Energy Efficiency Enhancement and Climate Change Mitigations of SMEs through Grid-Interactive Solar Photovoltaic System

According to the International Energy Agency’s estimation, Indian primary energy demand is expected to increase by about 1250 Mtoe and 1500 Mtoe by 2030. The 3 M management concept now changed into a 4 M management concept that includes energy management. In the case of energy management, the electrical energy sector assumes critical importance. An energy cost occupies nearly 30-40% of the production cost in small and medium-size enterprises (SMEs). Bureau of Energy Efficiency (BEE) has initiated a separate energy efficiency intervention to the SME’s, where the energy-efficient technologies, operational procedures, and proper awareness programs to SMEs are stated. This paper discusses the complete electrical energy audit on a small-scale Siddha and Ayurveda medicine industry. The traditional medicine manufacturing technologies make the process complex (process loads are intermittent/interlinked) during analysis. Hence, the detailed energy auditing/conservation studies on the power factor/harmonics were carried out without affecting Indian traditional medicine manufacturing technology. The postauditing design and installation of an intelligent controller by considering the intermittent/interlinked loads are carried out, and the effectiveness of the intelligent controller is ascertained with the energy conservation and the carbon emission reduction of SME. In addition, the climate change mitigation is ensured through the design and deployment of grid-interactive rooftop solar photovoltaic power plant using Solar Pro v4.5 (Photovoltaic System simulation software) with the power analysis, economic analysis and life cycle carbon emission of the proposed plant. The proposed solar photovoltaic power plant ensures energy self-sufficiency and sustainable energy utilization by carbon emission reduction on electricity utilization of SMEs.


Introduction
According to the Ministry of Environment and Forests (MOEF), 70% of the total industrial pollution of the whole nation (INDIA) is due to SMEs [1]. The Bureau of Energy Efficiency (BEE) has initiated the energy efficiency interventions in selected 25 SME clusters during the XI plan. During the XII plan, implementations of 100 technology demonstration real-time projects in five SME sectors envisaged facilitating large-scale replication of the successful technology. As per Energy Conservation Act, 2001, energy audit is defined as verification, monitoring, and analysis of the use of energy, including submission of technical report containing recommendations for improving energy efficiency with cost-benefit analysis and an action plan to reduce energy consumption. Energy auditing is a systematic approach for energy management and the first step in realizing the energy efficiency opportunities [2] with economic [3] consideration. The industrial energy audit is mainly focusing on the energy loss reduction [4] in the following aspects of the process, the operation modification, investment in energy-efficient technologies, load management, and conversion energy losses.
The power quality is a catchword that came into the power industry during the 1980s. According to the Institute of Electrical and Electronics Engineers (IEEE) standard IEEE 1100, power quality is "the concept of powering and grounding sensitive electronic equipment in a manner suitable for the equipment." The device may be anything; they will respond adversely towards the power quality issues. According to EDSA, power analytics ensuring business resilience, "30 to 40 % of all business downtime is closely associated with power quality problems" [5]. Businesses have many expensive investments towards the office, production equipment, and infrastructures. Power quality protection is a low-cost insurance policy against power wastage and accidents.
This paper deals with the objective of attaining the state of energy self-sufficient SME, and the quest for energy selfsufficiency commences once the conventional power grid is volatile and unreliable. The dependence on the conventional power grid will reduce the industry's overall productivity due to various constraints like peak time shutdown, off-peak time of operation, and high tariff with lower power quality. The paradigm shift from the conventional power grid to a nonconventional (renewable) power grid could address the issue and increase overall industrial productivity. Therefore, energy self-sufficiency is highly recommended for increasing productivity with less carbon emission through renewable energy resources.
This paper deals with the electrical anomalies that are pertaining to the power quality issues faced by a mediumscale Siddha and Ayurveda manufacturing enterprise in the complete electrical energy auditing perspective. The reflection of low power quality shows an increase in the electricity bill of the enterprise. This paper also deals with the postaudit proposal of grid-interactive solar photovoltaic (SPV) power plant for attaining the state of energy self-sufficiency of the SMEs using the Solar Pro simulation software, and it is a roadmap for climate change mitigation by carbon emission reduction.

Literature Review
The various forms of the power factor improvement in an SME unit with the underlying design calculations for power capacitors and various power quality issues in a process industry were discussed [6]. The clarity about the overall audit process of textile industry motors in turn helps us to study the old induction-type motor loads in this SME [7,8]. The process mapping of an industrial production process is a critical area that has to be taken care of to start up with the process, which helped us create a roadmap to start with the SME audit process under investigation [9].
The various economic aspects from the point of top-level management people, to implement the various collective recommendations by the electrical service company (ESCO), Industrial Assessment Centres (IAS), helped in making suggestions and recommendations for this SME [10]. The presence of power quality issues in the food processing industry was addressed, which gave clarity in the power factor capacitor's design to act as a harmonic filter to counter-effect the harmonics generated in the industry [11]. The author focused on the practical challenges in the environmental management of the Indian SMEs and its methodologies to address the environmental issues by considering the country's need and sector-specific investigation for identifying the relationship between the small SMEs [12]. The detailed energy and economic analysis for energy conservation measures help SME's energy auditing with detailed cost economics [3,13].
The energy audit is a consistent and useful tool for overcoming technological, information bottlenecks, and investment in energy-efficient measures [2]. The measurement [14] of data as a primary data collection is to understand the operation and event occurrence, calculate, explain, and validate the industry's energy consumption. The energy auditing tool [15] of Passive Home Planning Package (PHPP) and Transient System Simulation (TRNSYS) are used for energy estimation, and equivalent energy savings with greater accuracy and machine learning [16] algorithms are used for energy self-sufficiency. The effectiveness of energy audit diminishes with the number of employees increasing in the organizational size [17] in lighting, heating, insulation, and operations. The energy selfsufficiency [18] of SME is ensured by installing the SPV power plant with the sensitivity analysis of factors pertaining to the technical and economic consideration. The country's energy self-sufficiency and energy security is achieved by the 100% renewable energy transition based on the country's energy demand [19]. The renewable energy resource without or with negligible energy storage [20] is highly economical for attaining the state of energy self-sufficiency.
The solar PVsyst simulation software is used for designing the SPV plants in vessels [21]. The power and energy analysis of the designed SPV plant is carried out by the PVsyst software based on the vessel's route. The location-specific [22] solar potential and its performance can be analyzed using the PVsyst software. The 15 kWp grid-interactive SPV [23] is designed and simulated using the PVsyst software with the annual average performance ratio (PR) of 79.48%.
The design and performance analysis of 2 kWp SPV gives 73.5% with the PVsyst [24] simulation software in India's Odisha state. The economic analysis gives a payback period of 7.6 years. The annual average PR of 200 kWp simulated SPV plant is 81.7%. The real-time comparative analysis of performance ratio [25] ranges between 60% and 90%, and capacity utilization factor (CUF) ranges from 12% to 18% for the rooftop 20 kWp SPV power plant in the Telangana state of India. The design and performance analysis of 100 kWp Si-poly [26] SPV plant is carried out using the PVsyst simulation software. The annual average PR of 80% with a power generation of 165.38 MWh is achieved in the designed SPV plant.
The Solar Pro simulation software has a tremendous amount of metro [27] database for various global parts. Also, the interface for manual addition of the measured dataset makes the software more user-friendly and has greater accuracy. The design and performance analysis of 100 kWp SPV is carried out using the Solar Pro simulation software in the Telangana state of India. The Solar Pro simulation software is used for shadow analysis of the SPV plant. The seasonal tilt (or) inclination angle [27] for module mounting is calculated based on the field conditions using Solar Pro and 2 International Journal of Photoenergy obtained 30791.64 kWh/year for building energy performance enhancement. The Solar Pro software is used for 3.15 kWp SPV plant design and its fault characteristics [28] study during the faulty condition. The design and development of circuitbased solar module performance on shadow and faulty condition and its validity is verified using the Solar Pro simulation software package. The maximum power point (MPP) error of 10.17% [29] is recorded during the effectiveness comparison of the circuit-based module and Solar Pro simulator. From the review, SMEs have significant energy efficiency enhancement scope by enhancing the system's power quality. In addition, due to the various positive indices in the installation of SPV power plant in SMEs for attaining the state of energy self-sufficiency and climate change mitigation, the various commercial and noncommercial solar design and simulation packages are available. The Solar Pro v4.5 (Photovoltaic System simulation software) is used for obtaining an interactive 3D user interface for shading and designing panel mounting with more significant space and power optimization. It is also highly recommended for its unique features of calculation for shading and power analysis with minuteby-minute accuracy. Therefore, the proposed SPV's design and performance prediction is carried out by Solar Pro v4.5 (Photovoltaic System simulation software).

Methodology
The present technology practiced in Siddha and Ayurveda medicine production process is traditional cum mechanized with some modern machinery. In this enterprise, the medicine manufacturing process is undefined (i.e., intermitted in nature). The methodology of the detailed energy audit varies from industry to industry, and it is highly flexible according to the type of the industry. Here, the intermittent/interlinked traditional medicine manufacturing process is crucial to carry out the energy audit. According to the BEE guidelines, a systematic methodology for detailed energy auditing is shown in Figure 1.
The phase I: preaudit kickstarted to obtain the overall resource planning and organize the instrument for setting up a reference point for energy consumption. Here, the load curve and cost economic curves are obtained by collecting the macrolevel data from the responsible individuals and the historical dataset of the industry. The preaudit of the Siddha and Ayurvedic industry needs to be done precisely. The Indian traditional medicine manufacturing technology is unique and intermitted/noncontinuous, which cannot be altered based on the energy perspective. The lack of continuous running process machine and part loading operation is a crucial issue to address in this auditing. Therefore, planning and organizing the instruments for energy analysis and organization of resources are highly recommended.
The phase II: audit phase comprises developing the process and energy flow diagram with the active involvement of energy individuals of the industry. The survey and monitoring are carried out for all the connected loads to meet the supply and demand management of the industry. The detailed energy auditing phase is by continuous monitoring and logging of data using various energy auditing instru-ments like power on clamp meter for electrical energy studies, thermal imager for infrared thermography, and other various energy auditing instruments.
The process is followed by energy analysis using the obtained data and standard data. Based on the detailed energy audit, energy analysis is carried out. Therefore, the ENCON (Energy Conservation) opportunities proposed with the cost economics as a report to the top-level management.
The phase III: postenergy audit phase was initiated by the implementation of ENCON measures by the action plan recommended. The periodic reviews and follow-ups ensure the effectiveness of the implementation. Therefore, based on the detailed energy audit results, suggested ENCON recommendations were implemented accurately. The power quality analyzer analysis is a class "A" accuracy instrument used for continuous logging of electrical anomalies of the SME's power system on power quality issues like sag, swell, power factor, voltage-total harmonic distortion factor (V-THDF), and current-total harmonic distortion factor (I-THDF). The design and implementation of Intelligent Power Factor Controller (IPFC) and its effectiveness were studied in the post energy audit phase.
Also, a grid-interactive SPV power plant is designed and proposed with the power, economic, and carbon emission analysis using Solar Pro simulation software package for attaining the state of energy self-sufficiency SME. The feasibility study for the solar simulation was carried out by considering the various primary dataset of latitude, longitude, energy utilization pattern, connected load, energy demand, energy consumption details, building dimensions, type of building, and shade-free area (effective area) for solar module installation. Therefore, the proposed SPV plant is highly significant in energy self-sufficiency, and the renewable energy resource led to climate change mitigation.
The power quality analyzer (clamp-on-power meter) shown in Figure 2 is used at the vicinity of the point of common coupling (PCC) for the main power distribution panel in order to calculate the energy utilization pattern of the entire enterprise. Figure 3 shows the energy auditing carried in the enterprise. The power meter clamp is calibrated in threephase-four-wire configuration for detailed power quality and energy analysis of the enterprise. After the energy auditing analysis, the power quality issues have arrived. The graph gave the plotted results of the analysis and interpreted the same in the analysis. The power quality graphs show the total voltage, total current, power (real (kW), reactive (KVAr), and apparent (kVA)), power factor, voltage-total harmonic distortion factor (V-THDF), current-total harmonic distortion factor (I-THDF), and frequency.

Results and Discussion of Preaudit Phase
Energy auditing started with the collection of load curves from enterprise historical data. The load curve gives the necessary prerequests to carry out the energy auditing in the enterprise. The primary vertical axis of Figure 4 illustrates the enterprise's annual load curve, and the secondary axis gives the month-wise energy cost of the enterprise in the overall annual load curve. This load and cost curve reveals 3 International Journal of Photoenergy the preaudit phase of an energy audit by revealing a power consumption pattern. The overall electrical energy consumption concerning time gives the industry's loading pattern for a particular time. Figure 5 shows the gives of time versus voltage performance of the enterprise. The analysis starts from the beginning of the load to the load's termination to study the starting spikes or surges in the power system by connecting the power on clamp meters on the PCC. From the voltage profile, it is inferred that the presence of voltage unbalances in the system. The 5% voltage unbalance will increase the current consumption by 1 to 6 times of rated current consumption and reduce the efficiency of the electric motor load in the power system. Figure 6 shows the graphical representation of the time versus the current profile of the enterprise. The phase-wise current consumption is R-phase (A), Y-phase (A), B-phase (A), and neutral (N), respectively. Here, nearly 30 A of neutral current is present in the unit, and the total current is about 35 A during the recording period. The presence of unbalance in the current consumption profile clearly defines the poor load sharing between each phase. The unbalanced loads and the presence of current harmonics lead to a high neutral current in the system.

Phase-I preaudit
Step-1: Plan and Organize the Audit Step-2: Walk-through Audit and Meetings with heads and energy managers Step-10 : Implementation and Follow-ups Phase-III postaudit Phase Step-9 : Reporting and Presentation to top-level management Step-8 : Cost-benifit analysis Step-7 : Identification and Development of ENCON (Energy Conservation) Opportunities Step-6 : Analysis of Energy Use Step-5 : Conduct Detailed experimentation on Industry Step-4 : Conduct survey and monitoring Step-3 : Primary Data Gathering, Process and Energy flow diagram Phase-II Audit Phase   International Journal of Photoenergy Figure 7 shows the time versus real (W), reactive (VAr), and apparent power (VA). The presence of apparent power is more in the unit. The significance of reactive power injection in the SME is a minimum value, which concludes the consequence of the enormous consumption of the real power since there is a prevalence of lagging power factor in the enterprise. The need for compensation is essential to equate the power consumption without a considerable amount of wastage. Figure 8 shows the graphical representation of time versus % voltage-total harmonic distortion factor (V-THDF) from the graphical representation; the Y-phase voltage THDF is higher than other phases. At the PCC, the maximum allowable V-THDF is of 5% as per the IEEE 519-2014 and IEC 61000 standards. This voltage harmonic distortion in the enterprise is under the Central Electricity Authority (CEA) regulations. The presence of poor V-THDF directly reflects the temperature rise of the electric motor load in the enterprise. As the temperature increases, the efficiency of the motor drastically decreases. Figure 9 shows the time versus current-total harmonic distortion factor (I-THDF). At the PCC, the maximum allowable I-THDF if of 8% as per the IEEE 519-2014 and IEC 61000 standards. The presence of harmonics in the Yphase has higher value compared that with the other phase harmonics. The overall harmonic level of the enterprise is exceeding the central electricity authority rules and regulations. Figure 10 gives a graphical representation of the time versus the power factor of the enterprise. The range of power factor varies from 0.65 to 0.8 without any compensation technologies. The inefficient, ancient, and rewinding induction electric motor loads are the primary sources for producing low power factor. Figure 11 gives the graphical representation of the time versus frequency of the enterprise. There is no significant variation of frequency. Therefore, skin effect is minimum in the SME.
The enterprise has low power quality indices like lagging power factor, voltage, and current harmonic distortion, which unbalance from the detailed energy audit analysis. Therefore, the harmonic mitigating filter circuit is highly recommended, and proper load balancing between the phases is essential for better power quality. Also, the power factor improvement capacitors will address the above-mentioned power quality issues by the compensation technique.
From the detailed energy auditing, it is perceived that there is an unbalance exists in phases [30]. The loads are not evenly distributed in the system, and several loads are critical, which generates positive, negative, and zero sequence errors. Frequency variations are high due to nonlinear loading examples like Hammer Machine, Ball Mill. The power factor for the motors is about 0.65. Total harmonic distortion factor (THDF) is higher in the Y-phase, which recorded as 14%, which is above IEEE standard limits of V-THDF of 5% and I-THDF [31] of 8% at point of common coupling (PCC) as per the norms of Central Electricity Authority (CEA).
There are steps to study the sequence of operation of a particular medicine manufacturing process to get rid of the harmonic prone environment. The electrical operation is scheduled accordingly to the phase balancing with careful consideration of critical and nonlinear loads without affecting their traditional operations during the production process. This will reduce the neutral current and enhance the overall power quality of the enterprise.

Condenser Calculation of Intelligent Power Factor
Controller (IPFC). The required leading KVAr compensation by P.F. correction equipment [32] The sum of the machine's horse power rating is the active power for the power factor improvement calculation from 0.65 to 0.99.
The leading reactive power (KVAr) was supplied by power factor correction equipment = 72,052:41 KVAr.
The KVAr compensator rating of 72,052.41 is sufficient to enhance the power factor.  Figure 12 shows the Intelligent Power Factor Controller (IPFC), a smart, simple, accurate [33], and robust reactive power compensator. It is versatile in power factor mitigation [34] by its smart features of load sensing and storage of historical datasets. The IPFC is powered by various combinations of power capacitors for reactive power compensation [32]. The AT89S52 [35] is low power consuming, high-performance 8-bit Microcontroller with 8 k bit in-system programmable flash memory.
It provides the following standard features: 32 input-output lines, 256 bytes of RAM, watchdog times, two data pointers, fully duplex serial port, clock circuit, and memory storage facility. The voltage and current transformers are used to sense and measure the system's input voltage and current. The zero-crossing filter is used to obtain the instantaneous voltage and current point at which there is no voltage and current, respectively. The IPFC is equipped with the data storage facility for logging of present load and historical    International Journal of Photoenergy datasets for better reliable and faster compensation. The relay circuit is to electrically make (turn on) and break (turn off) the shunt capacitors [36] from the system. Based on the controller's load-sensing signal, the switching on and off of shunt capacitors is carried out. The relay drive is powered by the embedded system [37] to reduce the overall system cost to have robust, accurate control, and cost-effective.

Results and Discussion of Postaudit Phase
The postaudit phase is carried out to calculate the effectiveness of the installed IPFC unit. Figure 13 gives the graphical representation of the time versus voltage profile of SME after improvement using IPFC installation. The IPFC unit's installation achieves a 5% increase in the voltage profile. Figure 14       International Journal of Photoenergy power is achieved by installing the IPFC unit in the SME. Figure 16 gives the graphical representation of time versus the overall power factor of the SME at the point of common coupling after the installation of the IPFC unit. The 65% increase in the overall power factor is achieved after installing the IPFC unit in the SME. Figure 17 gives the time versus total voltage harmonic distortion factor after the installation of the IPFC unit. The V-THDF of 1.6% is within the IEEE 519 standards and limits under central electricity authority guidelines. Figure 18 gives the time versus total current harmonic distortion factor after the installation of the IPFC unit. The I-THDF of 4.8% is within the IEEE 519 standards and limits under central electricity authority guidelines. Also, the 27.27% reduction is achieved in the neutral I-THDF after installing the IPFC unit. Figure 19 gives the graphical representation of the time versus frequency profile that ensures the less amount of skin effect after installing the IPFC unit. Figure 20 gives the graphical representation of the exact comparison of power factor before and after installing power factor improvement capacitors (Intelligent Power Factor Controller). The average increase of lagging power factor from 0.6 to 0.99, with the IPFC controller's installation, is ascertained and shown in Figure 20. The 65% increase in the lagging power factor is achieved after the installation of the IPFC.

Climate Change Mitigations through Power Factor
Improvement. According to the Energy Information Administration (EIA), the USA, the electricity utilization holds 37% of carbon emission in the overall greenhouse gas emission. As per the CEA of India [38], 1 kWh of electricity emits 2 kg of CO 2 . From the detailed energy audit, we came to know the amount of CO 2 emitted from the enterprise operation.
The per-day power consumption is of 208 kWh before improvement; therefore, the following carbon dioxide emissions are calculated as follows: CO2 emission = 416 kg of CO2 per day ð6Þ 6.1.2. CO 2 Reduction after Power Factor Improvement.
CO2 emission = power in kWh/day ð Þ * 2 kg of CO 2 ð7Þ The per-day power consumption is of 205.92 kWh before improvement; therefore, the following carbon dioxide emissions are calculated as follows:

10
International Journal of Photoenergy Therefore, per day saving is 4.5 kg of CO 2 .
Per year saving of CO 2 = 1296 kg of CO 2 : ð9Þ

Design of Proposed Grid-Interactive Solar Photovoltaic System
Based on the detailed energy audit of the SME, the gridinteractive photovoltaic system is proposed for climate change mitigation and designed by the Solar Pro v4.5 (Photovoltaic System simulation software). As per norms of Central Electricity Authority (CEA) and Tamil Nadu Electricity Regulatory Commission (TNERC), 100% of the sanctioned demand [39] can be taken as the capacity of a grid-connected solar photovoltaic rooftop system. Also, the overall energy self-sufficiency is ensured via SPV installation sustainably. Figure 21 gives the overall single line diagram of the proposed 100 kWp solar photovoltaic power plant created using the PVsyst software. The general construction of the plant is divided into three prominent cases as PV array side (includes PV array and diodes), system side (includes inverter and its energy out), and load side (includes load, energy used, energy over, and energy back-up) for ease of operation and maintenance purposes. A 360 Wp polycrystalline module powers the 100 kWp SPV plant with a compactable string inverter for better grid interaction.

11
International Journal of Photoenergy Figure 22 gives the 3D CAD simulation of the proposed 100 kWp SPV plant. The interactive 3D CAD of Solar Pro software aids in developing the virtual design of 100 kWp SPV plant in the SME enterprise, which creates better performance optimization like shading and space distribution of SPV module installation in the premises of the enterprise.
The space optimization of the SPV plant is carried out by 3D CAD simulation of the proposed plant. The module-level dimension specifications are given as input, and optimal string and array combinations arrive by considering the inverter specification's capacity. The real-time two primary criteria are weight distribution for load-bearing capacity of the building and space availability for demand and installed capacity match. The ample space is available in the SME for the installation of the SPV plant. Therefore, space optimization is carried out by choosing the weight distribution for load-bearing capacity in the building. According to the guidelines, space and weight distribution are precisely taken as 30 kg/m 2 to 60 kg/m 2 of weight distribution throughout the SPV plant's installation, including module and module mounting structure. Figure 23 illustrates the solar irradiation details like total, horizontal, and direct irradiation of the enterprise generated by Solar Pro design software. The metrological data of Solar Pro simulation software is developed with the accurate metrological dataset from the NADO (New Energy and Industrial Technology Development Organization), a Japanese weather association. The collection of 1600 location dataset is equipped with the Solar Pro software. Here, the month of March is significantly having the maximum recorded irradiation of 220 kWh/m 2 with the maximum generation potential.

12
International Journal of Photoenergy        The effect of the average increase in the ambient temperature is directly proportional to the temperature rise of the SPV module. As per the Standard Test Conditions (STC), the SPV modules perform more effectively at 25 degrees Celsius. The negative temperature coefficient of voltage and power is about -0.35%/°C and -0.45%/°C, respectively [40]. Therefore, the temperature rise directly affects the power output and efficiency [40] of the SPV plants. Figure 25 illustrates the month-wise solar PV and AC energy generation (power analysis) of the proposed solar photovoltaic power plant. The maximum peak generation of 12,000 kWh is achieved during the month of March with the maximum total irradiation. The power analysis is carried out based on the solar generation and the historical power consumption pattern of the SME under investigation. Therefore, the average generation of 8000 kWh is maintained throughout the year as a positive indicator to move forward into the proposed SPV plant.

Economic
Analysis of the Proposed SPV Plant. The economic analysis of SPV is carried out using the Solar Pro simulation software with the month-wise historical data of SME power consumption. Figure 26 gives the month-wise selling, buying, and bill reduction price of the proposed SPV plant. As per the guidelines and regulations of state and central nodal agencies, the selling price of the SPV power plant is fixed. The higher average annual bill reduction is achieved based on the economic and power analysis due to the maximum SPV power generation, excess power evacuation (power export), and optimized energy utilization of SMEs. Figure 27 gives the month-wise load energy (i.e., load consumption and AC energy generated by the proposed SPV power plant of SME in the primary vertical axis). The secondary vertical axis gives month-wise cost economics of energy consumption and its bill reduction due to SPV power penetration and power export to the grid. The period from March to May is having the highest SPV generation and bill reduction. The average energy bill reduction (savings) is significantly maintained throughout the year. Figure 28 gives the economic payback period of 7 years on the proposed SPV plant, which is a positive indicator for the proposed SPV power plant.

Life Cycle Carbon Emission of the Proposed SPV Plant.
The life cycle carbon [41] emission of the proposed solar power plant is calculated in detail with the SPV modules, supports (includes the balance of system and other auxiliaries), and inverters. The amount of carbon emission generated from the proposed SPV plant's installation and operation is about 188.61 tCO 2 for the 30 years lifetime of the SPV plant. Therefore, the replacement carbon emission is based on SPV power generation as per the Central Electricity Authority (CEA) guidelines and regulations.
The carbon emission of grid-interactive SPV is taken, and the replacement emission is calculated as 4694.8 tCO 2 with the annual SPV power production of 167.17 MWh. The following International Energy Agency (IEA) considerations like the SPV power plant lifespan of 30 years, the 1% annual degradation, and the grid lifecycle emission of 936 gCO₂/kWh are 15 International Journal of Photoenergy considered for the calculation of CO 2 emission balance analysis. Therefore, the resultant CO₂ emission balance of 4506.2 tCO₂ is achieved from the proposed SPV power plant.

Conclusion
Complete electrical energy auditing was carried out. Based on the detailed analysis, the following suggestions and recommendations are prepared. The design and installation of 73 KVAr compensator capacitors will enhance the enter-prise's power factor to improve the SME's overall energy efficiency. The effectiveness of IPFC is ensured by 33.33% current reduction, 28.88% total power consumption reduction, 27.22% neutral I-THDF reduction, and a 65% increase in the overall power factor. Therefore, the effectiveness of installed Intelligent Power Factor Correction (IPFC) panel is highly significant, and it could enable the cost-effective, accurate, and high-performance reactive power compensation by installing the IPFC unit in the point of common coupling (PCC) instead of going with the load side reactive  power compensation to get the desirable compensation. There is a significant reduction in the enterprise's power consumption by installing the IPFC compensator, paving a roadmap to achieve climate change mitigation by reducing carbon dioxide emission by reducing 1296 kg of CO 2 from the electrical power consumption.
From the design of the SPV power plant, the availability of SPV potential, energy, and cost economic performance is highly feasible for SMEs to deploy the SPV power plant. The SPV energy generation and utilization lead to energy bill reduction of SME and additional revenue by exporting the excess power to the grid. The replacement carbon emission of 4694.8 tCO₂ is possible by the installation of the proposed SPV plant. Therefore, the proposed solar photovoltaic power plant is highly feasible to deploy in the SME for its energy and economic savings with the more significant environmental sustainability for climate change mitigation. Therefore, the energy self-sufficient of SME is highly feasible by the proposed SPV plant in a sustainable manner.

Data Availability
The data used to support the findings of this study are available from the corresponding author upon request.