Control of the Variable-Speed Pumped Storage Unit-Wind Integrated System

-e integration of variable-speed pumped storage unit (VS-PSU) guarantees an efficient peak regulation and frequency modulation of the power grid. -e present research analyzes the active power flow of the VS-PSU under synchronous, subsynchronous, and supersynchronous speed in both generation and pumpingmodes.-e control strategy of the VS-PSU is realized by the dq-axis vector control method. Furthermore, the control of the VS-PSU integrated with wind power has been conducted using DIgSILENTplatformwith the VS-PSU of 300 kW capacity. Results show that the fluctuation of the power output of the wind power plant can be reduced effectively. -e safe, economical, and stable operation of power system integrated with wind power can be achieved by the significant contribution of the VS-PSU.


Introduction
e intensified integration of intermittent renewable energy sources such as wind, tidal, and solar power puts higher demands to the grid frequency control [1][2][3]. e refined frequency control approach is urgently desired in power network operation [3]. e pumped hydro storage (PHS) is known as the most reliable way for realization of peak load regulation, frequency modulation, and phase modulation, emergency reserve [4][5][6][7][8][9]. e traditional power generatormotor operates in the constant speed and frequency mode so that the pump-turbine operating condition is determined by the water head and load. e lack of power regulating the ability of the traditional constant-speed pumped storage units under pumping mode causes a significant impact on the absorption level of new energy in the regional power grid [10]. e variable-speed pumped storage unit (VS-PSU) responds faster under generation mode and adjusts the grid power under pumping mode more flexibly [10,11]. For PHS, the development of variable-speed operation was firstly reported in Japan in the 1990s [12], and results showed that the transient response characteristics were quite satisfactory.
Up to now, Japan and Europe possess the largest installed capacity of VS-PSU plants in the world [13] and have carried out in-depth work in the research and application of VS-PSU [14][15][16], while in China, the growing tendency for the development of the PHS [17] indicates the tremendous potential to integrate the variable-speed technology in the near future.
PHS has the ability of spatial-temporal translation of energy. As an auxiliary peak-regulating power source for traditional power units, variable-speed pumped storage power station is of great significance to relieve the peakregulating pressure of power grid [18]. e active power is controlled by adjusting the rotor speed especially during the pumping mode [19][20][21]. A doubly fed induction machinebased variable-speed pumped storage (VSPS) system was established to investigate the performances in generating mode based on a comparison of phasor model and detailed model simulations [22]. e reactive/active power responses in a very short time for voltage and frequency control enables more dynamic tracking of the load variation because the power of the pump-turbine is proportional to the third power of the unit speed [21,23,24]. e variable-speed pumped storage power generator can operate within a certain speed range according to the change of water head to meet the optimal unit speed. us, cavitation and sediment wear of turbine blades can be reduced and the pump-turbine adapts to a wider head variation [18,25,26]. Despite all the advantages in installation of the VS-PSU, the economic and efficiency analysis is significant for practical industrial application. e economic benefits of converting an existing fixed-speed pumped storage hydropower plant to adjustable speed were estimated and they concluded that the final revenue is increased by 58% [27]. Filipe et al. [28] presented an architecture of the optimized bidding strategy for VS-PSU participated power plant. Despite the various researches on the VS-PSU, there are still some problems to be solved in the aspects of participation of VS-PSU in the grid security and stability control strategy, economic dispatch, and the coordination control strategy with new energy. e present research analyzes power flow of the VS-PSU under both generation and pumping modes to provide the principle of VS-PSU integration. e mathematical models of the VS-PSU have been derived for the realization of doubly fed induction machine (DFIM) power control. Studies on the coordinated operation of the VS-PSU and wind power have been conducted by a systematic simulation. Two schemes are proposed to demonstrate the coordinated dispatch between VS-PSU and wind power.

Operation Principle of the Variable-Speed
Pumped Storage Unit (VS-PSU)

Active Power Flow for the VS-PSU.
e PHS power station operates under two main operating conditions: pumping and generation mode, which are used to regulate the peak and trough periods of power consumption, respectively. e stator of the doubly fed induction machine (DFIM) is connected to the grid, and the rotor adopts the three-phase symmetrical excitation winding. e excitation is provided by the frequency inverter with arbitrary adjustable amplitude, frequency, phase, and phase sequence. When the rotor windings of DFIM are fed with symmetrical alternating current, the rotation of the magnetic field relative to the rotor will be generated in the air gap with a speed of Nr.
e relationship between the speed and the current frequency of the inverter is as follows: in which N r , f 2 , and p represent the rotation speed of the magnetic field relative to rotor, the current frequency of the rotor, and the pole number of DFIM, respectively. In order to achieve stable electromechanical energy conversion, the rotating magnetic fields of the stator and rotor must remain relatively static.
in which N 1 and N 2 represent rotor mechanical speed and the rotation speed of the magnetic field relative to stator. e positive or negative N r depends on the direction of N 1 . When N 1 changes, N r is controlled by adjusting the rotor current frequency to maintain the speed balance. According to the variation of the rotor speed, the operation conditions of the DFIM can further be divided into three modes, namely synchronous, subsynchronous, and supersynchronous operation mode. In the synchronous operation mode, the unit outputs active power to the grid and the inverter provides DC excitation to the rotor winding under generation, whereas the grid feeds active power to the unit and the inverter provides DC excitation to the rotor winding under pumping mode. e active power flow during subsynchronous and supersynchronous operation is given in Figures 1 and 2. In the subsynchronous operation mode, the unit outputs active power to the grid, and the grid feeds to the rotor winding through the inverter under the power generation condition (see Figure 1(a)), whereas the grid feeds active power to the unit, and the rotor winding outputs active power to the grid through the inverter under the pumping condition (see Figure 1(b)), while, in supersynchronous operation mode, the unit outputs active power to the power grid, and the rotor winding feeds it to the grid through the converter under the power generation condition (see Figure 2(a)), whereas the power grid feeds it to the generator, and the grid feeds active power to the rotor winding through the converter under the pumping condition (see Figure 2(b)).
e VS-PSU is excited through tailoring the current (or voltage) of slip frequency in the rotor of the DFIM. e constant frequency and constant voltage output of the stator are realized by adjusting the amplitude, frequency, and phase of excitation voltage. e rotor of the VS-PSU is excited by two "back-to-back" voltage-mode PWM converters which play a significant role in the electrical control system. e two-way flow of energy can thus be ensured with the rotor excitation frequency converter. Additionally, the voltage frequency, active power (generator-motor speed), and reactive power of the stator can be controlled by the realization of continuous adjustment of the amplitude, frequency, and phase of the output current. e output frequency range will meet the requirements of the DFIM including the speed regulation in a range of 90% to 110% synchronous speed and slip frequency adjustment in a range of ± 10% synchronous speed.

Control Strategy of VS-PSU.
e target control object of the two PWM converters is a DFIM. Because of the magnetic coupling in the circuit of the DFIM, the mathematical model of the DFIM in the three-phase coordinate system is nonlinear and time-varying high order system. e general control diagram of the DFIM is designed in Figure 3, and detailed process has been provided in the following. e dq-axis vector control technology is adopted to achieve decoupling control.  Mathematical Problems in Engineering e variables referred above (and below) have been summarized in Nomenclature section (presented at the beginning of the paper), while full voltage equation can be derived as follows: e torque and motion equations is as follows: T e � n p L m i qs i dr − i ds i qr , Generally, the vector control system of the asynchronous motor takes rotor flux as a reference, and then the direction of rotor flux is determined as d axis of the synchronous coordinate system. However, if the doubly fed system with variable-speed and constant frequency is still oriented by rotor flux or air gap flux, the calculation of stator active power and reactive power will be complex, which will affect the real-time processing of the control system. erefore, when the stator flux is oriented on axis d, the following equations can be obtained: Since the stator side of the DFIM always runs at a fixed frequency, 50 Hz is considered for this research. In this case, the voltage drop of stator resistance is much smaller than the inverse potential of the motor. erefore, the stator winding resistance of the motor can usually be ignored, and the stator voltage equation can be simplified as Corresponding torque equation is e active and reactive power of the rotor side can be obtained as It can be derived from equations (9) and (10) that the active power and reactive power of the generator stator have a linear relationship with the torque component and excitation component of the rotor current, respectively. e active power and reactive power of stator can be independently controlled by adjusting the two current components, and, thus, the power decoupling control is realized in the stator side.
Similarly, the rotor voltage equation can be obtained: Let and we can obtain where the transfer functions of u dr ′ and i dr are linear. As can be seen from Figure 4, we can obtain u dr ′ from i dr after the PI regulation. u dr * can be calculated by the full compensation of voltage based on i dr (Figure 4). u qr * is obtained from the closed-loop of rotor current in q axial from Figure 5, which can be expressed as 4

Mathematical Problems in Engineering
According to the characteristics of the reactive power on the stator side, the total copper consumption of the system is minimized in the generating process of the DFIM. e copper loss equation of the DFIM is Transforming equation (13) into a function of stator current in d-axis, And let dP Cu where e preset reactive power is given according to the system power factor requirements. Combining equations (14) and (15), the preset reactive current can be calculated. Stator flux linkage is the key to rotation transformation in vector control technology. In the static coordinate system, the stator voltage equation ignoring the stator resistance is given as As can be seen from the voltage equation in the static coordinate system, the stator voltage synthesis vector is 90°a head of the stator flux vector. e observed three-phase voltage of stator is transformed by 3/2, and the stator voltages u α , u β of the stationary coordinate system are obtained. en let θ be the stator voltage vector position, and stator flux vector position can be expressed as θ 1 � θ − 90°to locate the position of the d axis of the coordinate system. e rotor position θ r can be measured directly through the code disc. e position of d axis refers to the rotor position being θ s � θ 1 − θ r . Assuming that the rotor voltage in d-q axis is given, the three-phase voltage on the rotor side u * ar , u * br , u * cr can be obtained through rotation transformation and 2/3 transformation (see Figure 6). e power control scheme can thus be summarized as shown in Figure 3, from which the decoupling control of the active and reactive power of the variable-speed and constant frequency DFIM system is realized.

VS-PSU for Stable Wind Power
Generation. e great fluctuation exists in wind power since the output of the wind turbine changes with the variation of the wind speed. In a short time-scale, the wind power cannot be kept steady by the wind turbine generator due to its small inertia. e fast fluctuation of wind power will inevitably affect the power flow, voltage, and frequency of the regional power grid. Typical characteristics of randomness and unpredictability of wind power plants are recorded in Figure 7. As can be seen in Figure 8, the active power of VS-PSU increases nonlinearly with the increase of wind power, which indicates that the fluctuation of wind speed will lead to the frequent fluctuation of active power at low wind speed and cause the frequent change of network power flow eventually. Meanwhile, the VS-PSU will not be connected to the grid for power generation when the wind speed is too high (safe consideration) or too low.

Wind Turbine Model.
e relationship between the mechanical energy, Pw, output by the wind turbine, and the wind speed, Vw, corresponding to the captured wind energy is presented in the following: in which the power coefficient C p is the function of tip speed ratio ω s and pitch angle sω s � ω s − ω r : e mechanical torque output of the wind turbine T w can be expressed as

Mathematical Problems in Engineering
Maximum mechanical power can be obtained by adjusting the pitch angle of a wind turbine according to the alternation of wind speed. C p and P w characteristic curve of a wind turbine is shown in Figures 9 and 10, respectively. It can be seen from Figure 9 that there is only one value of ψ s that enables C p to achieve its maximum when the pitch angle is fixed, and the corresponding tip velocity ratio is called the optimal tip velocity ratio of wind turbines.

Control of VS-PSU Integrated System.
e idea of using VS-PSU to control the fluctuation of output of wind power plant is similar to the function of the low-pass filter. erefore, the low-pass filter can be used to filter out the low-frequency components, and then the medium-frequency and high-frequency signals of wind power regulation needed by the VS-PSU can be obtained.
is section is dedicated to present the operation characteristics of the above proposed control strategy based on the DIgSILENT, and the corresponding schematic diagram is provided in Figure 11. e simulation model equipped with a set of 300 MW VS-PSU connected to the local power grid in the region with high permeability of new energy is designed and connected to the 220 kV ac power grid through the step-up transformer. As shown in Figure 12, two control schemes of the VS-PSU integrated with wind power are proposed   according to different input signals. e input signal of realtime or forecasted power is superimposed on the reference power through the restrain fluctuate module. In scheme one, the real-time power output of the wind power plant is considered as an input signal (see Figure 13), P in . Figure 14 shows the active power output of wind turbines obtained from numerical simulation based on different low-pass filtering time constants (T1 � 5 s, T2 � 10 s, T3 � 15 s). Results show that the variation range of the active power output and frequency of the wind turbine in the near region have been effectively reduced, which relieves partial pressure in the power regulation by the conventional unit. Besides, regulating the speed of VS-PSU is faster with increase in low-pass filtering time constants. On the other hand, the output waveform of the controller is delayed compared with the input waveform due to the lag effect of the low-pass filter, which is not conducive to power system dispatching. e wind power plants are generally equipped with wind power prediction system, which can forecast wind power in advance. erefore, scheme two adopts the method based on the predicted wind power data of the power plants as the input signal, P in . Two control schemes are compared in Figure 15 and the negative power output is obtained   Mathematical Problems in Engineering from the perspective of grid side under pumping mode. e power output of the VS-PSU without integration of the wind power is constant (red one) as labeled with no additional control. It can be concluded that the fluctuation of wind power can be effectively suppressed based on the VS-PSU with both the schemes proposed in this study. However, the "delay" effect of the low-pass filter has been effectively compensated based on the predicted power data in the second scheme. It indicates the better effect of scheme two in stabilizing the power output fluctuation of wind energy integration when compared with scheme one. Based on the wind power curve in Figure 7, the frequency responses of the VS-PSU integrated wind power generation system under different filtering time constants (no additional control, T � 15 s, T � 50 s) are given in Figure 16.
e system frequency fluctuation is obviously reduced after the VS-PSU is adopted, and the frequency fluctuation of the system decreased significantly in the case of T � 50 s.

Conclusions
In the present research, the control over the VS-PSU integrated wind power generation system is analyzed primarily using the dq-axis vector control strategy. e operation characteristics of wind power after the integration of VS-PSU is simulated based on DIgSILENT platform considering different filtering time. Results show that the VS-PSU can effectively reduce the regulation pressure of the conventional power unit, especially when taking the predicted power data of the wind power plant as the input signal because of the delay effect of real-time power output. Additionally, the frequency fluctuation of the wind power generation system is obviously reduced after the VS-PSU is adopted, and the frequency stabilization effect is better with the increase of the filter time constant. e coordinated operation of VS-PSU in wind power grid provides more safe and effective regulation approaches for the peak regulation and frequency modulation.

Data Availability
e data used to support the findings of this study are available from the corresponding author upon request.

Conflicts of Interest
e authors declare no conflicts of interest.