System Design and Optimisation Study on a Novel CCHP System Integrated with a Hybrid Energy Storage System and an ORC

For achieving higher energy transferring efficiency from the resources to the load, the Combined Cooling, Heating, and Power (CCHP) systems have been widely researched and applied as an efficient approach. The key idea of this study is designing a novel structure of a hybrid CCHP system and evaluating its performance. In this research, there is a hybrid energy storage unit enhancing the whole system’s operation flexibility while supplying cooling, heating, and power. An ORC system is integrated into the CCHP system which takes responsibility of absorbing the low-temperature heat source for electricity generation. There are a few research studies focusing on the CCHP systems’ performance with this structure. In order to evaluate the integrated system’s performance, investigation and optimisation work has been conducted with the approaches of experimental studies and modelling simulation. The integrated system’s configuration, the model building process of several key components, the optimisation method, and the case studies are discussed and analysed in this study. The design of the integrated system and the control strategy are displayed in detail. Several sets of dynamic energy demand profiles are selected to evaluate the performance of the integrated system. The simulation study of the system supplying selected scenarios of loads is conducted. A comprehensive evaluation report indicates that the system’s efficiency during each study process differs while supplying different loads. The results include the power supplied by each component, the energy consumed by each type of load, and the efficiency improvements. It is found that the integrated system fully satisfies the selected domestic loads and various selected scenarios of loads with high efficiency. Compared to conventional power plants or CHP systems, the system efficiency enhancement comes from higher amount of recovery waste heat. Especially, the ORC system can absorb the low-temperature heat source for electricity generation. Compared to the original following electrical load (FEL) control strategy, the optimisation process brings overall efficiency improvements. The system’s overall efficiency was increased by from 3%, 3.18%, 2.85%, 17.11%, 8.89%, and 21.7% in the second case studies. Through the whole study, the main challenge lies within the design and the energy management of the integrated system.


Introduction
e combined cooling, heating, and power CCHP systems have the function of recovery of the waste heat to supply cooling and heat to satisfy the electrical power demand simultaneously [1]. By the other means, the trigeneration systems have advantages of high-efficiency energy transferring compared to the conventional energy systems [2]. e features of high efficiency and low emission which likely contribute significantly to reduce emissions draw a lot of attention in the recent decades.
Utilizing the recovered heat is a core technology for the CCHP systems. A general point about the CCHP systems' capacity is that the power rate lower than 1 MWe is regarded as small-scale applications. Systems with smaller capacity are called small-scale or microscale CCHP systems [3]. e small-scale and microscale CCHP systems are a popular topic as the household energy demand or small commercial applications are suitable loads for this kind of distributed energy systems and such remote loads cannot get a highefficiency power supply in common case [4]. Adollahi discusses a multiobjective optimisation on the residential smallscale CCHP system. In this CCHP system, the energy efficiency, the total installation cost rate, and the cost rate of the environment are optimised simultaneously [5]. Another CCHP system designed for small-sale applications is presented by Maraver aiming at improving the use of biomass resources and distributed generation. In that research, the concepts of artificial thermal efficiency and the primary energy saving ratio are introduced to evaluate the designed system. e results of the research show that a small-scale CCHP plant based on biomass combustion is an efficient energy generation system [6]. A multienergy products system normally needs an advanced control system [7]. e control strategy of the complex energy system is also an area many recent research studies focus on [8].
e most popular and reasonable operation strategy for CCHP systems is following thermal load (FTL) [9] and following electrical load (FEL) [10]. A domestic CHP system which is also integrated with an electrical energy storage unit is using the FEL strategy to offer electricity and heat to the demands. e final results show that, with the support of the FEL strategy, the integrated CHP system has much higher efficiency compared to conventional off-grid CHP systems. For the most popular FTL and FEL control strategy, applying either of the strategies often causes power surplus which brings an efficiency reduction [11]. In a similar system, a dynamic programming operation strategy was developed to distribute the generated energy which brings 19% efficiency improvement [12]. For solving this problem, integration of energy storage units is proposed to improve part load efficiency and operation flexibility [13]. A distributed power generation system (DPGS) with an electric energy storage (EES) system has a similar idea with the current study. e results show that the DPGS-EES system was working properly to meet the demand [14]. ere is an attempt of integrating the hybrid electrical energy storage with a domestic CHP system. e results show that Lang presents a CCHP system with the thermal energy storage system driven by a microturbine. e results of the system's operation show that the primary energy consumption of that CCHP system is significantly lower than that of conventional separate production systems [15]. A hybrid photovoltaic-trigeneration system is presented by Amir which contains batteries in its system structure. e batteries store the electrical energy from the solar panels and support the energy supplying of the system. e overall efficiency is demonstrated to be higher, and less emissions are generated compared to the current combination of centralized power plants and household heating technologies [16]. Among all the energy storage technologies, the supercapacitors have the ability to accommodate a large amount of energy in a short time. It has a similar operation principle and function with batteries [17]. When a distributed energy system has a dynamic electrical load, supercapacitors are suitable to be integrated in because of its high-power density. A CHP system combined with hybrid electrical energy storage was presented and simulated by Chen et al. In that system, the hybrid electrical energy storage system which contains lead acid batteries and supercapacitors supported the system to satisfy the dynamic load with limited energy source with high efficiency [18]. Among all the attempts, a few systems successfully combine the traditional batteries and supercapacitors with the CCHP systems.
ere is always mismatch between the energy supply and the demand, especially in the multipower products generation systems [19]. Lots of researchers have been working on this topic to avoid excess output of electricity or heat [20]. In the CCHP systems, the waste heat is recovered for improving the system's efficiency. Besides that, it is well proven in actual operational condition that there is a potential part of waste heat which can be further extracted and transferred to useful energy by the ORC systems [21]. e idea of combining the CCHP system with ORC has been tested by many former researches. Zare combines a geothermal-driven CCHP system with the ORC system. e ORC system is used to absorb part of system internal heat for higher power output [22]. In Wang's CCHP-ORC system, the fuel consumption is reduced [23]. e ORC systems have proven that part of low-temperature heat can be transferred to available electricity [23,24].
e integrated system studied in this research combines the trigeneration system, a novel electricity storage system, and the ORC system.
is new designed integrated system manages to meet the energy demand at high efficiency with its optimised operation strategy. e aim of this study is to establish a feasible solution to tackle the challenge, i.e., to investigate and develop an integrated system of combined trigeneration, energy storage, and ORC to generate multienergy products (power, heat, and cooling) with high efficiency; to reduce the energy consumption; and reduce the carbon emissions from the stand-alone systems.
is system structure shows its novelty for integrating the core components-a CCHP system, a hybrid energy storage unit, and an ORC system. Combining the ORC system and energy storage unit (including supercapacitors) with the trigeneration system is the very first attempt. e research focuses on building this integrated system and optimisation of the system's operation. Simulation on this integrated system is built from the results of the experimental tests. e optimisation process is the main content of this article. e detailed objectives of the research are as follows: (1) Investigating the state of the art of current energy systems; considering what types of the energy system and which technologies can reach the aim of the research; and selecting the energy system and technologies for the study (2) Selecting the case study of a stand-alone user demand; designing an integrated system which can meet the demand; and setting up computational 2 Complexity models to simulate and evaluate the system's performance (3) Carrying the optimisation process on the system's operation on several scenarios; displaying the best/ optimisation of the system's performance e main contribution of this article includes the following: (1) Designing a novel structure of the hybrid CCHP system and evaluating its performance (2) Investigating the control approach for the multiobject energy system and obtaining an optimised result With this newly designed CCHP system integrated with hybrid energy storage units and an ORC system, the system should have the ability to satisfy the electricity, heating, and cooling demand simultaneously with high efficiency.

System Design.
e schematic diagram of these components is displayed in the Figure 1 where the energyproducing lines are distinguished by different colours. is integrated system combines the key components to supply multitype of energy products.
e CCHP system includes a diesel engine, a generator, a heat recovery system, and an absorption chiller. e engine drives the generator to supply electricity. e generator operates with the energy storage units to supply energy for the electrical load. e electricity generated from the ORC is an auxiliary electricity source for this system (electricity from ORC is only available when the engine is operating). e function of electricity supplying of the system is given the highest priority in the system design because of the frequent changing electricity demand. e heat recovery system collects and transfers energy from waste heat to satisfy the heating demand and cooling demand. Part of the low-temperature heat is absorbed by the ORC system. When the recovery waste heat is not sufficient, the electricity is used to support the heating supply or cooling supply. e adsorption refrigerator produces most of the cooling energy. Cooling demand has lower priority than the other two energy demands.

Size of the System.
is study aims at building a micro-CCHP system and supplying according loads. Specifications about the diesel engine and the generator are shown in the Table 1. e power rate of the engine is 8.8 kW, and the output rate of the generator is 6.5 kW. Except the generated electricity, part of available power from the gas emissions and coolant water of the engine is also considered as a power source to the integrated system. e theoretical full load peak power output of the system including electricity, heating, and cooling is estimated 17.6 kW. Power demand under 13 kW is a reasonable range for this integrated system to supply. e peak power demand of the loads selected in this study is around 10 kW.

Control Strategy.
Implementation of the operation strategies aims at achieving a high efficiency to supply the load. In the control strategies which have been conducted and tested, the most popular two investigated controlling strategies for similar systems are following the thermal load (FTL) and following the electric load (FEL) [25]. e selected load lasts for 24 hours. During this period, the power demand has an unpredictable swing according to different human activities. erefore, the control strategy of this integrated system applies FEL. e operation logical diagram is displayed in Figure 2. Supplying the electrical energy demand has the highest priority. e allocation of electricity storing and consumption depends on the power demand of the load when the engine is operating. When the electrical demand is fully satisfied, the waste heat recovery system supplies energy for the thermal part and cooling part. e thermal load is satisfied by the recovered waste heat. e cooling energy is also supplied by the adsorption chiller which also extracts the recovered waste heat as energy source.
Based on the amount of energy demand, the integrated system is designed to operate as several states. e electricity demand has the highest priority, when the electricity demand is not fully supplied, and the ORC system uses the recovered heat and transfers them to electricity (when the engine is operating). When the electricity demand is fully supplied, the integrated system supplied thermal energy secondly. e supplying of cooling energy has the lowest priority. When the thermal energy generated is not sufficient for the load, the energy stored in the energy storage system supports the generation of thermal energy.

Optimisation Principles of the System's Operation.
e original strategy makes the engine to operate with a flexible range of load. A similar optimisation process is applied in the former research [26]. e optimisation process shown in this section aims at reaching the system's maximum efficiency by making the engine to work at maximum power. e engine in the system is the prime mover. It transfers the energy in the fuel into the system with certain efficiency.
e energy storage units contain the supercapacitors and the batteries. e power of the energy storage equals the summation of the two components' power.
e equation expresses the recovery energy amount from the engine.
Part of the recovery energy is used to support the operation of the ORC.
When the generator is operating, the energy using to supply the load consists of the power of generator, energy   storage system, and the electric power output from the ORC.
During the system's operation, the recovery energy is used to satisfy the heat demand. e thermal storage unit reserves part of the excessive energy.
When the generator is not operating, the energy storage units support the electric loads. Because of lacking recovery energy, the heating load and the cooling load are supplied by the energy stored in the storage units.
Supposing that the system's operation follows the electric load (FEL), the optimisation of the system aims at minimizing the engine's operation time. From calculating the difference between the minimum engine operation time and the compensational engine operation time, a better operation for the integrated system can be obtained.

Limiting Conditions.
ere are a few restrictive conditions in the optimisation process for guaranteeing sufficient power for the load. For ensuring the batteries' lifespan, the state of charge of the batteries is limited within the rage from 40% to 100%. At the same time, the power supplied by the system must be equal or higher than the power demand. e thermal energy stored in the storage units is required to fulfill the thermal load and the cooling load. e recovery thermal energy is allocated to three parts which are responsible for the thermal storage, heating demand, and cooling demand, respectively. 40% < SOC(t) < 100%, e saved energy is expressed by the following equation. e energy saving is

Model Building of the System
e principle of building the components is introduced in this section where the process of model building is expressed. e evaluation work and the optimisation process are completed by the simulation models in the Matlab software environment. e accuracy of the build System start SOC of the electrical energy storage stay above 30% The power demand is less than 2.5 kW The power demand is less than 6.5kW The hybrid energy storage units operate to supply electricity, using electrical appliance to satisfying the heat and cooling demand  components is guaranteed by fitting the performance of the components with their experimental tests results.

Generator of the System.
e electricity generation applied in this project is a diesel engine. Equation (16) describes the mathematical model of the engine.
In the equation, e engine transfers the chemical energy to mechanical energy and, then, to electricity. Model for this part is built in Matlab software. Using the corresponding parameters, the recovered heat rate is also given in Table 2.
From the simulation results of the engine's model, the engine's electrical power output and the recovery heat simulation have error less than 1.42%. ese results indicate that the model can simulate the operation performance of the engine with a high accuracy.

Heat Recovery System.
e model of the waste heat recovery module is based on the experimental results given by a former swan researcher. In the research of the biofuel microtrigeneration system, a previous researcher Hongdong tested the engine with 5 types of oil which are shown in the Figure 3 [27]. After fitting curve with the rests results, the heat recovery rate from gas oil's burning is modelled. e heat recovery system is simulated as a black box using a performance curve to fit the experimental results. ere are five operation points which are 10%, 25%, 50, 75%, and 100% load. e available waste heat and the recovered heat energy have a linear relationship based on curve analysis, and the mathematical model is shown by the following equations: (11) Figure 4 shows the comparison of test results and the simulation under different load conditions. Based on the control strategy of this integrated system, most of the recovery system's operations are settled when the engine is loaded over 60%. It indicates that the error of the recovery system's model is around 0.2% to 1.75%.

Cooling
Generation. In this integrated system, the chiller part consists of an adsorption chiller and the cooling generation appliance. e cooling generation is considered in two situations: 1, when the engine is working, the adsorption chiller absorbed the recovered waste heat to generate cooling energy; 2, when the engine is off, the cooling is transferred from the electrical appliance. e cooling power out is shown in the following formula: When the engine is on: When the engine is off:

Hybrid Energy Storage
System. e power requirement of the integrated system is a variable during the different times of the day. For supplying reliable energy, the integrated system combines the hybrid energy storage system as its energy back up to make up for the disadvantages of a distributed system. e hybrid energy storage units consist of the lead acid batteries and the supercapacitors in this research.
For optimal utilization of the energy stored in the energy storage units, the size of the batteries and the supercapacitors is calculated and selected.

Battery.
e batteries have high energy density. It is responsible for supplying enough electricity to load. e formula which expresses the operation of the lead acid batteries using state of charge as its variable is listed as follows [27]: In the equation, σ is the self-discharge rate of the battery whose value is set as 0.2% per day. C Bat is the capacity of the battery. e detail parameters of the batteries and the supercapacitor are shown in Table 3.

Supercapacitor.
In this study, the supercapacitors are selected for satisfying dynamic changing power demand. e specifications of the supercapacitor are listed in Table 4. e formula of the supercapacitor is displayed in the following equation: Here, ε is the dielectric constant, E is the electric field intensity, and C is the volume of the supercapacitor.

Working Fluid Selection.
e ORC system integrated in is designed for low-grade heat recovery. e ORC system is driven by the waste heat absorbed from the engine. Several key factors have the most significance on the ORC's performance which are source temperature, working medium, safety issues, and problem of degradation. For all the working fluids, the ODP, GWP, R134a, and R245fa are appropriate to be applied in a small-scale ORC [28]. R123a has ozone depletion potential which leads to aggravate the global warming.
e R245fa has similar chemical and physical properties as a good candidate for the ORC system. It also has zero-ozone depletion potential, low toxicity, no flammability, and applicable critical temperature and pressure. erefore, R245fa is selected as the working fluid in the ORC system. An ORC system contains several basic components: a heat source, evaporator, turbine, condenser, and pump. e waste heat recovered by this system consists of heat from the exhaust gas and the coolant of the engine. For achieving the highest efficiency during the heat transferring process, the working fluid is selected as R245fa. is working fluid has lower ebullition temperature which has lower evaporating temperature than water. Figure 5 shows the T-S diagram of R245fa in an ORC cycle. e R245fa is pumped to the evaporator, and its entropy and temperature are slightly increased before entering the evaporator. When the working fluid is leaving the evaporator, the entropy of R245fa increases compared to its state before. After that, the R245fa goes into the turbine, and the temperature decreases when its entropy slightly increases.

ORC Model Building.
Power output of the ORC system is modelled in this study, and some similar ORC system equations are also applied in the author's former research [26]: where W p is the pump's power; m ORC is the mass flow rate; η p is the pump's efficiency; and h 2 , h 1 are the inlet and outlet fluid enthalpies.
Heat accepted by the evaporator is Q ep ; ξ is the evaporator effectiveness; Q ro is the recovered thermal energy; h 2 are the enthalpies of the working fluid at the outlet of the evaporator. e process of the condenser is expressed by the following equation: In the equation, Q cd is the heat output of the condenser and h4 is the working fluid enthalpy at the outlet of the turbine. e turbine power output is In the equation, W t is the turbine output power and η t is the isentropic efficiency of the turbine.
e ORC system's overall efficiency is where η ORC is the efficiency of the ORC system. e thermal dynamic module of the ORC system was developed by the researcher from the same group. More details can be found in this research [29]. In this study, a general efficiency module is applied to represent the ORC system's ability of transferring low-temperature waste heat.

Case Study
e case study includes two parts of evaluation work on the system performance. In the first case study, the system is required to supply multitype of energy to a dynamic changing domestic load. Simulation of supplying dynamic load with this system is performed in a former research [26]. However, in this article, the energy supplying of the supercapacitor is imported. It has higher accuracy and more realistic power response compared to the former research. Also, the selected domestic load includes new load from a summer day and a winter day separately. In the second case, the system is supplied to two sets of designed loads (six scenarios of load) in two seasons. is article evaluates the system's performance of supplying energy to load through the two case studies.

Case Study 1-High-Resolution Domestic Load Supplying
Simulation.
e case study shows the optimised operation of the integrated system meeting the power demand of a domestic load in two seasons.
e integrated system is regulated to supply three energy products for two varying loads for 24 hours. e load targets selected in this case study show a seasonal difference on power demand.
In both simulations, the control strategy applies the optimised FEL power allocating strategy. Electricity demand gets the priority. e recovery heat is the available thermal energy collected from the system. Part of the recovered heat is utilised to supply cooling load. For household domestic cooling load, in this case, the cooling load is a refrigerator. e cooling load is simulated as a pulse-shape power demand. e optimisation for the operation is applied in the simulation which makes the operation time of the engine to be optimised to a minimum value.

Summer Day Case.
e first simulation is a summer day load. e operation results are shown in Figure 6.
In Figure 7, wave A shows the power demand of the domestic load on a summer day. e simulation results show that the peak power demand is larger than the capacity of the system. roughout the simulations, the system's capacity is expanded by ##% with integrating the hybrid energy storage unit. Wave B shows the engine's operation. e engine is regulated to operate only at the peak power demand period. e supercapacitors respond to high-density power demand. In the wave D, it only operates when the power demand and power supplying have sudden change. e wave C shows the power supplied by batteries which support most of the power demand when the engine is not working. Part of lowtemperature waste heat is utilised by the ORC. is part of thermal energy transmitted to the ORC is converted to electricity which increases the energy utilisation efficiency. 8 Complexity During the system's operation, when the engine is on, the ORC system utilizes the low-temperature waste heat and transfers them to available electricity. Based on the calculation of the results, the ORC contributes 2.3% electricity which brings a 2.37% increment to the electrical efficiency. e recovered waste heat is used to supply the thermal demand.
e specific thermal demand lacks data support. erefore, the heat consumption is an estimated value based on the government's data and the household's energy consumption pattern [30]. e thermal energy generated is 4.6 kWh, and it is fully consumed to supply the thermal power demand. Most of the waste heat is recovered for heat demand. e thermal energy could be either stored in a heat tank or consumed directly to the load. e system is flexible to deal with the thermal energy. e simulation results show that 41% of available energy generated by the system is consumed for heat demand.
An absorption chiller is integrated in the system for satisfying cooling demand. e simulation results show that the cooling energy demand of the selected domestic load is 4.32 kWh. e cooling load is satisfied with 25.76% recovered heating energy.

Winter Load.
In the simulation, the power source of the dynamic load consists of the engine and the waste heat recovery system. Wave A shows the power demand in Figure 7. e peak power demand cannot be satisfied by the engine alone. e hybrid energy storage unit operates as an auxiliary power supplier. In the simulation, energy storage units supplement the energy gap when the peak energy demand is larger than the rate power of engine. From the C and D chart in Figure 7, large amount of electrical energy was supplied by the batteries. e supercapacitors offered certain amount of energy in short time to fulfill the dynamic energy demand. Batteries' state of charge started from 80% and ends at 75% when the simulation ends. e ORC system in this simulation produces 0.38 kWh with the heat source recovered from the engine. e operation of the ORC system makes the trigeneration to have higher conversion rate on the waste heat energy. e electricity supplied by the ORC system takes up 2.4% of the total dynamic energy demand.
When the recovery heat is used to generate the electricity, the supplying of the heating demand is affected. In this case, as the efficiency of the recovery heat is higher than that of the ORC system, using certain amount of the recovery heat for electricity generation is under the condition that the heat demand is sufficiently supplied. e heat demand is fulfilled by the recovered waste heat. e energy consumption is an estimated value which is in a reasonable range. e winter day load consumes 5.7 kWh of heat. Most of the waste heat is used for thermal demand. Part of low-temperature waste heat is transmitted to the ORC for electricity conversion. e cooling energy consumption is 0.62 kWh in this case which is supplied with 2.7% recovered heat. Table 5. In the two simulations, the energy demands are similar, which are 12.92 kWh and 15.98 kWh, respectively. e energy demand of the target residential household has larger energy demand on a winter day than on a summer day. e engine is designed to operate at a shortest time to save energy. e integrated system satisfies the energy demand in both cases with the engine only operating at peak times. During the long off-peak time, the energy storage units supply the energy demand to the load. e ORC system transferred part of the waste heat energy to electricity. Limited by the heat source, the ORC system only generates a small amount of energy in these two cases. Although the ORC system enhances the system energy conversion ratio based on the results of the simulations, stable heat sources are necessary to have high economic efficiency. e electrical energy storage units are important in the simulation for expanding the system's capacity and enhancing the system's stability. With the energy storage units, the trigeneration system has the ability to supply load larger than the engine's rate power. e amount of energy supplied by the engine was 8.93 kWh in summer and 11 kWh in winter. At the same time, the energy storage system only supplied 3.68 kWh in summer and 4.59 kWh in winter. It indicates that the energy storage system operates as auxiliary supplied in the electric part of the trigeneration system. Combined with the energy storage system, the energy supplying has little waste. e calculation results from the generator output and energy consumption, and the efficiency enhancements of the system are 47.00% and 39.70% in this case study. In the energy storage system, the lead batteries have high energy capacity compared to the supercapacitors. e maximum error of the two sets of simulation is 2.42% and 2.15%. e average simulation errors are controlled in 1.85% and 1.79% in two sets, respectively.

Case Study 2-the Optimisation Process on Several
Scenarios. Aiming at a comprehensive evaluation on the system's performance, various scenarios of load are designed for the system's performance assessment. e cooling, heating, and electricity loads on typical summer and winter days under different conditions are given in the Figures 8 and 9. In the simulation, the loads are designed to two groups. e first groups are loads for applications on typical summer days. e second groups are loads designed for applications on typical winter days. Unlike in domestic summer load and winter load, more complex requirements on the heating, cooling, and electricity are selected in this case study. e energy consumption in the scenarios come from the cooling, heating, and electricity loads profiles for industrial, commercial, and residential areas. e system simulated in this research has the power rate same as that in case study 1. Using the system to supply a wide range of loads gives a comprehensive evaluation on the system's performance. Table 6 shows the simulation results of the system's optimised operation. Simulation results from the 6 scenarios give a comprehensive evaluation on the system' performance. Scenario one, scenario two, and scenario three simulate the system's operation on a summer day. e other three loads are designed for energy supplying in a winter day. e later three simulations investigate the system's performance on a winter day. During the system's simulation, the ORC system supplied about 10% of the electric energy demand. In the different scenarios, the energy storage units improve the system's capacity significantly. e minimum value was in scenario 5 (41.5%), and the maximum value is in scenario 6-64.15%. After the optimisation process, the system's engine operated with less time, and the system's overall efficiency is improved in each scenario. Based on the optimisation results, the engine is controlled to operate with full power rate with minimum time to satisfy the load.

Optimisation Results of Case Study 2.
Different from the previous simulation of the trigeneration system, short time of the engine's operation with full power rate improves the electric efficiency of the system. e optimisation process converts more energy to electricity from the fuel, and the higher electricity efficiency contributes to the system overall efficiency. In the first three scenarios, the overall efficiency is lower than that in the last three scenarios. e load on a typical summer day needs more cooling energy, which is the weak part of the system. e cooling energy in this system is transferred from the recovery heat. It limited the cooling energy conversion efficiency, which is the fundamental reason why the system's efficiency is low in the first three scenarios. In the last three scenarios, the system generated more heating and electricity which make the overall efficiency higher.

Conclusions
is study describes a detailed study on the optimisation of the operation of the integrated CCHP system.
In the first case study, the proposed system supplied the complex power demand with the overall efficiency 35.70% and 42.70%.
ere is over 40% efficiency enhancement compared to conventional separate production systems. Besides that, in the simulations, the optimisation process saves 3.61 kWh and 1.86 kWh in the summer case load and winter case load, respectively, compared to the original control strategy applied.   In the second case study, several designed scenarios of loads are the power demand in the evaluation process of the system. e loads show a random energy consumption on typical summer days and on typical winter days. e overall efficiency varies from 33.49% to 56.53% in the 6 scenarios. e simulation of supplying the designed load and processing the optimisation on the system shows that the system's energy performance is enhanced from 3% to 22.35%.
is study shows that the idea of this integrated system is an efficient solution of multienergy products generation. Although this structure of the energy system has the ability of handling the dynamic power supplying with flexibility, more energy source is suggested in the future research.

Future Work of is Project
(1) As an off-grid energy system, the wind turbine, and the photovoltaic panel have great potential to supply green energy to the new designed CCHP system. More energy sources are looking forward to being integrated in. (2) A more detailed thermal dynamic analysis about the system's thermal energy supplying will be carried on in the future work. (3) e control strategy of the system has potential to be improved. In the future work, the intelligent algorithm will be added in for more flexible and efficient energy distribution.

Nomenclature
P fuel : Fuel consumption (primary energy consumption) of the trigeneration system P engine : Power output of the engine generator P s : Power output of the energy storage system P SU : Power output of the supercapacitor P BT : Power output of batteries P LOAD : Electrical power demand (load) P R : Power output of the recovery system P T−ST : Power output of the thermal storage system P ET : Power consumption of transferring from electricity to thermal energy P EC : Power consumption of cooling generated by electricity P OE : Power generated from the ORC system P OT : Rate of low level heat from the ORC P ORC : Power output of the ORC system P C−L : Cooling load P: Electrical output power SOC: Batteries' state of charge te: At the end of operation time C S : Batteries' capacity W p : Power of the pump ξ: Evaporator effectiveness Q ep : Heat obtained by the evaporator Q ro : Recovered thermal energy E: Generated Electromotive Force (EMF) in volts φ: Air gap flux per pole in webers Ω: Angular velocity in radians per second T d : Developed torque in Newton-meters T d : Armature current in amperes K: Constant for the given machine η: Electrical efficiency of the engine η C : Efficiency of recovery heat transferring to cooling energy η p : Efficiency of the pump η engine : Efficiency of the engine η recovery : Efficiency of the recovery process η ORC : Efficiency of the ORC α: Ratio of recovery heat transferring to thermal load supplying β: Ratio of recovery heat transferring to cooling supplying σ: Self-discharge rate of the battery η Bat : Electricity efficiency of the battery ε: Dielectric constant E: e electric field intensity C: Volume of the supercapacitor t ′ : Optimised m ORC : Organic fluid mass flow rate W t : Turbine output power.

Data Availability
e data used to support the findings of this study are available from the corresponding author upon request.

Conflicts of Interest
e authors declare that they have no conflicts of interest.