, “Optimum coordination of directional overcurrent relays using the hybrid GA-NLP approach,” IEEE Transactions on Power Delivery, vol. 26, no. 1, pp. 109–119, 2011.

R. Eberhart and J. Kennedy, “A new optimizer using particle swarm theory,” in Proceedings of the 6th International Symposium on Micro Machine and Human Science, pp. 39–43, Nagoya, Japan, October 1995.

Y. del Valle, G. K. Venayagamoorthy, S. Mohagheghi, J. C. Hernandez, and R. G. Harley, “Particle swarm optimization: basic concepts, variants and applications in power systems,” IEEE Transactions on Evolutionary Computation, vol. 12, no. 2, pp. 171–195, 2008.

J. Y. Wu, “Solving constrained global optimization problems by using hybrid evolutionary computing and artificial life approaches,” Mathematical Problems in Engineering, vol. 2012, Article ID 841410, 36 pages, 2012.

Y. Kao, M. H. Chen, and Y. T. Huang, “A Hybrid algorithm based on ACO and PSO for capacitated vehicle routing problems,” Mathematical Problems in Engineering, vol. 2012, Article ID 726564, 17 pages, 2012.

T. Zhang, T. Hu, Y. Zheng, and X. Guo, “An improved particle swarm optimization for solving bilevel multiobjective programming problem,” Journal of Applied Mathematics, vol. 2012, Article ID 626717, 13 pages, 2012.

M. M. Mansour, S. F. Mekhamer, and N. E. S. El-Kharbawe, “A modified particle swarm optimizer for the coordination of directional overcurrent relays,” IEEE Transactions on Power Delivery, vol. 22, no. 3, pp. 1400–1410, 2007.

H. H. Zeineldin, E. F. El-Saadany, and M. M. A. Salama, “Optimal coordination of overcurrent relays using a modified particle swarm optimization,” Electric Power Systems Research, vol. 76, no. 11, pp. 988–995, 2006.

J. A. Nelder and R. Mead, “A simplex method for function minimization,” Computer Journal, vol. 7, pp. 308–313, 1965.

P. Chootinan and A. Chen, “Constraint handling in genetic algorithms using a gradient-based repair method,” Computers and Operations Research, vol. 33, no. 8, pp. 2263–2281, 2006.

A. Liu and M. T. Yang, “A new hybrid Nelder-Mead particle swarm optimization for coordination optimization of directional overcurrent relays,” Mathematical Problems in Engineering, vol. 2012, Article ID 456047, 18 pages, 2012.

A. Liu, E. Zahara, and M. -T. Yang, “A modified NM-PSO method for parameter estimation problems of models,” Journal of Applied Mathematics, vol. 2012, Article ID 530139, 12 pages, 2012.

A. J. Urdaneta, L. G. Pérez, and H. Restrepo, “Optimal coordination of directional overcurrent relays considering dynamic changes in the network topology,” IEEE Transactions on Power Delivery, vol. 12, no. 4, pp. 1458–1464, 1997.