Computational Intelligence and Neuroscience
Volume 2015 (2015), Article ID 620360, 12 pages
http://dx.doi.org/10.1155/2015/620360

Research Article

Fuzzy Inference System Approach for Locating Series, Shunt, and Simultaneous Series-Shunt Faults in Double Circuit Transmission Lines

Aleena Swetapadma and Anamika Yadav

Department of Electrical Engineering, National Institute of Technology, Raipur 492010, India

Received 20 June 2015; Accepted 4 August 2015

Academic Editor: Elio Masciari

Copyright © 2015 Aleena Swetapadma and Anamika Yadav. This is an open access article distributed under the Creative Commons Attribution License, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.

Abstract.

Many schemes are reported for shunt fault location estimation, but fault location estimation of series or open conductor faults has not been dealt with so far. The existing numerical relays only detect the open conductor (series) fault and give the indication of the faulty phase(s), but they are unable to locate the series fault. The repair crew needs to patrol the complete line to find the location of series fault. In this paper fuzzy based fault detection/classification and location schemes in time domain are proposed for both series faults, shunt faults, and simultaneous series and shunt faults. The fault simulation studies and fault location algorithm have been developed using Matlab/Simulink. Synchronized phasors of voltage and current signals of both the ends of the line have been used as input to the proposed fuzzy based fault location scheme. Percentage of error in location of series fault is within 1% and shunt fault is 5% for all the tested fault cases. Validation of percentage of error in location estimation is done using Chi square test with both 1% and 5% level of significance.

1. Introduction

In general, the transmission line faults are categorized into series faults and shunt faults. Unlike the shunt faults, which are characterized by substantial increase in current flow, the low magnitude of current following a series fault makes it difficult to be located by conventional approaches based on calculation of impedance and using fundamental component of current and voltage. Series fault is defined as a fault for which the impedances of the three phases are not equal, which is usually caused by the interruption of one or two phases. Series faults in EHV lines may occur due to broken conductor or a circuit breaker malfunction in one or more phases. The broken conductor leads to unbalance and flow of asymmetrical current arising because of the open conductor coming in series with the effected lines. As per field studies, a series fault may occur due to one of the following reasons:

(i)Broken conductor(s) due to storm, falling of trees.(ii)When poles of the circuit breakers fails to open.(iii)Opening of jumpers at tension tower (angle locations) due to accident and storms.(iv)Mechanical failure of jumpers.(v)Burning of jumper cones due to local heating at joints because of loose contacts/high contact resistance during prolonged operation.

Although series fault is not dangerous to the system, the operation of the load connected is hampered. The numerical distance relays, which are widely used for protection of transmission lines, only give an alarm that particular phase(s) is/are open, but no trip command is issued to the circuit breaker. Further the distance relays are unable to locate the open conductor (series) fault. Faults in transmission lines affect the power flow and reduce the reliability of transmission system. Fault location estimation is an important task in transmission system for carrying out maintenance work to improve power flow reliability and reduce repairing expenses.

Some research has been done to detect the open conductor/series fault. Open phase conductor detector system is described in [1] consisting of transmitters and receiver where transmitter(s) detects the open phase conductor by monitoring the phase conductor voltage using redundant inputs. Carrier communication is used for open conductor detection in [2]. Open conductor fault calculation in four parallel transmission lines using twelve-sequence component methods is discussed in [3]. ANN based techniques are used for enhancement of distance relay performance against open conductor in HV transmission lines in [4]. However these schemes [1–4] are unable to find the location of series/open conductor fault.

There are many schemes reported for shunt fault location estimation. Phasor measurements units (PMU) are used by many researchers nowadays for finding the location of shunt faults in transmission lines [5–17]. Phasor measurement fault location algorithms can be categorized as synchronized [5–9] and unsynchronized [10–14]. Synchronized measurement can be achieved using global positioning system (GPS) and high speed broad band communication system. GPS has a remote telemetry unit which provides the synchronized data through transmission control center [5]. Fault analysis functions, such as fault detection, classification, and location, are implemented for a transmission line using synchronized samples from two ends of a line in [6]. Traveling-wave based fault location techniques for transmission grids using synchronized voltage measurements are proposed in [7]. Synchronized current measurement from both ends and voltage measurement from one end are used for fault location estimation in [8]. In [9] only half cycle of the postfault synchronized voltage and current samples from both ends of the line are taken to estimate location of fault. Fault locations are also estimated using two-end unsynchronized phasor measurement in series-compensated lines [10–12]. Shunt fault location estimation algorithms can be categorized in terms of using one-end data [13–17] and two-end data [6, 7, 9–12]. Phase coordination approach using one-end data for fault location estimation is proposed in [13, 15, 16]. Differential equation approach using one-end data is proposed in [14, 17]. Fault distance is also estimated using modal theory by taking two-terminal data [11]. It is noteworthy to mention here that these schemes [5–17] are not applicable for series/open conductor fault location estimation task.

Fault location algorithms for shunt faults are reported by researchers using different soft computing techniques like artificial neural network (ANN) [18–21], fuzzy [22] and adaptive neurofuzzy inference system (ANFIS) [23], SVM [24], and so forth. Among all the soft computing techniques, fuzzy inference system is used mostly in engineering applications, for example, fault classification [25], due to its easy implementation and less computation work to get accurate results unlike other training based soft computing methods. Moreover there is a chance that simultaneous series and shunt faults may occur in the transmission line as discussed in [26, 27] which can lead to incorrect operation of relay. Digital distance relaying scheme which takes care of a simultaneous open conductor and ground fault occurring coincidently on the same phase at the same point on a series-compensated double circuit line is proposed in [28]. But the scheme treats the simultaneous open conductor and ground fault as single line to ground fault.

Hence, it can be concluded that, hitherto, none of the earlier reported papers [1–28] can locate both series and shunt faults and simultaneous series-shunt faults. In this paper, a method is proposed using synchronized phasors and fuzzy logic to classify the fault and estimate fault location of series faults, shunt faults, and simultaneous series and shunt faults. The proposed fuzzy based method works in three stages. In the first stage, the current and voltage signals obtained from both ends of the line are preprocessed to calculate the fundamental components and zero-sequence component of current signals. Thereafter, two fuzzy modules for fault classification have been designed to discriminate the type of fault, that is, whether series fault or shunt fault or simultaneous series and shunt fault has occurred. Further, according to the type of fault, a particular fuzzy module for fault location of series or shunt or simultaneous series or shunt will be activated which finds the location of fault in kilometers from the relaying point.

2. Fuzzy Inference System (FIS) and Its Application

Fuzzy inference system is chosen to locate the faults in transmission lines in this work because it is easy to implement and it does not require training module to produce outputs. Due to less computation work than other soft computing techniques fuzzy system is chosen. Fuzzy inference system deals with fuzzy logic which starts with the concept of a fuzzy set. A fuzzy set is a set without a crisp, clearly defined boundary. It can contain elements with only a partial degree of membership. A fuzzy set can be defined by the following expression:

where represents the universal set, is an element of , is a fuzzy subset in , and is the membership function of fuzzy set .

FIS chosen to be used here is “Mamdani” type because it expects the output membership functions to be fuzzy sets. As fuzzy logic used here is to estimate the location of fault which is not a fixed value, so it is better to use Mamdani method than to use Sugeno method. Membership functions are designed with various membership functions like Gauss, triangular, trapezoidal, and sigmoid functions and so forth. In this work input and output are designed with triangular member function because it has lowest error in location. The triangular membership function is a function of a vector, , and depends on three scalar parameters, , , and , as given by (2) or (3). Consider the following:

or

Fuzzy sets and fuzzy operators are the subjects and verbs of fuzzy logic. If-then rule statements are used to formulate the conditional statements that comprise fuzzy logic. A single fuzzy if-then rule assumes the form as shown in

where and are linguistic values defined by fuzzy sets on the ranges and , respectively. From the inputs impedance values their membership values are obtained. This process is called “input fuzzification.” From the consequent of each rule (a fuzzy set) and the antecedent value obtained a fuzzy implication operator is applied to obtain a new fuzzy set. Implication method used here is “minimum” which truncates the consequent’s membership function and the product which scales it. Then it combines the outputs obtained for each rule into a single fuzzy set, using a fuzzy aggregation operator which is “maximum” in this case. The fuzzy set is then transformed into a single numerical value. Defuzzification method used here is the “centroid” method which returns the centre of the area under the fuzzy set. Center of gravity method is a grade weighted by the areas under the aggregated output functions. The centroid defuzzification method can be given as in

where for all .

By following all these steps described above fuzzy module is designed for fault classification and location estimation module. Detailed fuzzy design of the proposed fault location schemes for series faults, shunt faults, and simultaneous series and shunt faults will be described in next section.

3. Proposed Fuzzy Based Series, Shunt, and Simultaneous Series and Shunt Faults Classification and Location Estimation

Proposed method uses synchronized phasor measurements and fuzzy inference system to estimate the fault location. Steps followed in the proposed method are described in Figure 1 for the estimation of fault location and are described in following subsections.

Figure 1: Flow chart of proposed method.

3.1. Power System Network

The utility electrical power plant system selected for modelling is the existing 400 kV transmission line between Korba NTPC to Raipur PGCIL in Chhattisgarh state. Length of the transmission line is 220 km between Korba to Raipur as shown in Figure 2. Power transfer through the double circuit line is 341 MW. Synchronized phasors of currents and voltages are preprocessed using Discrete Fourier Transform (DFT) and sequence analyzer. Fundamental component of current and voltages is obtained using DFT. Zero-sequence currents are obtained using the sequence analyzer in order to determine whether ground is involved in the fault loop or not.

Figure 2: Existing 400 kV transmission line between Korba NTPC to Raipur PGCIL in Chhattisgarh.

3.2. Design of Fuzzy Module for Classification of Series Fault (FIS-CSR) and Shunt Fault (FIS-CSH)

For classification of type of faults, the fundamental components and zero-sequence components of currents of both ends are taken. Two different FIS modules are designed, one for classification of series fault (FIS-CSR) and the other for classification of shunt fault (FIS-CSH). In this present study Mamdani type FIS has been used because its outputs are in fuzzy sets.

3.2.1. Fuzzy Module for Classification of Series Fault (FIS-CSR)

A single FIS module has been designed for detecting the presence of fault in a particular phase. The same FIS has been used for the other two phases. Each phase FIS module takes its fundamental phase current as input and provides single output representing the presence of fault in that phase by trip high (TH) or trip low (TL) for no fault condition. The fundamental components of three phase currents of both circuits measured at both ends of the line are used as input for fault classification. Fundamental component of current is set to certain range which corresponds to fault or no fault in each phase. Three ranges of are selected using triangular member function, that is, low, medium, and high. The output trip logic also contains two ranges of triangular member function, that is, trip low (TL) (0) and trip high (TH) . The degree of membership functions for input phase fundamental current is shown in Figure 3(a) for series faults. FIS-CSR has six outputs corresponding to the three phases of the parallel lines (double circuit lines). The rules designed for faulty phase identification and fault classification are as follows:

(1)If fundamental phase current is low or medium then trip is TH.(2)If fundamental phase current is high then trip is TL.

Fuzzy inference system for fault classification of series fault (FIS-CSR) takes the fundamental current of each phase as input and produces the state of each phase (whether faulty or not) as output.

(a) Series fault

(b) Shunt fault, phase identification

(c) Shunt fault, ground identification

Figure 3: Degree of member function for (a) series fault, (b) shunt fault phase identification, and (c) shunt fault ground identification.

3.2.2. Fuzzy Module for Classification of Shunt Fault (FIS-CSH)

The shunt faults are classified into phase to ground (LG), double phase to ground (LLG), phase to phase (LL), and three-phase (LLL) faults. As discussed in Section 2, for faulty phase identification, the fundamental components of three phase currents are taken as input to FIS-CSH for classification of phases. Further, for ground identification, separate FIS module has been designed which takes the zero-sequence current signals of the two circuits 1 and 2 as input. Each input’s signals are distributed in three ranges with triangular member function, that is, low, medium, and high. There are six outputs for faulty phase identification corresponding to the three phases of circuit 1: A1, B1, and C1 and A2, B2, and C2 of circuit 2 which becomes high in case of fault and otherwise remains low (0). The degree of membership functions for input current is shown in Figure 3(b) for shunt fault phase identification and in Figure 3(c) for ground identification. The rules designed for faulty phase identification are as follows:

(1)If fundamental phase current is low or medium then trip is TL.(2)If fundamental phase current is high then trip is TH.

Further the rules used for ground identification are as follows:

(1)If zero-sequence current is low or medium then trip is TL.(2)If zero-sequence current is high then trip is TH.

3.3. Design of Fuzzy Module for Fault Location

Once the fault is detected and its type is identified, then the next task of protective relaying scheme is to estimate the fault location from the relaying point. In this study, two separate FIS modules have been designed for series fault (FIS-LSR) and shunt fault (FIS-LSH). Based on type of fault that has occurred in the monitored transmission line, that is, whether series fault or shunt fault or simultaneous series-shunt fault, the corresponding fuzzy module for fault location will be activated which estimates the location of fault.

3.3.1. Fuzzy Module for Series Fault Location (FIS-LSR)

During series fault, the fundamental component of current signals is the same in all the faulted phases for fault at a particular location (either single phase open fault or multiple phase open faults). Hence only one faulty phase fundamental current is taken as input for design of fuzzy location module for series faults. The block diagram of fuzzy module designed for fault location estimation of series faults (FIS-LSR) is shown in Figure 4(a).

(a)

(b)

Figure 4: Fuzzy modules: (a) series FIS-LSR and (b) shunt FIS-LSH for fault location.

Fundamental components of current values are divided into ranges like using triangular member functions. Output represents the fault location in kilometers which is divided into 111 ranges using triangular member function like . Total number of rules designed for series fault location is 112 as given below:

(1)If input is then location is .(2)If input is then location is . ⋮ (111)If input is then location is .(112)If input is then location is .

3.3.2. Fuzzy Module for Shunt Fault Location (FIS-LSH)

For designing fault location module for shunt faults using fuzzy inference system, the phase impedance is calculated for faulty phase(s) from

where is fundamental component of voltage and is fundamental component of current. is taken as input to the fuzzy module for fault location estimation of shunt faults. Different fuzzy modules for different types of fault (LG, LLG, LL, and LLL) for fault location estimation are designed. Based on type of fault which has occurred in the system identified by fault classification module, the corresponding FIS-LSH will be activated and fault location will be estimated. Figure 4(b) shows the fuzzy based fault location modules (FIS-LSH) of different types of shunt fault; impedance () of faulty phase is taken as input to fuzzy module and fault location is estimated. In Figure 4(b), it is clear that for LG faults there will be only one input as only one phase is faulty. Fundamental components of impedance () are divided into a number of ranges like using triangular member functions. Output fault location is also divided into ranges using triangular member function like . Total number of rules made for LG shunt fault location is 56. The rules are given below:

(1)If input is then location is .(2)If input is then location is . ⋮(55)If input is then location is .(56)If input is then location is .

For LLG and LL faults, there are two inputs to the fuzzy module as shown in Figure 4(b). Fundamental components of impedance values for faulty phase 1 () and phase 2 () are divided into ranges like and using triangular member functions. Output fault location is also divided into ranges using triangular member function like . The rules for LLG faults are given hereunder. Similarly LLL fault location module is designed using three inputs for location estimation as shown in Figure 4(b):

(1)If input 1 is and input 2 is then location is .(2)If input 1 is and input 2 is then location is .(3)If input 1 is and input 2 is then location is . ⋮(55)If input 1 is and input 2 is then location is .(56)If input 1 is and input 2 is then location is .

3.3.3. Simultaneous Series and Shunt Fault Location

If both series and shunt fault classification FIS modules (FIS-CSH and FIS-CSR) detect the presence of fault, then simultaneous series and shunt fault has occurred. In case of simultaneous series and shunt faults, location of series fault will be obtained using one-end measurement and that of shunt fault will be obtained using remote end measurement. For simultaneous series and shunt faults, FIS-LSR is activated for series fault end and FIS-LSH is activated for shunt fault end, which determines the location of respective fault.

4. Results and Discussion

Performance of the proposed method is evaluated by varying different fault parameters like fault type, fault location, and fault inception angle. Fault resistance in case of shunt faults is kept constant () in proposed method. The FIS module is designed to give output fault location as 500 km during no fault/normal operating condition and during faulty condition; it will give an estimated fault location as output. The percentage of error in fault location estimation is calculated using (7). The test results for different series faults, shunt faults, and simultaneous series and shunt faults are discussed in detail in this section:

4.1. Series Fault Classification and Location Estimation

The proposed scheme involves two stages; first is fault classification and then location estimation. In the first stage, both the FIS modules FIS-CSR and FIS-CSH are tested to detect the fault and classify the fault type, that is, whether the fault is series or shunt fault. For example, a series fault in A1 phase has occurred at 60 ms time and 64 km away from the relaying point; the test result of both the FIS is shown in Figure 5. Figure 5(a) shows the six outputs of FIS-CSR which become high after 80.5 ms for phase A1 only depicting that the fault is series fault in A1 phase of circuit 1 while Figure 5(b) shows that the outputs of FIS-CSH are all low (0) confirming that there is no shunt fault in the system. Once the fault type is classified as series fault, the corresponding FIS module for series fault location estimation is activated and the output of FIS-LSR during a series fault in phase A1 at 64 km at 60 ms time is shown in Figure 6. The estimated fault location is 63 km after 88 ms time as shown in Figure 6. Further the proposed scheme is also tested for different series faults with varying fault location and inception angle and some of the results of proposed fault location scheme are given in Table 1. The test result shows the high accuracy in determining the fault location with much less % of error.

Table 1: Test results of series faults location estimation.

Fault type
Fault inception angle (°)
Fault location (km)
Estimated location (km)
Error (%)

A1
0
6
7.000
−0.0045

B2
45
36
35.000
0.0045

C1
90
66
66.000
0.0000

A2B2
135
96
96.000
0.0000

B1C1
180
126
126.000
0.0000

C2A2
225
156
157.000
−0.0045

A1B1C1
270
186
189.000
−0.0136

(a)

(b)

Figure 5: Output of fuzzy based fault classification modules during A1 phase series fault at 64 km in 60 ms time. (a) FIS-CSR and (b) FIS-CSH.

Figure 6: Output of fuzzy based fault location module FIS-LSR during A1 phase series fault at 64 km at 60 ms time.

4.2. Shunt Fault Classification and Location Estimation

The proposed scheme can simultaneously detect the presence of fault and also classify the fault whether it is series or shunt fault as, during no fault or normal condition, all outputs of both the fuzzy modules FIS-CSR and FIS-CSH are low (zero), and in case of any type of fault the corresponding fuzzy classification module output changes its state from low to high after some time. This can be clearly seen from the test results shown in Figure 7 during A1B1G shunt fault in circuit 1 at 50 km at 60 ms time.

(a)

(b)

Figure 7: Output of fuzzy based fault classification modules during A1B1G1 shunt fault at 50 km in 60 ms time. (a) FIS-CSR and (b) FIS-CSH.

Figure 7(a) shows that all the outputs of FIS-CSR are low throughout the simulation time (0–160 ms) and Figure 7(b) shows the outputs of FIS-CSH fault module which become high for phases A1, B1, and G1 after 73.54 ms time verifying that it is A1B1G shunt fault in circuit 1. As the fault type classified is LLG type of shunt fault, LLG shunt fault locator estimates the fault location as 50.69 km as shown in Figure 8. Few more other types of shunt fault are tested and results are reported in Table 2.

Table 2: Test results of shunt faults location estimation.

Fault type
Fault inception angle (°)
Fault location (km)
Estimated location (km)
Error (%)

A1G
0
9
9.000
0.0000

B2G
45
29
27.000
0.0090

C1G
90
49
49.665
−0.0030

A2B2G
135
69
70.200
−0.0050

B1C1G
180
89
88.640
0.0010

C2A2G
225
109
109.200
−0.0009

A1B1
270
129
132.600
−0.0163

B2C2
315
149
148.200
0.0036

C1A1
0
169
171.200
−0.0100

A2B2C2
90
189
195.000
−0.0272

Figure 8: Output of fuzzy based fault location module FIS-LSH during A1B1G fault at 50 km at 60 ms time.

4.3. Simultaneous Series and Shunt Faults Location

The simultaneous fault may consist of two different types of fault: series and shunt at the one location or at different locations [27, 28]. For example, consider open circuit in one phase and simultaneously a single phase to ground fault occurring coincidentally on the same phase or different phase at the same location in the transmission line network. A simultaneous series and shunt fault is simulated by assuming that one end of the conductor has been broken and fallen to the ground, while the other end of the conductor is hanged on the tension tower without touching the ground. The proposed method is tested for this situation and Figures 9(a)–9(d) show the test results during A1G shunt fault at 80 km from sending end at 60 ms time and simultaneously the other end of A1 phase conductor is open, that is, A1 phase series fault at the same location from sending end but 140 km from remote end bus. The output of proposed FIS-CSR and FIS-LSR during series fault is shown in Figures 9(a) and 9(c) and Figures 9(b) and 9(d) show the outputs of FIS-CSH and FIS-LSH for shunt fault, respectively. From Figure 9 it can be seen that the proposed scheme correctly identifies the fault type and the faulty phase and its location. Proposed fuzzy based method is tested for some other simultaneous series and shunt faults and results are given in Table 3, which corroborate that the proposed scheme works equally well during simultaneous series and shunt faults situation also, as compared to existing schemes which fails.

Table 3: Test results of simultaneous series and shunt fault location estimation.

Fault inception angle (°)
Series fault type
Estimated series fault location (km)
Error (%)
Shunt fault type
Estimated shunt fault location (km)
Error (%)

0
A1 at 200 km from receiving end
196.000
1.818
A1G at 20 km from sending end
18.000
0.909

60
B1 at 180 km from receiving end
182.000
0.909
B1G at 40 km from sending end
36.000
1.818

120
C1 at 160 km from receiving end
161.000
0.454
C1G at 60 km from sending end
54.000
2.727

180
A2 at 140 km from receiving end
140.000
0.000
A2G at 80 km from sending end
76.000
1.818

240
B2 at 120 km from receiving end
119.000
0.454
B2G at 100 km from sending end
98.000
0.909

300
C2 at 100 km from receiving end
98.000
0.909
C2G at 120 km from sending end
118.000
0.909

0
C1 at 209 km from receiving end
216.000
−0.0318
A1G at 11 km from sending end
9.000
0.0090

45
B2 at 22 km from sending end
21.000
0.0045
C2G at 198 km from receiving end
199.000
−0.0045

90
A1 at 177 km from receiving end
182.000
−0.0227
B1G at 43 km from sending end
45.000
−0.0090

135
A2B2 at 63 km from sending end
63.000
0
C2G at 157 km from receiving end
165.000
−0.0363

180
A1 at 137 km from receiving end
140.000
−0.0136
B1C1G at 83 km from sending end
85.800
−0.0127

225
B2 at 103 km from sending end
105.000
−0.0090
C2A2G at 117 km from receiving end
117.000
0.0000

270
C1 at 97 km from receiving end
98.000
−0.0045
A1B1 at 123 km from sending end
124.800
−0.0081

315
A2 at 143 km from sending end
147.000
−0.0181
B2C2 at 77 km from receiving end
78.000
−0.0045

0
C1A1 at 57 km from receiving end
56.000
0.0045
B1G at 163 km from sending end
171.000
−0.0363

90
A2B2 at 183 km from sending end
182.000
0.0045
C2G at 37 km from receiving end
36.000
0.00454

180
A2B2C2 at 203 km from sending end
203.000
0
A2G at 17 km from receiving end
18.000
−0.0045

270
A1B1 at 213 km from sending end
215.000
−0.0090
B1G at 7 km from receiving end
9.000
−0.0090

(a)

(b)

(c)

(d)

Figure 9: Outputs of fuzzy modules during A1G1 shunt fault at 80 km from sending end at 60 ms time and A1 series fault at 140 km from receiving end. (a) FIS-CSR, (b) FIS-CSH, (c) FIS-LSR, and (d) FIS-LSH.

4.4. Validation of % of Error in Fault Location Using Chi Square () Test

A large number of fault case studies had been carried out to evaluate the performance of proposed method by varying different fault parameters like types of fault, fault location, and fault inception angle and % of error in location estimation is calculated. The % of error in series faults location estimation lies within 1%; on the other hand the error lies between 0–5% in case of shunt faults; thus it is necessary to validate it using some validation test, for example, Chi square () test. Fault location error of shunt faults is divided into two ranges 0 to ±2.0% and ±2.1 to ±5%. Figure 10 shows the percentage of fault cases in which the shunt fault location error is within 0 to ±2.0% and ±2.1 to ±5% ranges.

Figure 10: % of error distribution for different faults: LG fault, LLG fault, LL fault, and LLL fault.

The computed value of must equal or exceed the appropriate critical value to justify rejection of the null hypothesis at 0.05 or 0.01 level of significance. It shows whether the apparent differences or relationships are true differences/relationships or whether they merely result from sampling error [29]. Chi square test results are shown in Table 4. Fault cases for different range of error according to fault type are the calculated ones which is the observed frequency of error distribution (). Expected frequency of occurrence of error for each of the cells (column or row) for all types of fault is calculated from the observed frequency of the error using (8). is calculated for all types of fault for all the ranges of error and shown in Table 4 by using (9). Different levels of significance for different degrees of freedom are shown in Table 5. Degree of freedom can be calculated as per (10). Consider

where is the expected frequency of error, is observed frequencies in columns, is observed frequencies in rows, and total is the sum of all the frequencies = 2100. Consider

where is the observed frequency of error. Consider

where is the degree of freedom.

Table 4: test for fault location error for different types of fault.

Fault type
Parameters
Range of percentage of error

0% to ±2%
±2% to ±5%

LG

420
140

437.333
122.666

0.686
2.449

LLG

440
120

437.333
122.666

0.016
0.057

LL

520
140

515.428
144.571

0.040
0.148

LLL

260
60

249.904
70.095

0.407
1.453

Table 5: Levels of significance for different degrees of freedom.

Degree of freedom
Level of significance

5%
1%

1
3.84
6.64

2
5.59
9.21

3
7.82
11.34

4
9.49
13.28

5
11.07
15.09

In this method there are 4 rows and 2 columns, so degree of freedom is 3. From Table 5, with degree of freedom 3, calculated value is less for both 5% and 1% significant levels for all types of fault. This shows that null hypothesis is accepted and the error for fault location will not be the same for replication of experiment. Thus the proposed fuzzy based fault location scheme is accurate and can be used for series and shunt fault location estimation.

5. Conclusion

This paper proposes a new approach using synchronized phasor measurement and fuzzy system to classify the series, shunt, and simultaneous series-shunt faults and predict the fault location in a double circuit transmission lines. Proposed method is effective in determining accurate fault location because it is not affected by variation in fault type, fault inception angle, fault distance, and so forth. Fuzzy inference system used for series and shunt fault location estimation is “Mamdani” type. Fault location error in case of series fault is within 1%, while in case of shunt fault it is up to 5%. So error validation of shunt faults is done using Chi square test. The major contribution of the proposed scheme is that it classifies the fault type (both series and shunt) correctly and estimates the correct value of fault location of series faults and simultaneous series-shunt faults which has not been reported to date.

Conflict of Interests

The authors declare that there is no conflict of interests regarding the publication of this paper.

References

A. C. Westrom, A. P. S. Meliopoulos, G. J. Cokkinides, and A. H. Ayoub, “Open conductor detector system,” IEEE Transactions on Power Delivery, vol. 7, no. 3, pp. 1643–1651, 1992.

E. C. Senger, W. Kaiser, J. C. Santos, P. M. S. Burt, and C. V. S. Malagodi, “Broken conductors protection system using carrier communication,” IEEE Transactions on Power Delivery, vol. 15, no. 2, pp. 525–530, 2000.

P. Xu, G. Wang, H. Li, Y. Liang, and P. Zhang, “A new method for open conductors fault calculation of four-parallel transmission lines,” in Proceedings of the Asia-Pacific Power and Energy Engineering Conference (APPEEC '10), pp. 1–4, IEEE, Chengdu, China, March 2010.

M. Gilany, A. Al-Kandari, and B. Hassan, “ANN based technique for enhancement of distance relay performance against open-conductor in HV Transmission Lines,” in Proceedings of the Computer and Automation Engineering (ICCAE '10), vol. 5, pp. 50–54, Singapore, February 2010.

M. J. B. Reddy, D. V. Rajesh, P. Gopakumar, and D. K. Mohanta, “Smart fault location for smart grid operation using RTUs and computational intelligence techniques,” IEEE Systems Journal, vol. 8, no. 4, pp. 1260–1271, 2014.

M. Kezunovic and B. Perunicic, “Automated transmission line fault analysis using synchronized sampling at two ends,” IEEE Transactions on Power Systems, vol. 11, no. 1, pp. 441–447, 1996.

M. Korkali, H. Lev-Ari, and A. Abur, “Traveling-wave-based fault-location technique for transmission grids via wide-area synchronized voltage measurements,” IEEE Transactions on Power Systems, vol. 27, no. 2, pp. 1003–1011, 2012.

C. A. Apostolopoulos and G. N. Korres, “Accurate fault location algorithm for double-circuit series compensated lines using a limited number of two-end synchronized measurements,” International Journal of Electrical Power and Energy Systems, vol. 42, no. 1, pp. 495–507, 2012.

J. Sadeh, N. Hadjsaid, A. M. Ranjbar, and R. Feuillet, “Accurate fault location algorithm for series compensated transmission lines,” IEEE Transactions on Power Delivery, vol. 15, no. 3, pp. 1027–1033, 2000.

J. Izykowski, E. Rosolowski, P. Balcerek, M. Fulczyk, and M. M. Saha, “Fault location on double-circuit series-compensated lines using two-end unsynchronized measurements,” IEEE Transactions on Power Delivery, vol. 26, no. 4, pp. 2072–2080, 2011.

M. Kizilcay and P. La Seta, “A new unsynchronized two-terminals fault location method on series compensated lines,” in Proceedings of the IEEE Russia Power Tech, pp. 1–7, June 2005.

M. Fulczyk, P. Balcerek, J. Izykowski, E. Rosolowski, and M. M. Saha, “Fault locator using two-end unsynchronized measurements for UHV series compensated parallel lines,” in Proceedings of the International Conference on High Voltage Engineering and Application (ICHVE '08), pp. 88–91, IEEE, Chongqing, China, November 2008.

M. M. Saha, K. Wikström, J. Izykowski, and E. Rosolowski, “New concept for fault location in series-compensated parallel lines,” in Proceedings of the IEEE Power Engineering Society Winter Meeting, vol. 2, pp. 769–774, February 2001.

E. Rosolowski, J. Izykowski, and M. Saha, “Differential equation based fault location algorithm for series compensated transmission lines,” in Proceedings of the 15th Power Systems Computation Conference (PSCC '05), Liege, Belgium, August 2005.

R. Dutra, L. Fabiano, M. Saha, and S. Lidstrom, “Fault location on parallel transmission lines with series compensation,” in Proceedings of the IEEE/PES Transmission & Distribution Conference & Exposition: Latin America, pp. 591–597, 2004.

M. M. Saha, J. Izykowski, E. Rosolowski, and B. Kasztenny, “A new accurate fault locating algorithm for series compensated lines,” IEEE Transactions on Power Delivery, vol. 14, no. 3, pp. 789–795, 1999.

G. Song, J. Suonan, and Y. Ge, “An accurate fault location algorithm for parallel transmission lines using one-terminal data,” International Journal of Electrical Power and Energy Systems, vol. 31, no. 2-3, pp. 124–129, 2009.

J. Gracia, A. J. Mazón, and I. Zamora, “Best ANN structures for fault location in single- and double-circuit transmission lines,” IEEE Transactions on Power Delivery, vol. 20, no. 4, pp. 2389–2395, 2005.

A. Yadav and A. Swetapadma, “A single ended directional fault section identifier and fault locator for double circuit transmission lines using combined wavelet and ANN approach,” International Journal of Electrical Power and Energy Systems, vol. 69, pp. 27–33, 2015.

A. Swetapadma and A. Yadav, “All shunt fault location including cross-country and evolving faults in transmission lines without fault type classification,” Electric Power Systems Research, vol. 123, pp. 1–12, 2015.

S. Ekici, S. Yildirim, and M. Poyraz, “A transmission line fault locator based on Elman recurrent networks,” Applied Soft Computing Journal, vol. 9, no. 1, pp. 341–347, 2009.

M. J. Reddy and D. K. Mohanta, “A wavelet-fuzzy combined approach for classification and location of transmission line faults,” International Journal of Electrical Power and Energy Systems, vol. 29, no. 9, pp. 669–678, 2007.

M. J. B. Reddy and D. K. Mohanta, “Performance evaluation of an adaptive-network-based fuzzy inference system approach for location of faults on transmission lines using Monte Carlo simulation,” IEEE Transactions on Fuzzy Systems, vol. 16, no. 4, pp. 909–919, 2008.

S. Ekici, “Support Vector Machines for classification and locating faults on transmission lines,” Applied Soft Computing Journal, vol. 12, no. 6, pp. 1650–1658, 2012.

S. R. Samataray, “A systematic fuzzy rule based approach for fault classification in transmission lines,” Applied Soft Computing, vol. 13, no. 2, pp. 928–938, 2013.

V. Cook, “Distance protection performance during simultaneous faults,” Proceedings of the Institution of Electrical Engineers, vol. 124, no. 2, pp. 141–146, 1977.

F. M. Abouelenin, “A complete algorithm to fault calculation due to simultaneous faults—combination of short circuits and open lines,” in Proceedings of the 11th Mediterranean Electrotechnical Conference (MELECON '02), pp. 522–526, IEEE, Cairo, Egypt, May 2002.

V. H. Makwana and B. R. Bhalja, “A new digital distance relaying scheme for series-compensated double-circuit line during open conductor and ground fault,” IEEE Transactions on Power Delivery, vol. 27, no. 2, pp. 910–917, 2012.

J. W. Best and J. V. Kahn, Research in Education, Pearson Education, 10th edition, 2006.