Optimization of a Hybrid Off-Grid Solar PV—Hydro Power Systems for Rural Electrification in Cameroon

,


Introduction
Tere has been a rising global attention on power supply policies with the aim of establishing sustainable strategies to meet the ever-growing demand.Tese strategies emphasize three quintessential goals surrounding the energy challenge: power supply security, power afordability, and environmental sustainability.Tis is a serious concern especially in developing countries.About 17% of people do not have access to electricity globally, out of which 85% reside in rural areas; with a greater percentage from sub-Sahara Africa [1].Most rural households use diferent sources of energy, with a huge reliance on biomass for cooking/heating and backup diesel generators for lighting, as well as candles and kerosene for lighting by those who cannot aford a diesel generator.Te consumption of these energy sources has known alarming consequences such as the fact that biomass and fossil fuel combustion emit poisonous chemicals which are harmful to the environment.Renewable energy (RE) is increasingly being used in reducing the defcit between power demand and supply [2].Other induced drivers are the environmental concerns of fossil fuel usage and climate change challenges [3].Renewables such as wind, hydro, and solar energy are essential for developing sustainable power systems for communities deprived of access to power.Te solar PV technology, among other renewables, has a lot of prospects because of its availability and environmental friendliness [4], but variations in solar irradiance limit the ability to reliably supply appliances without hybridizing with other energy sources.Te RE systems when coupled in a hybrid confguration are more reliable in the delivery of electricity [3].Microhydroelectric facilities are renewables with the potential to resolve the low rural electrifcation issue in of-grid communities.Te implementation of a microhydropower is shown to have a relatively less environmental impact on aquatic life such as fsh.Tis is more evident with the advancement in technology.For instance, there is an evolving hydro turbine technology such as the Archimedean screw turbine which is friendly to aquatic species like fsh [5].
As the solar PV penetration in the network increases, its impact on grid planning, system security, scheduling, and control becomes steadily more prominent [6].Tere is a need for control mechanisms and adequate reserve capacity in the power system to mitigate these impacts.Interestingly, the hydropower system has the capability of rapidly regulating system variables especially peak regulation, modulating frequency, and system emergency standby [7].Tese properties can be used in the compensation of the fuctuating solar PV output and hence, supply stable electricity to users.
Cameroon's location around the equator in West Africa and its tropical climate expose it to sufcient global solar insolation with a GHI ranging between 4.9 kWh/m 2 /day and 5.8 kWh/m 2 /day [8].Te mean annual daily global solar irradiation is about 5.2 kWh/m 2 /day with peak sun hours of about 5 h per day thus, making solar energy a promising energy source.Cameroon has many small-scale to largescale rivers with the potential for power production especially in remote areas [9].It is reported that Cameroon has the third largest hydropower potential in Africa, after Congo-Kinshasa and Ethiopia, with a possible exploitable potential of 103 TWh per year [9].However, available data for small rivers in Cameroon are scarce, and this necessitates the need for the government to ease the acquisition of this information for scholars.Research on the subject of hydrobased hybrid system optimization is limited, especially for Cameroon.As of 2019, Cameroon's rural electrifcation rate was 32% while the national electricity access rate was 63% [10].Previously, the electrifcation of rural areas was mainly through grid extension but this option has been quite slow, as shown by the progress in rural electrifcation.Tere are challenges in the energy sector in Cameroon such as low clean energy access, rising energy demand, high grid extension costs, and regular power outages [11].Grid extension to remote areas is often challenged by the high cost and rugged nature of of-grid communities such that pursuing this choice becomes uneconomical [3].Worst is that, some of these remote locations are sparsely populated, making them less attractive for investors and technically challenging for developers [3].Sparsely populated areas promote power losses through the distant distribution of electricity among users.Tis shows that of-grid systems are therefore highly favorable for supporting these locations.
While the government's efort has been previously on grid extension and recently on the installation of standalone thermal plants, some nongovernmental organizations (NGOs) have installed of-grid renewable energy systems in some rural areas.Te of-grid thermal plants installed by the energy of Cameroon (ENEO)-power utility company-have some issues such as environmental pollution, high fuel costs, and high operation and maintenance (O & M) cost.In 2018, the government began, through ENEO, a program to hybridize these of-grid thermal plants with renewable power sources, mainly using solar PV [12].Currently, there is a pilot hybrid solar PV-thermal power plant in Djoum with a 369 kWp solar PV plant.Te of-grid systems installed by NGOs are not properly optimized.No comprehensive study has been done to determine the reliability, performance, and sustainability of the hybrid power stations in the Cameroonian context.Moreover, the Tongou hydropower station installed by an NGO sufered from acute power outages owing to poor system design [11].Tere was a situation of complete disappearance of the river hosting the microhydroelectric station, causing periods of no power production.Tis is a serious problem as most of these NGOfnanced power projects are either loans or donations to the villages with the potential of acting as a barrier to the uptake of renewables by reducing the confdence on these systems.Tis study contributes to the existing gap regarding hybrid of-grid systems in Cameroon by assessing their feasibility and sustainability in solving the rural electrifcation challenge, as well as illustrating how the cost of energy could be drastically reduced with the generation of power from more small hydroelectric plants.Also, a grid extension analysis is conducted to determine the point at which grid extension is cost-optimal and deduce which option (standalone system or grid extension) is best for the community.Promoting rural mini-grids by conducting in-depth technical study of system reliability, performance, and investment indicators is fundamental as it helps developers to ensure that the systems are technically and fnancially sustainable.Tis study will assist in reinforcing the implementation of ENEO's hybridization program and NGO-fnanced of-grid systems in the country.Moreover, this study will provide information on mini-grids as a suitable solution to improve rural electricity access.Tese data are needed to stimulate the upscaling of the hybrid systems in Cameroon as well as methods of hybrid system optimization.
Tis study focuses on the optimization of a hybrid solar PV and microhydro system with a battery storage to be deployed in a rural community in Menchum District, Cameroon.Tis community is of-grid.Te system is designed in a way which ensures that the loads are reliably met by the system.Te HOMER Pro software and genetic algorithm (GA) were used in the study.A comparative study at the economic level showed that regulating the hydropower capacity was capable of reducing the system LCOE and reconfguring the entire architecture.

Literature on Hybrid Renewable Optimization.
Hybrid system optimization is challenging because of aspects such as variability in power demand, nonlinearity of RE components, numerous parameters, and the 2 Journal of Electrical and Computer Engineering interdependence of the control strategy and the optimum confguration [3].Te optimization of the system is important as it helps ensure the least investment while fully utilizing the resources and system components.Te reliability of the energy system to meet the load and the lifetime system cost are major targets of the optimization.
Many studies have been conducted on of-grid renewable solutions for communities.In order to determine the feasibility of of-grid renewable energy supply to touristic sites in Australia, studies by [13] used the NPC, faction of renewable, and payback period as factors to base their decision on choosing the best option.In Cameroon, the scholars in [14] conducted studies on the simulation of standalone systems for rural communities with power needs ranging from 0 to 50 kW.Teir aim was to fnd a suitable way of supplying electrical energy to these localities.Te scholars in [15] simulated a hybrid microhydro PV system in Batocha-Cameroon using the HOMER software.Similar studies were conducted by [14] on an of-grid energy system in Cameroon using HOMER with consideration of combinations involving hydro-diesel generator-solar-LPG-battery.Tey all used a hypothetical load profle with no aspect of productive use of energy considered.Also, a diesel generator (DG) was part of the optimal system selected which does not currently ft into the government's plans of phasing out all thermal plants.Similar studies in Cameroon by [16] using the particle swarm optimization (PSO) to design a hybrid ofgrid power system were conducted.Te study presented the battery-PV-DG as the optimum confguration at an LCOE and NPC of 0.132 $/kWh and $38,817.7,respectively.Te PSO and diferential evolution (DE) were used in the optimization of a hybrid battery/PV/hydro system, and the results obtained were an optimum NPC and LCOE of $93,958.07 and 0.06192 $/kWh, respectively [17].Still in Cameroon, a study by [18] using the HOMER software to design an optimum microhydro/DG/PV/battery architecture with an LCOE of 0.443 $/kWh.Te feasibility of an ofgrid hybrid Hydro/PV/Wind in six sites [19] was assessed in Ethiopia with the aim of supplying cost-efective power to rural communities.Te researchers used HOMER Energy for optimization and obtained diverse system confgurations with LCOE less than 0.16 $/kWh.Studies by [20] reported that the PV/wind/diesel/battery hybrid system was a feasible option for of-grid supply of electricity to rural areas in Pakistan.Te HOMER results indicated that the hybrid system was attractive with a renewable energy penetration of 84%, an LCOE of 0.45 $/kWh, and a 69% reduction in greenhouse gas (GHG) emissions.Another study has been done in 10 rural villages in Iran, comprising a hybrid PV/ DG/battery system using HOMER [21].Te LCOE obtained from the various options was in the range of $0.615 to $0.722.Techno-economic analysis on a hybrid PV/DG/ battery was conducted by [22] on a university campus in Delhi using HOMER.Tey obtained an optimal system with an NPC of $170,348 and an LCOE of 0.090 $/kWh.Still on campus in Delhi, a techno-economic analysis of of-grid PV/ DG/battery was conducted by [23] using HOMER, where the optimal system gave an NPC and LCOE of $639,981 and 0.34 $/kWh, respectively.
A metaheuristic bonobo optimizer (BO) was used in the optimization of an of-grid hybrid wind-DG-PV-battery in a rural area in Saudi Arabia [24].Teir objective was the minimization of the annualized system cost (ASC), and the algorithm found a least ASC of $149,977.2.In [25], the PSO and Monte Carlo techniques were used to optimally size a PV-wind-battery with minimization of the total annual cost (TAC) as an objective function.In [26], a genetic algorithm (GA) was used for the optimum sizing of a PV-wind-batterysolar collector system with the minimization of NPC as an objective function.Tese metaheuristic algorithm-based research studies for of-grid rural electrifcation are focused on parameters like ASC, NPC, LCOE, and loss of power supply probability (LPSP).without a justifcation on whether these systems need to be deployed as of-grid systems or if there's need for extension of the existing grid.Tis is pertinent in the context of rural electrifcation where policies need to be backed by compelling and established research on which options are much better and why.Tere is a need for a grid extension analysis where stakeholders are provided with information on whether the standalone option is worth pursuing even if the other economic indicators are promising.However, the scholars in [27,28] agree that the PSO and GA are amongst the most promising optimization methods used to solve the energy system optimization problem, and this is corroborated by several publications.Generally, the inferences drawn from the works in [27,28] are that the GA is scalable, independent of the initial solution, and can easily be merged with other techniques.For the PSO, the algorithm evades the complex model and high computational burden of the GA, and its implementation is simpler.Nonetheless, the downside of PSO is that it is not robust, especially when the dimensions of the problem are large.Genetic algorithms are well-suited for complex optimization problems with a large search space, making them particularly efective for sizing decisions that involve multiple parameters and interdependencies.GA employs a population-based search strategy that enables exploration of the solution space concurrently.Tis feature is advantageous when dealing with renewable energy systems, where the optimal sizing may not follow a direct path and needs exploration of various confgurations [3].Terefore, this study will use the GA for validating the results obtained from HOMER.Te peculiarity of meta-heuristic approaches is that they can be adapted to several problems with no signifcant changes in the algorithms, hence the name meta.Table 1 provides a summary of other studies and limitations identifed.

Contribution and Paper Outline.
Most of the studies on RE system optimization have been focused on optimal system confguration and cost minimization without highlighting the contributions of the subsystems to the costoptimized function.Although most of the authors focused on techno-economic assessment, they fail to present a comprehensive route for validating the results obtained in a way that provides a clear contrast between optimization techniques.For example, in the studies that used more than one tool to conduct the optimization, the choice of tool was  [14] Rural area, Iran Te PSO and Monte Carlo technique were used to optimally size a PV-wind-battery with minimization of the total annual cost (TAC) as the only objective function.Te optimal was wind/battery system with a TAC of $17183.11which was lower than that of the other confgurations such as PV/wind/battery and PV/battery) Comparison with only stochastic tools, no grid extension analysis, TAC was the only parameter, no analysis of system reliability [29] Rural area, Cameroon Simulation was done with HOMER.Te optimum architecture was 5 kW PV, 2.12 kW hydro, 1 kW diesel; 125 battery, 6 kW inverter, and 6 kW rectifer.Te microhydro-PV-diesel-battery system gave a total NPC of $70,042 and LCOE of 0.278 $/kWh No assessment of grid extension, no comparison with another tool, the use of diesel which is polluting [15] Rural area, Saudi Arabia Four metaheuristic algorithms (big-bang-big-crunch (BBBC), GA, crow search (CS), and the butterfy optimization algorithm (BOA)) were used to compare with the bonobo optimizer.Te optimal hybrid wind-diesel-PV-battery gave a minimized annualized system cost (ASC) of $149,977.2No assessment of grid extension, all tools used to compare were AI-based, use of diesel [24] Multimedia center, Cameroon PSO was used.Te optimum PV-battery-diesel system gave an LPSP, LCOE, NPC and emissions of 0.003%, 0.132 $/kWh, 38,817.7 $, and 2.2 kg/ year, respectively No grid extension analysis, no comparative analysis with another software, the use of DG [16] Rural area, Pakistan Simulation was done with HOMER.Te optimum confguration had 10 kW PV, 20 kW wind capacity, 30 kW diesel, 50 batteries, and a 50 kW converter.Te feasible option had a renewable energy penetration of 84%, LCOE of 0.45 $/kWh and total NPC of $359,465 No grid extension analysis, no comparative analysis with another software, the use of DG [20] University campus, India Simulation was done with HOMER.Techno-economic analysis on a hybrid PV/DG/battery.Tey obtained an optimal system with an NPC of $170,348 and an LCOE of 0.090 $/kWh No grid extension analysis, no comparative analysis with another software, the use of diesel [22] Rural area, Cameroon Tey used DE and PSO.Te optimization of a hybrid battery/PV/hydro system and the results obtained were an optimum NPC and LCOE of $93,958.07 and 0.06192 $/kWh, respectively No grid extension analysis, no comparative analysis with another software [17] Rural area, Iran Simulation was done with HOMER for 10 rural villages with a system comprising PV/DG/battery system.Te LCOE obtained in the various options were in the range of $0.615 to $0.722 $/kWh.Meymand village gave the best performance (NPC of $12053 and LCOE of 0.615 $/kWh) was the most appropriate option No grid extension analysis, no comparative analysis with another software, the use of diesel [21] Rural area, Cameroon Simulation was done with HOMER.Te PV/diesel/small hydro/battery was found to be the most viable economic system for Southern Cameroon with a 0.443 $/kWh energy cost No grid extension analysis, no comparative analysis with another software, the use of diesel [18] Rural area, Ethiopia HOMER was used in the study.Te optimum confguration was hydro/ PV/wind with LCOE less than 0.16 $/kWh and an NPC of $246,787

Journal of Electrical and Computer Engineering
No comparative analysis with another software, no grid extension analysis [19] 4 Journal of Electrical and Computer Engineering all from a particular category such as all meta-heuristics.Tis study attempts to compare the soundness and robustness of a commercial tool like HOMER Pro and an AI-based algorithm like the GA so that inferences could be made from the results obtained.A summary of the novel insights and contribution is presented as follows: (i) Tis study uniquely demonstrates, through a sensitivity assessment, how the increase in hydropower capacity can afect the optimal system confguration as well as the LCOE.Tis will have policy implications in Cameroon which has a longstanding history of supporting large hydropower installations while ignoring microhydropower development.(ii) Application of a multiobjective GA and HOMER Pro software is used to solve the sizing and cost optimization of a hybrid of-grid hydropower-solar renewable energy system.By comparing HOMER with GA results, the study aims to bridge the gap between a widely adopted commercial tool and a machine learning-based approach, providing insights into the applicability, advantages, and limitations of both.(iii) It explores the design of a hybrid power system while upholding the technical sustainability and cost tradeof through manual calculation, an aspect which is still a black box to energy experts.(iv) It identifes the best rural electrifcation option through exploiting HOMER's grid extension assessment database where cost-optimized analysis is conducted between the of-grid system and the nearest grid-connected community.(v) Instead of focusing on designing a single energy system as is common in most tools, the study exploits HOMER's ability to fexibly suggest several electrifcation options while selecting the optimal alternative based on the elimination criteria.
Comparative studies on 68 tools for renewable energy system analysis indicated that HOMER was one of the most appropriate tools for conducting optimization of both ofgrid and on-grid systems [30].Tis was further supported by [31], who pointed out that HOMER was a widely used and popular software.Te HOMER software is widely used for the design of RE systems and will be used in this study to optimize the hybrid PV-hydro RE system alongside the GA method for validation of the fndings.HOMER has an intuitive user interface, it is consistent in its energy system design, and is reliable.Terefore, it has been used in this study.Cameroon has relatively exploitable amounts of solar irradiation by virtue of its location near the equator and satisfactory hydroelectric potential in several communities.Tis implies that the country's precarious rural electricity access situation could be addressed through hybrid system combinations particularly in those locations where these resources are present.Tis research examines the feasibility of using an of-grid solar/microhydro renewable energy system for afordable electricity generation to meet the power demand of a rural area in Cameroon.Here, the system is sized in line with the solar/microhydro resources and the power demand of the location.Ten, an economic analysis is done on the hybrid system while comparing it with other supply options such as grid extension or a standalone system.In addition, a sensitivity assessment is conducted to explore the infuence of increasing the hydropower capacity on the system confguration and LCOE.
Te initial part of the study is an introduction which is followed by a review of the literature on RE optimization.Moreover, the methodology is presented with an elaboration of the modeling of system components.Te results and discussion are equally presented with the major fndings of the study.Finally, the study ends with a summary of the results.

Materials and Methods
Te research paper used the HOMER Pro software to simulate data collected in order to determine the feasibility of electrifying a remote community in Cameroon, and the results were validated using computational GA.HOMER Pro is a unique energy modeling application which has a worldwide database of resources such as solar irradiation, wind, temperature, as well as the RE system components.Te simulation will involve several constraints and data such as the solar/hydro resource of the site, load profle, and other economic considerations.Te study used several combinations of energy resources (solar, microhydro, and batteries) while monitoring system performance factors such as the LCOE, NPC, storage capacity, and system reliability.

Study Area.
Te location of interest is a small community called Munkep, situated in the North West Region of Cameroon.It lies between a latitude of 6.742 N and a longitude of 9.98 E with an elevation of 502.6 m above sea level [32].Tis farming community is located about 23 km from the nearest electrifed community.Te map of the study area is shown in Figure 1.Te community currently uses diesel generators, solar home systems (SHSs), batteries, frewood, candles, and kerosene lamps for lighting.In the community, most households rely on diesel generators to produce electricity at a relatively high cost, and there are no plans that the grid will be extended to this community within the medium or short term.Regrettably, low-income families who survive on barely less than a dollar per day can only use kerosene for lighting and most often, frewood for cooking and lighting.Te negative efects of the kerosene and diesel generators include air pollution, health hazards, and environmental degradation.Te loads of the Munkep community will be met by a hybrid energy system which is made up of a microhydro generator as the primary energy source coupled with a solar PV and a battery network.

Objective Function Formulation.
Te main objective is to minimize the NPC which will in turn minimize the LCOE.For a hybrid system, the NPC involves several cost Journal of Electrical and Computer Engineering components discounted with a discount rate to the present value using capital cost, replacement cost, maintenance, and operation cost.Te NPC represents all the costs that occur within the project lifecycle, with future cash fows.Te objective function is represented by the following equation [34]: where C Cap is the capital cost of the system, C O&M is the system's operation and maintenance cost, and C R is the system's replacement cost.Te economic assessment in HOMER is such that it seeks to reduce the system cost and identify the optimum confguration.Te optimum hybrid system confguration is determined using the NPC, and it is also represented as in the following equation [34]: where ASC is the annualized system cost and CRF is a ratio to calculate the present value of the system components for a given time period taking into consideration the interest rate.It is calculated using the following equation [17]: where i is the interest rate, n is the project life time.
Te LCOE is equally a signifcant component of the system design and it indicates how economically proftable the system can be.It is calculated using the following equation [17]: where P load is the load power.Te loss of power supply probability (LPSP) is a measure of system reliability index which represents the potential of the system's inability to meet the load demand.It is estimated by the percentage of the energy defcit of the total energy produced by the hybrid.Te LPSP ofers information on the hybrid system reliability and it is calculated using the following equation [35]: where P load is the total system load, P PV is the total generated PV power, P Hydro is the total generated hydroelectric power, E Batt(t) is the energy stored in the battery at a time t, and E Batt_min is the minimum energy that can be stored in the battery.
An LPSP of 0% implies the load will be satisfed all the times and an LPSP of 100% implies that the load cannot be supplied at all.

Bound Constraints.
Tere are constraints regulating the limits of the solar panels, hydro turbines, and the battery system.Tey are presented as follows: 6 Journal of Electrical and Computer Engineering P Hydro_Max is the hydro turbine's maximum power, N Bat_Max is the maximum number of batteries, and N solar_Max is the maximum number of solar modules.Table 2 shows the boundary limits of the constraints used in the simulation.

Resources Assessment.
Cameroon has a fairly good solar radiation with global horizontal solar radiation fuctuating from 4.29 to 6 kWh/m 2 [36] and a huge potential for hydropower [14].Te solar resource data was obtained from NASA while the hydro resource was scaled from data used by [17] in a location with a similar rainfall pattern.

Solar Resource Assessment and
Temperature.Te solar resource information for the Munkep village was obtained from NASA (latitude of 6.742 N and longitude of 9.98E) and ranged from 4.015 kWh/m 2 /day in August to 6.047 kWh/m 2 / day in February, representing the period of the rainy and dry seasons in Cameroon [32].It is the 22 -year average insolation data.Sustainable power generation in a PV system occurs at a daily radiation greater than 3.5 kWh/m 2 /day [37].Te daily solar radiation and the clearness index of Munkep village are shown in Figure 2.
Figure 2 shows that February is the sunniest month with a solar radiation of 6.047 kWh/m 2 /day, while August has the least solar radiation of 4.015 kWh/m 2 /day.Te daily radiation reduced from February to August and later rose until December.Te trend observed in the monthly solar resource is the reverse with the microhydro resource, enabling the complementary operation of the solar and hydro systems in the hybrid topology.Te fow rate of the run-of-river falls when the solar radiation increases.
Solar module operation is greatly afected by the ambient temperature, and it is important to include the temperature efect in the model.Te dry season has periods with one of the highest ambient temperatures, while the rainy season presents the lowest ambient temperature.HOMER Pro uses the ambient temperature to compute the solar PV output power.Figure 3 shows the site's monthly average ambient temperature.
Te power output of the PV system is given by the following equation [38]: where P out_pv is the output power of the PV system, P PV_rated is the PV rated power, G is the solar radiation (W/m 2 ), G ref is the solar radiation at reference conditions (G ref � 1000 W/ m 2 ), T ref is the cell temperature at reference conditions (T ref � 25 °C), K T is the temperature coefcient of the maximum power (K T � −3.7 × 10 −3 / °C), and T c is the cell temperature which is determined by the equation [38]: T amb is the ambient temperature.

Hydro Resource Assessment.
In general, a microhydroelectric plant would generate a few hundreds kilowatts of power usually through a run-of-river scheme.Tis technique is suitable in areas where the available hydro resource possesses a low discharge.Te determination of fow rate using rainfall runof patterns was not possible owing to the enormous data requirements which were not available at the time of the study.Te site has several rivers whose stream fows were not measured.However, the annual fow used by [17] was scaled and used in the simulation.Te monthly fow data is presented in Figure 4.
Te net head used in the study was 3.2 m, and the design fow was 1000 l/s (1 m 3 /s).Te study considered a minimum fow ratio and a maximum fow ratio of 50% and 150%, respectively.A turbine efciency of 80% was used in the study.Te turbine transforms the moving water from the penstock into mechanical energy which is later converted into electrical energy by the generator.Te power produced in the hydropower system is given by the following equation [17]: where P H is the power produced by the hydro system in watts, ρ is the water density (1000 Kg/m 3 ), H n is the net head in meters (m), Q is the fow rate (m 3 /s), g is the acceleration due to gravity (9.8 m/s 2 ), η TG is the product of the turbine and generator efciency, and Q min and Q max are the turbine minimum and maximum stream fow.Te hydropower station has a limit to the power it can produce, and it is expressed as a function of the fow rate: Table 3 shows the data used in the simulation of the hydroelectric system.

Electricity Usage of the Rural Community.
Te Munkep community needs electricity mostly for domestic appliances such as lamps, TVs, radios, cell phones, and refrigerators.Tere were some considerations for community loads such as iron and computers in schools, community halls, health posts, small-scale industrial activities, and rural commercial facilities such as small processing factories for cassava four and soya bean four, cold storage, and cottage industries.Table 3 represents the list of all connected loads to the system with their unit power rating in Watts.Te demand has been Journal of Electrical and Computer Engineering estimated considering the appliance rating and use patterns for households, potential commercial activities, and energy use in productive applications.Clearly, the demand estimation is a crucial element for the entire system design, and further improvement is possible by incorporating social information of the users as well as their preferences.Te village under consideration has 100 households with an average of 5 persons per household, a community school (class 1 to class 6), a church, and a health post.To bring a little more improvement to the village, the researchers added more electric loads like four milling machine and a community water pump.Te loads like lighting, TV, radio, mobile phones, refrigerator, microphone (for the church), ofce equipment (printer, photocopy machine, and computer for the school) are taken to be primary loads, which   4 shows the loads considered in this study while Figure 5 shows the hourly load profle.

Modeling of the Hybrid Renewable Energy System.
Te HOMER Pro software was used in this study.HOMER Pro is the universal standard for optimizing microgrid design from village power and island utilities to gridconnected campuses and military bases [39].Formerly conceived at the national renewable energy laboratory and improved and distributed by HOMER Energy, HOMER (hybrid optimization model for multiple energy resources) encompasses three powerful tools in one software product, so that engineering and economics work side by side.HOMER simulates the system for power generation over the time period of 25 years at 60 minutes of interval, presenting the results for a period of one year.Te battery bank, the inverter and other important components that make up the hybrid system were also considered.Te architecture system has an AC bus and a DC bus.Te microhydro system generates AC power whereas the solar PV system generates DC power.A bidirectional converter is used to convey the excess energy in the system to charge the battery network.Te battery network intervenes only when the system cannot meet the loads.Te excess energy in the system after the battery is full, is sent to dump loads.Te schematic shown in Figure 6 shows the proposed hybrid system.

Power Management Strategy of the System.
Te management of energy in hybrid of-grid systems is essential, as it ensures system reliability and security.It makes good use of energy with minimum wastage, optimum power generation, as well as the suitable operation of system components.A procedure was created in order to show the engineering process and ofer a step-by-step way of predesigning the hybrid renewable energy solution.Te emphasis was on choosing a cost-efective renewable energy system (hybrid solar-microhydro).Te control strategy operates according to the following description: (1) Te dispatch of the subsystems of the hybrid RE has the following order of priority: hydro-solar-battery bank.Te microhydro subsystem meets the base load.When the microhydro and solar PV outputs are equal to the load power, the battery bank does not extract energy.As soon as excess power becomes available from the two subsystems (microhydro and solar PV), the optimization program redirects the excess energy to charge the battery in case the state of charge (SOC) is not at the maximum level.(2) If the total energy produced by the microhydro and solar PV is more than the load demand at any given time such that it can negatively afect the hybrid system, the energy surplus is discharged through dump loads.
(3) If the total power generated by the PV and hydro systems is less than the load demand, the energy defcit is covered by the battery, depending on the SOC.
Table 5 shows the economic parameters used in the model while Figure 7 shows the power management strategy of the hybrid system.
Te control strategy of the hybrid PV microhydro ofgrid system with storage operates according to the schematic in Figure 7. Te main generators are the microhydro and the solar PV system.Once the program starts, the algorithm verifes whether the microhydro system can efectively meet the load without soliciting power from the solar PV and battery bank.If the load is more than the power generated by the microhydro system, the power generated by the solar PV system is added while the excess power is used to charge the battery bank, depending on whether the battery SOC is less than the minimum SOC.In case the battery bank is full while there is surplus power in the network, the surplus is directed to dumbed loads (power curtailment scenario).Te fow of power in both the DC and AC buses is bidirectional with the help of a converter.

Genetic Algorithm (GA).
GA is a computational metaheuristic algorithm that is based on the natural evolution theory using chromosome structures and a recombining process during the iteration process [40].GA has 3 fundamental operators, namely, crossover, selection and mutation.Weak species in the population are eliminated so that only strong species are retained and this is executed by the selection operator.Te crossover operator searches better individuals in the population from the chromosomes of 2 parents in the population.Te mutation operator helps in mutating individuals that generate better solutions in the search space.Te mutation process retains the population variety with better solutions [41].Table 6 shows the GA parameters.
Te approach generates an initial population with individuals satisfying an LPSP less than 5% at a minimum LCOE.Te Roulette wheel approach selects the operator that randomly transfers the genes to the next generation depending on their features.After the selection, the parent chromosomes undergo the process of crossover while checking if the LPSP is satisfed by the new generation of child individuals.If the program fails to meet the criterion, the parent chromosomes are not replaced by the new generation of child individuals, but in case the new generation of child individuals satisfes the criterion, then the parents are replaced.Te individual genes change depending on the mutation rate and the LPSP criterion.Te mutation process is successful if the criterion is met.Finally, the program termination criteria are verifed and if they are met, the program stops.Te steps in the algorithm are presented below; Journal of Electrical and Computer Engineering 2.8.Sizing of Charge Controller.Te solar charge controller is rated based on the voltage and the ampacity which depend on the PV array confguration and the output current of the module supplied to the controller.A 30% tolerance is given to the charge controller ratings to cover the surge current and is given by the following equation [37]: where I R is the controller current ratings, I SC is the shortcircuit current of a single solar panel, and N p is the number of solar panels connected in parallel.Te bold values are the sum total of entries in the column where they appear.For example in category A, the bold value 24.2 represents the total kW of appliances in that category (i.e., category A).

38.80
Load Power (kW)  10 Journal of Electrical and Computer Engineering 2.9.Sizing of the Converter.From the simulation, the maximum power discharged by the battery network during peak load was 6.43 kW, and the power from the hybrid system converted for battery charging was 11.64 kW.Nonetheless, the bidirectional converter considers the maximum power converted, implying that the power contributions at the DC bus are 11.64 kW from the battery bank and 4 kW from PV, making a total of 16.64 kW.
Considering the possibilities of load growth for a period of 5 years, the inverter oversize factor was assumed to be 1.3 [37].Te converter power ratings are determined by equation (12) [37]: where P R_Con is the converter power ratings and P Trans is the maximum transferred power.

Evaluation of the Cost of the Hybrid System Components Using HOMER Pro
From the inputs, the various costs of the hybrid system components are shown in Figure 8, as simulated in HOMER Pro.It is observed that the NPC of the optimum system combination was $90,469.16.Te energy generated by all resources and the power fow from December 7 to December 13 are depicted in Figure 9. Figure 9 shows that hydropower production is highly fuctuating, as this is the dry season in Cameroon with much reduced river fow.It is also observed that the solar PV and battery provide relatively less energy in meeting the loads.Interestingly, high solar radiation is observed during this period such that the solar PV complements the defciency in the microhydro system.

Solar PV Power Generation from the HOMER Pro
Simulation.Te annual solar energy production has a rated capacity of 3.5 kW, with a maximum yield of 3.1 kW (Table 7 and Figure 10).It is seen in Figure 11 that the PV system produces electricity from 6 am to 6 pm with maximum power production occurring at noon.Tere is an average of 4 sunny hours (10 am to 2 pm) where power generation fuctuates within the range of 2.8 to 3.5 kW.Generally, it is observed that there is high solar irradiation during the months of January, February, and December.Hence, the power generated from the solar system is higher.Solar radiation, as well as the generated electricity, during the other months is marginally lower.

Solar PV Sizing.
Te 260 W Peimar SG290MFB solar panel, with an efciency of 17.8%, was selected while considering a 2000 $/kWp capital cost.An equipment lifetime of 25 years and a replacement cost of 1200 $/kWp were considered.Te system voltage (V sys ) considered in this study is 48 V, and it is used to calculate the number of panels in a parallel connection.Te derating factor used in the analysis was 80%.
Step 1. Calculating the installed power Te peak sun hours (hours at 1 kW/m 2 � kW/m 2 /day) are determined considering the worst month of the year.A peak sun hour of 4 h/day is chosen in this study.
To determine the installed power [4] ( Computing the number of solar modules in a string using a module voltage of 26.3 V [4] where N s is the number of solar panels connected in series, V m is the nominal voltage of a single solar panel, and V sys is the system voltage.
Computing the number of parallel connections using 260 Wp PV module [4] where N p is the number of solar panels connected in parallel, P PV_rated is the power ratings in W of a single solar panel, and P peak is the PV peak power of the system.Te total number of solar modules becomes [37] N T PV � N s P PV rated � 7 × 2 � 14 solar panels, (16) where N T_PV is the total number of solar panels.Te solar module considered in the study has an area of 1.627 m 2 .Terefore, the overall area needed to install the solar PV array will be [37] Area where the A PV is the area of a single solar panel.

Microhydro Power Generation from the HOMER Pro
Simulation.Table 8 and Figure 12 show the output features of the microhydro system.Power production drops during the months of November, December, January, and February due to the reduction in the river fow rate, as seen in Figure 12. December is the month which is most afected by the dry season, causing the least hydropower production.Tis power drop is supported by the battery bank and solar PV to meet the power demand.
Figure 13 shows the heat map of the annual microhydropower production where three colours are used to categorize the variation of output power throughout the year.Te red colour running from day 1 to day 280 represents the output power from the microhydro at 31.5 kW whereas the green colour represents the 24.61 kW (reduction in power generation).As for the blue colour, it represents the power output of the least power generation from the microhydropower (worst period of the year).After running the system to understand the output power for each component for one year, December 13 was found to be the worst day with the lowest microhydro output and maximum battery charging and discharging.

Battery Charging and Discharging from the HOMER Pro
Simulation.From the simulation, the annual energy supplied to the loads by the battery bank was 287 kWh/yr while the annual charging energy of the battery system was 326 kWh/yr.It is noticed that the annual battery charging energy is greater than the energy supplied to the load because the battery system charges slowly but discharges rapidly to quickly respond to the peak demand.It is recommended to charge batteries slowly, especially lead batteries, in order to extend their lifetime through a reduction in the current fowing through their terminals.
Figure 14 shows that the input power from the hybrid system used for battery charging and the battery state of charge during the months of February.February 19 to February 15 is the period with the worst battery discharge scenario where maximum battery discharge went down to 38.06% of the state of charge.It is observed that the system input power used to charge the battery reduces exponentially while the battery state of charge increases.Also, it is observed that as the battery SOC increases, less and less input power from the hybrid system is needed to charge the battery.

Battery Sizing.
After running the simulation, the battery bank's maximum power delivered in a year is 6.43 kW per hour, and hence, the load energy provided by the battery is 6.43 kWh.
Tus, the net capacity storage of the battery (B charge ) in Ah/day is [4] where DOD is the battery depth of discharge and assumed to be 40%, E t is the total load energy met by the battery bank, and V T_bat is the battery bank terminal voltage.Te battery autonomy is 1.9 hours because there is a high fow rate from the run-of-river hydro, and the optimization program supports more hydropower generation because it is cost-competitive.Terefore, Te total Ah needed in the system is determined by calculating the number of batteries connected in series and in parallel.Te selected battery is 260 Ah.
where N bat_P is the number of batteries in parallel and B Sin- gle_bat is the charge in ampere hour (Ah) of a single battery.
Computing the number of series connected batteries [4]   where N bat_series is the number of series connected batteries, V bat is the voltage of a single battery.Te total number of batteries needed in the system is [4] where N bat_Total is the total number of battery units.

Grid Extension
Analysis in HOMER Pro.Te impact of the system's LCOE is compared with the actual average cost of electricity in Cameroon without subsidy.Te amount used for the unsubsidized cost of electricity in Cameroon is 0.12 $/kWh for residential users.Te electricity tarif in Cameroon is currently subsidized by the government, and it is 0.07 $/kWh for residential customers.Comparing the unsubsidized electricity tarif helps in the identifcation of the cost-optimal solution of the mini-grid with respect to grid extension.Te extension of the medium voltage (MV) line in Cameroon is 10,000 $/km [42], with an O & M cost of 200 $/year/km.It was observed that the system's break-even grid extension distance was 2.21 km.Tis implies that the hybrid of-grid system with an LCOE of 0.0453 $/kWh is competitive for locations further than 2.21 km from the nearest grid-connected community.However, the community is about 23 km away from Esu village which is the nearest grid-connected community; therefore, the of-grid option is economical.Figure 15 shows the system's break-even grid extension distance.

Sensitivity Analysis of the Hybrid Microhydro-Solar
Battery System.A sensitivity assessment is required to examine how system variables are afected by major changes in       the network.In optimizing of-grid system with a battery bank, the HOMER tool usually supports the confguration of having a battery bank because it uses the lifetime of the battery bank which is far from what happens in practical applications.Tis is the reason why results obtained from a simulation tool, with often ideal considerations, need to be properly interpreted from a practical perspective.Tis weakness of the choice of system suggested by HOMER is refected in the variation of microhydropower output and the LCOE, as shown in Figure 16.It shows how the LCOE steadily drops as the hydropower input increases, an indication that the microhydropower is capable of providing power at one of the lowest costs for of-grid applications in Cameroon.

Journal of Electrical and Computer Engineering
Te battery capacity required in the system was monitored while the hydropower output was increasing, and it was observed that the battery size dropped considerably with rising hydropower generation, as seen in Figure 17.Te fgure shows a drastic drop in the battery capacity as the hydropower output is increased.It implies that the battery bank can be completely eliminated with the addition of more hydropower capacity.Te battery plates undergo considerable stress that helps reduce their expected lifetime.Te addition of more batteries in the system leads to high O & M costs and having to replace the battery over two times before the end of the project.Tese challenges make the use of this confguration unfavorable for rural electrifcation.
Te optimal combination of the hybrid system is the 32.2 kW microhydro and the 3 kW solar PV, without a battery bank.Te HOMER Pro simulation intuitively supports the option based on the battery autonomy of less than 2 hours (1.96 hours) obtained after the system optimization.A huge investment in adding a battery system with an autonomy of less than two hours is a reckless economic decision especially for an of-grid system targeting rural areas.Besides, eliminating the battery bank helps to avoid the deep and extended battery discharges which signifcantly reduce the lifespan of the battery.Te selection of this confguration considers the practical and operational resilience of hydro systems which deliver fairly stable power supply to the base load at a relatively lower LCOE and less failure rates.Small-scale hydroelectric plants can also provide fexibility to support solar PV systems [43].Te optimization saw a steady solar PV capacity with rising hydropower output, as seen in Figure 18.
Te sensitivity analysis shows a stable solar PV output, a decreasing size of the battery bank and LCOE while the hydropower is increasing.With the abundance of microhydropower resources in Cameroon, this option will help to provide cheap electricity to low-income earners in rural communities.However, the system's reliability depends on a broad study of the river fow rate of the facility in order to determine the seasonal variation and fow rates.Terefore, it is advisable to add hydropower generation to storage capacity.Tough the use of energy storage will help to stabilize the intermittent solar PV in providing energy on demand, the cost of frequent battery replacement has been a major obstacle over the years.Te optimum system combination depends on the load profle, and hence, studying the power demand profle is vital in matching demand and supply of electricity.It should be noted that the LCOE (0.0453 $/kWh) for the optimum system proposed by the HOMER simulation is far less than the grid parity in Cameroon for residential customers (60 XAF/kWh ≈ 0.07 $/kWh).Tis is so because the electricity tarif has been subsidized by the government and any economic assessment that fails to consider this aspect will yield a deceptive economic decision.However, a further increase in hydropower capacity is capable of further reducing the LCOE as well as the battery capacity.
Meanwhile, hydropower will greatly contribute to carbon reductions for future decades [44].While wind and solar installations have equally grown recently, the most-used RE resource for power generation globally is currently hydropower.Hydroelectricity will continue to play a unique role in  modern power grids due to its economic viability [45].Te deployment of small-scale hydroelectric technologies for rural electrifcation is cost-efective and has low environmental impacts.Another important driving force in hydroelectric development is their role in pumped storage where they facilitate the integration of intermittent wind and solar PV systems [6].Terefore, it is recommended that the government promotes, the use of the huge hydropower potentials, ensuring the production of base power in of-grid communities from hydro, which will help provide the needed fexibility for the subsequent integration of wind and solar in the network.
Cameroon has an estimated large hydropower potential of 23 GW and a potential for small hydro of about 970 MW [46] distributed across the country.Tis represents an indisputable asset for electrifying remote areas in Cameroon.Tere is also a useable potential of about 34 GWh for pumped hydropower in Cameroon which has less environmental impact [47].Nonetheless, it remains under-exploited with large hydro having an exploitation rate of less than 5%, 0% for pumpedhydro and <0.1% for small-hydro.Hybridizing these small hydro-based renewables with other sources can contribute in stabilizing the transmission network in Cameroon.Tere are promising prospects for small hydro in Cameroon especially with the backing of the HYPOSO (hydropower solutions) framework [48], whose aim is to increase the renewable energy share and rural electricity access through sustainable hydropower solutions within fve countries including Cameroon.Pumped-hydro storage plants, because of their mode of operation, would signifcantly contribute to Cameroon's energy policy in that they would facilitate the integration of variable energy sources and improve on the required fexibility to regulate possible grid congestion.Te government established the Vision 2035 as the nation's expansion blueprint.Te objective of the vision is to transform Cameroon into an industrialized, middle-income country with a guaranteed high living standards for Cameroonians by 2035, and clean energy supply has been identifed as a pillar in meeting this goal.In line with this strategic vision, Cameroon has equally adopted the UN SE4ALL (Sustainable Energy for All) program.
Tis study shows how small-hydroelectric installations can cost-efectively electrify rural communities and opines that the government should facilitate an institutional framework that does not emphasize only on large-scale hydroelectric generation but also on small-scale facilities which are known for their less environmental and social impacts.Te pumped-storage hydro can be used to replace the battery storage and hence evade the high cost imposed by a battery.Tis will help to intervene during peak-load periods and store power during periods of excess generation.Interestingly, the technical potential in Cameroon is sufcient to adequately shape the institutional framework.

System Validation with GA.
To validate the results obtained from HOMER Pro, the optimization was done using GA following the procedure mentioned in Section 2.7 above.System optimization of LCOE, LPSP, and NPC was executed using GA developed in the MATLAB environment with an HP ProBook workstation equipped with two 2.50 GHz Intel Core CPUs and 4 GB of RAM.
Te GA approach converged into an optimal solution at the 10 th iteration, as seen in Figure 19.GA is stronger at exploring the global search space than HOMER Pro, giving it the ability to perform better at locating the global optimum.It implies that the ftness landscape of this optimization problem can be better solved using GA, as it can quickly locate an optimal solution.
Te optimum system size of GA showed the least LCOE with the proposed capacities of 3 kW solar PV, 34.56 kW hydropower, and no battery storage.Te NPC, LPSP, and LCOE obtained by GA were, respectively, $86,990.94,0.99%, and 0.0344 $/kWh.Te LPSP of 0.99% obtained in the GA showed that the proposed hybrid RE system respected the LPSP condition (LPSP < 5%), implying that the system is reliable.
Comparing the results from GA and HOMER Pro, GA gave a lesser LCOE of 0.0344 $/kWh than HOMER Pro (0.0453 $/kWh).However, the LCOE obtained from the two approaches is acceptably satisfactory especially for rural electrifcation where the benefciaries are often low-income earners.Similarly, the NPC obtained from the GA method ($86,990.94)was less than that obtained using the HOMER Pro ($90,469.16)approach.Te lower LCOE and NPC values of GA can be explained by its sensitivity to minimize or completely ignore components of the system that increase system cost, as seen in the optimal confguration that has no battery storage.Tis supports the fact that stochastic methods are more realistic, economically viable, and accurately predict system operation than deterministic methods.
A summary of the results from the GA and HOMER Pro are presented in Table 9. Te results show that the GA approach is more cost-efective compared to HOMER Pro.Te LCOE of GA was 0.0344 $/kWh while that of the HOMER Pro simulation was 0.0453 $/kWh.Also, the GA simulation had more hydropower capacity than the HOMER Pro simulation.Te GA's more orientation towards hydropower generation is due to the cost-competitive nature of hydroelectric plants over solar PV and battery storage.From Table 9, it is observed that GA gave zero battery capacity, and it is explained by the high cost of purchasing and replacing batteries within the project life.16 is a curve response on the sensitivity of the system's LCOE to the variation in hydropower capacity of the optimum confguration system.According to the fgure, the LCOE of the optimal system seems to respond directly to variation in the hydropower capacity, as seen in the steepness of the curve.Tis implies that sufcient resources should be allocated for the accurate mapping of microhydroelectric sites in Cameroon.

Discussion of Results. Te plot in Figure
Considering the results obtained from this study and comparing them with similar studies in Cameroon and beyond, we benchmark our fndings with the results

Journal of Electrical and Computer Engineering
presented by [16] where they used the particle swarm optimization (PSO) to design a hybrid of-grid power system in Cameroon.Teir study found the battery-PV-diesel generator (DG) as the optimum confguration at an LCOE of 0.132 $/kWh which is far more than the amount obtained in our study.Tis puts the afordability of this system into question and casts doubt on whether this system can be sustainably managed by the benefciaries who are mostly low-income earners.Still in Cameroon, the fndings of [18] on the optimum microhydro/DG/PV/battery architecture using the HOMER software did not tally with those obtained from our study, as the LCOE for their study was 0.443 $/ kWh.It is evident that the addition of a DG as part of the optimal system not only increases the operation cost but equally damages the environment, and this justifes the diference between the LCOE obtained in their studies and that gotten from this study.Te fndings from our research agree with those of [17] where the hydro-PV was designed for a rural community in Cameroon.Te scholars found an optimum LCOE of 0.06192 $/kWh which is closer to the value obtained in our study.
Comparing with the fndings by [49], we equally observed that the biogas-PV-biomass-wind-fuel cell-battery system did not agree with the results of our study.Teir LCOE of 0.214 $/kWh was, however, higher when gauged with the outcome of our study.Judging the results of our studies with that of [50] where GA was used on a rural power system in India, the optimum solar-biogas-biomasswind-fuel cell-battery system disagreed with the fndings of our studies.Unlike our study with a low LCOE, their study produced electricity at an LCOE of 0.163 $/kWh.Similar studies in Nigeria by [51] using the same method presented an optimal solar-wind-battery-DG system with an LCOE of 0.25 $/kWh which is high when compared to the LCOE of the optimal system in our study.Judging our studies with fndings from [52] using HOMER where the PV-microhydro-battery combination was selected as the optimal system to power an of-grid community in Ethiopia, their results were in harmony with those obtained from our study.Te LCOE obtained in their study was 0.044 $/kWh as the system was mainly powered by hydroelectricity.
A glaring observation, which is signifcant to note, is that while the DG forms part of the major component in the optimal systems of the research works [16,18,20,51], it is absent in the optimal confguration of our study.Tis has considerably afected the LCOEs of these systems, as fuel prices and operation cost are likely to afect the economic viability of the systems.Te possible justifcations for these noteworthy diferences are as follows: (i) Variation in resource availability infuences the output.Tere are a few hydro-based hybrid systems available in the literature.Te year 2009 witnessed the construction of the world's frst 10 MW hydro-solar power plant in Yushu, China [53].Six years later, a larger hydro-solar PV power plant was constructed in Qinghai, China, with an overall solar capacity of 850 MW [54].Although hydroelectricity signifcantly contributed to meeting the peak load in our study, the overall outlook seems to suggest that solar PV technology is ideal, as we observe a stable 3 kW solar capacity in Figure 18.Tis implies that just like microhydro water fow rate data, substantial investment is equally needed to establish an efective solar radiation data center in Cameroon.Te system's viability can also be improved by providing tax cushions on RE components.Tis will signifcantly reduce the initial capital cost and hence, minimize the LCOE and NPC.

Conclusion
Tis paper presents the results of the optimization of a hybrid solar PV-micro hydro energy system for the electrifcation of a remote community in Cameroon.Te proposed system was simulated using GA and HOMER Pro with inputs such as the stream fow rate, the solar radiation, and the cost of system components.Te analysis was compared with the grid extension option to determine whether the hybrid of-grid option was competitive, and the break-even grid distance was determined.Te system's life-cycle cost was conducted for over 25 years.First, HOMER was used to optimize the system, and the results of the HOMER simulation revealed that the solar/hydro/battery system can meet the village loads with an optimal size of 32.2 kW microhydro, 3 kW solar PV, 2 units of generic 260 Ah lead battery, and 21.63 kW converter.Tis option represents an LCOE of $0.0453/kWh and an NPC of $90,469.16.Furthermore, the GA was simulated with MATLAB coding, and it gave an NPC, LCOE, and LPSP of respectively $86,990.94,0.0344 $/kWh, and 0.99%.Te optimal system confguration obtained during the GA approach was 34.56 kW hydropower capacity, 3 kW solar PV, and zero battery storage.When the GA and the HOMER simulations were compared, the GA method was more cost-efective than the HOMER method with the least LCOE and NPC.All the sources used in the system were renewable, and hence, the proposed system was environmentally friendly.With the increasing global advocacy for sustainable development goal (SDG) 7, this study is in line with the tenet of afordable and clean energy.Again, there is no general optimal solution for hybrid renewable energy systems due to multiple constraints.Some in-depth technical details need to be carried out by the modeler to make fnal design decisions, and the best hybrid system depends on the customer's consumption profle.A limitation of this study is that the load profle was based on estimates which are likely to deviate from reality if the system is to be deployed in real life.Hence, there is a need to conduct a thorough load demand assessment in the community before the implementation of the hybrid system.Te optimum operational reliability of a hybrid system including hydro in the mix is dependent on extensive analysis of river fow rates to ascertain the season of possible fow variations.Te fow data used in this study were scaled from data obtained from a neighboring river, and the deployment of this system in the community will require analysis of the river fow in the community.Also, demand response is essential in microgrid design due to uncertainties in supply and to maintain operational reliability when energy production is less than demand.If reserved power is needed to meet short-term power shortages, an extra expenditure needs to be considered for the suitable reserve with a pondage that will provide auxiliary power supply to complement supply during seasons of low infows or low solar radiation and minimize excess energy production.
Tis study demonstrates the use of a hybrid renewable energy system to meet the electricity needs of the Munkep community at a cost that is far below the unsubsidized utility tarif of 80 CFAF/kWh ($0.12/kWh) in Cameroon.Te study proposes a solution to meet the electricity needs of the village.Te viable solution recommended by this study is the installation of a 32.2 kW hydropower capacity of 3.2 m height at an average fow of 1.5 m 3 /s and a 3 kW solar PV system without a battery network.Tese fndings will help stimulate policy on renewable energy utilization, especially incentives on the acquisition of PV and hydropower systems by communities.However, future studies can explore the use of cascaded hydropower turbines within the same river corridor to improve overall system efciency as well as possibly integrate another energy resource to improve energy production in the village.Power produced by the hydro system P Hydro :

Nomenclature
Total generated hydroelectric power P Hydro_Max : Hydro turbine's maximum power P load : Total system load P Peak : Peak solar power capacity P PV : Total generated PV power P out_pv : Output power of the PV system P PV_rated : Solar panel rated power P R_Con : Converter

Figure 7 :
Figure 7: Power management of the hybrid system.
y+1 l,j ) and determine the best ft chromosome b (X y+1 l,j is the decimal representation of X y+1 l,j,b ) Step 9: If F y+1 b � F y b1 then b � b1 Step 10: If y < max_iteration, then y � y + 1; and go to step 5 and continue henceforth Step 11: Return X y+1 j,b which is the optimum solution.ALGORITHM: Genetic algorithm.

Figure 8 :
Figure 8: Summary of system cost.

Figure 11 :
Figure 11: Power output of the solar PV system.

Figure 14 :
Figure 14: Hybrid system input power supplied to charge the battery and battery state of charge.

Figure 15 :Figure 17 :Figure 18 :Figure 16 :
Figure 15: Te assessment of the hybrid system and the existing grid.

Figure 19 :
Figure 19: Convergence curve of the GA simulation.

Table 1 :
A summary of studies on energy optimization.

Table 2 :
Boundary limits of variables.

Table 3 :
Specifcations of the hydro system.Journal of Electrical and Computer Engineering should be supplied whenever required.Since most of the residents in the village are farmers and the primary loads are lighting loads, the peak load appears in the evening from 18: 00-21:00.Te sum total of the daily energy consumption of the community is approximately 431.32 kWh.Table

Table 5 :
Cost specifcations for the design.

Table 7 :
Data for solar PV production.

Table 8 :
Output of the microhydro system.

Table 9 :
Comparative analysis of HOMER Pro and GA simulation.