The Scientific World Journal

Volume 2014 (2014), Article ID 581724, 6 pages

http://dx.doi.org/10.1155/2014/581724

Research Article

Investigation on Mercury Reemission from Limestone-Gypsum Wet Flue Gas Desulfurization Slurry

Chuanmin Chen, Songtao Liu, Yang Gao, and Yongchao Liu

School of Environmental Science & Engineering, North China Electric Power University, Baoding 071003, China

Received 31 August 2013; Accepted 15 January 2014; Published 4 March 2014

Academic Editors: J. Canario, G.-C. Fang, and F. Scala

Copyright © 2014 Chuanmin Chen et al. This is an open access article distributed under the Creative Commons Attribution License, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.

Abstract.

Secondary atmospheric pollutions may result from wet flue gas desulfurization (WFGD) systems caused by the reduction of Hg²⁺ to Hg⁰ and lead to a damping of the cobenefit mercury removal efficiency by WFGD systems. The experiment on Hg⁰ reemission from limestone-gypsum WFGD slurry was carried out by changing the operating conditions such as the pH, temperature, Cl⁻ concentrations, and oxygen concentrations. The partitioning behavior of mercury in the solid and liquid byproducts was also discussed. The experimental results indicated that the Hg⁰ reemission rate from WFGD slurry increased as the operational temperatures and pH values increased. The Hg⁰ reemission rates decreased as the O₂ concentration of flue gas and Cl⁻ concentration of WFGD slurry increased. The concentrations of O₂ in flue gas have an evident effect on the mercury retention in the solid byproducts. The temperature and Cl⁻ concentration have a slight effect on the mercury partitioning in the byproducts. No evident relation was found between mercury retention in the solid byproducts and the pH. The present findings could be valuable for industrial application of characterizing and optimizing mercury control in wet FGD systems.

1. Introduction

Mercury and its compounds are highly toxic species which have a considerable impact on human health. A large proportion of mercury is emitted to the environment by the burning of coal. This process is responsible for about one-third of anthropogenic mercury emissions [1, 2]. Mercury may be present in flue gas as elemental mercury (Hg⁰) or oxidized mercury (Hg²⁺). It may also be retained in fly ash particles, in which case it is referred to as particle-bound mercury (). Whereas is retained in the electrostatic precipitators or bag filters, both Hg²⁺ and Hg⁰ species from the flue gas are emitted to the atmosphere in power plants without undergoing any postcombustion processes to reduce emissions. In some cases, wet flue gas desulfurization (WFGD) systems installed in coal fired power plants to control SO₂ emissions have been used to decrease mercury emissions [3–7]. In such systems, SO₂ usually reacts with the limestone slurry to produce insoluble gypsum.

Hg²⁺ can be efficiently captured in WFGD by taking advantage of its high solubility in water [3, 5, 8]. However, the elemental mercury is difficult to capture with typical air pollution control devices (APCD) due to its volatility and chemical stability [1]. One strategy which is being explored is the use of a catalyst or oxidant to oxidize elemental mercury in the upstream of WFGD system, and then the oxidized mercury is absorbed by WFGD slurry. However, during the work aimed at enhancing the mercury-removal performance of WFGD systems, investigators discovered that a portion of absorbed oxidized mercury will be reduced to elemental mercury (Hg⁰) in WFGD system and eventually released into flue gas [9–11], and the total mercury removal efficiency was significantly limited. As such, to improve the efficiency, it is necessary to control mercury reemission from WFGD slurry to prevent from reducing the cobenefit of wet scrubber mercury removal.

Studies on elemental mercury reemission in lab- and pilot-scale WFGD systems were reported in recent years. Some researchers indicated that the reduction process presumably occurred via aqueous reduction of Hg²⁺ by sulfite ions. The process was initiated by the formation of unstable intermediate, HgSO₃, which immediately decomposed to aqueous Hg⁰ and eventually reemitted to gas phase [11–13]. The authors also studied the effect of some operational parameters, for example, pH value, concentration of S(IV), temperature, and concentration of Cl⁻ on elemental mercury reemission [10, 14, 15]. Wo et al. [10] indicated that flue gas Hg⁰ reemission across a wet FGD scrubber can be reduced by increasing the initial pH value, concentration of S(IV), or lowering the temperature. But Wu et al. [15] had the opposite conclusion about the effect of pH on the mercury reemission. Their work suggested that Hg⁰ reemission was suppressed by decreasing the pH. They also suggested that there existed a qualitative relationship between the initial oxidation-reduction potential (ORP) values of the slurries and Hg⁰ reemission across the slurries [15]. Some literatures [10, 12] had yet concluded that the Cl⁻ had inhibition effect on the reduction of Hg²⁺, where the formation of ClHg was suggested as the main cause for this inhibition [16].

Furthermore, these parameters not only affect Hg⁰ reemission, but also impact the partitioning behavior of mercury in the solid and liquid byproducts. To better understand the performance of Hg⁰ reemission in the wet FGD system, a sequence of experiments was carried out in order to evaluate the influence of different operational parameters on Hg⁰ reemission efficiency in a bubbling reactor and the partitioning behavior of mercury in the solid and liquid byproducts was also discussed.

2. Experiments and Methods

2.1. Experimental Apparatus

The schematic diagram of a lab-scale wet FGD simulated system is illustrated in Figure 1. The elemental mercury (Hg⁰) reemission and the factors that impact Hg⁰ reemission were investigated by using the simulated scrubber. This system consisted of an oxidized mercury (Hg²⁺) injection system, carrier gas system, scrubbing system, and mercury analyzer system. The scrubbing system was composed of a bubbling reactor, a water bath, and a magnetic stirring system. The Hg²⁺ injection system was a peristaltic pump system, which can deliver the HgCl₂ solution to the bubbling reactor as the source as well as control and adjust its injection rates. The Hg²⁺ solution went directly to the bottom of the flask through a Teflon tube. The carrier gas system included cylinder gases, mass flow controllers (MFCs), and delivery piping, which was made of Teflon tubes. The desired flow rates of the carrier gases were controlled by calibrated MFCs. The reaction solution was stirred under N₂, O₂, and CO₂ atmosphere to remove the produced Hg⁰.

Figure 1: Schematic of the experiment system.

2.2. Experimental Procedure

At the beginning of each test, a slurry with the desired concentration (1% w/w) was prepared and poured into the reactor; the reactor was submerged into the water bath at the desired temperature. The CaSO₄ and CaSO₃ (mixing rate, 90/10) were used to simulate the slurry of the limestone-forced oxidation wet FGD system. The Hg²⁺ injection system was a peristaltic pump system, which can deliver the HgCl₂ solution to the bubbling reactor as the source of Hg²⁺ as well as control and adjust its injection rates. A 50 μg/l Hg²⁺ solution was pumped into the reactor at a rate of 10 mL/h. The initial pH of the solution was controlled through the combined addition of CaCO₃ and H₂SO₄ to the reactor and measured by pH meter. Other chemicals, such as NaCl as the source of Cl⁻, were selectively added to the bubbling reactor. The carrier gas with a flow rate of 1000 mL/min was introduced into the scrubber. The carrier gas came in contact with the slurry through the scrubber. Then, the carrier gas arrived at the mercury analyzer, which initiated the test. When the blank testing values of the mercury concentrations in the carrier gas were stable, the Hg²⁺ solution was injected. Continuous Hg⁰ concentration detection at the outlet of the simulated WFGD reactor was started at this point by a LUMEX RA-915+ Hg analyzer until the steady state was achieved. The mercury content of the solid and aqueous samples generated in the lab-scale tests was also determined by means of LUMEX RA-915+ Hg analyzer. No oxidized mercury was detected through multiple tests because the oxidized mercury dissolved in the slurry. The elemental mercury concentration that was emitted from the slurry was tested to quantify the elemental mercury reemission levels. The mercury concentrations were recorded once per minute. The mercury mass balance for each test was calculated. It is found that the error of the overall mercury mass balance was in the range of 94%–105% for all tests. The range of experimental conditions used for the scrubber slurry and the simulated flue gas is included in Table 1.

Table 1: Experimental conditions.

Parameter
Simulated WFGD slurry
Simulated flue gas

Reagent
90%CaSO₄/10%CaSO₃
—

Initial pH
3–7
—

Temperature (°C)
20–75
20

O₂ (vol.%)
—
0–15

CO₂ (vol.%)
—
12

N₂ (vol.%)
—
As balance

Gas flow rate (mL/min)
—
1000

Hg²⁺ concentration (g/L)
50
—

Hg²⁺ injection rate (mL/h)
10
—

Hg²⁺ concentration at scrubbing system inlet (calculated in gas, g/m³ gas)
—
8.3

Cl⁻ (ppm)
0–5000
—

2.3. Mercury Reemission Efficiency Calculation

In this paper, mercury reemission efficiency () was calculated by the equation listed as follows:

where is the mercury reemission efficiency, is the inlet Hg²⁺ concentrations, and is the outlet Hg⁰ concentration.

3. Results and Discussion

3.1. Effect of the Oxygen Concentration in the Flue Gas on Hg⁰ Reemission

The impact of oxygen concentration in the flue gas on Hg⁰ reemission from the simulated WFGD slurry is shown in Figure 2. The experiments reported in Figure 2 were performed at a pH of 5.5 and a temperature of 55°C. The experimental range of oxygen concentration used in these experiments was from 0% to 15%. From Figure 2(a), it can be seen that the Hg⁰ reemission rates increase as the oxygen concentration in the flue gas increases. The Hg⁰ concentration in flue gas reached about 6.87 μg/m³ for 0% O₂ at 100 min when Hg⁰ concentration was stable. In contrast, only 2.62 μg/m³ was obtained for 15% O₂. The Hg⁰ reemission reaction mechanism is explained by using the chemical reaction in [15]

(a)

(b)

Figure 2: (a) Effect of the oxygen concentration in the flue gas on Hg⁰ reemission. (b) Relationship between the proportion of mercury retained in the solid and liquid fraction of the slurry and the concentration of oxygen concentration in the flue gas.

The was oxidized into through reaction (3) when the carrier gas that contained O₂ was blown into the scrubber. Thus, the concentration of was decreased, which resulted in a lower Hg⁰ reemission rate:

The mercury partitioning in the byproducts indicates that an increase in mercury retention in the solid fraction occurs at lower concentrations of O₂ in flue gas (Figure 2(b)). This suggests that sulfate ions may be contributing to the formation of a small amount of mercury sulfate which then precipitates with the gypsum particles or decomposes in HgO(s) [14].

3.2. Effect of the Temperature on Hg⁰ Reemission

The tests of Hg⁰ reemission at different temperatures were conducted. The experimental range of temperature used in these experiments was from 20 to 75°C by adjusting the temperature of the water bath. The pH value of the slurry was kept at 5.5. Figure 3(a) shows the elemental mercury concentrations versus the HgCl₂ injection time at four temperature levels. It can be seen that the Hg⁰ reemission rate increases with the temperature of the simulated scrubber. The Hg⁰ concentration in flue gas reached about 4.87 μg/m³ at 75°C at an injection time of 100 min, while it was only 1.29 μg/m³ at 20°C. Figure 3(b) shows that there was a slight decrease in mercury retention in the solid fraction with the temperature rising.

(a)

(b)

Figure 3: (a) Effect of the temperature on Hg⁰ reemission. (b) Relationship between the proportion of mercury retained in the solid and liquid fraction of the slurry and the temperature.

3.3. Effect of the pH on Hg⁰ Reemission

Six tests at different initial pH values (3, 4, 5, 5.5, 6, and 7) were conducted in the simulated scrubber. The temperature of the solution was 55°C. The Hg⁰ concentration curves at different pH values are shown in Figure 4. From Figure 4(a), it can be found that the Hg⁰ reemission rates increase as the pH values increase. The Hg⁰ concentration in flue gas reached about 5.60 μg/m³ for at 100 min. In contrast, only 2.09 μg/m³ was obtained for . Equation (2) was a reversible reaction, according to the principle of chemical reactions, and a counter reaction was performed at a lower pH value, where the concentration of H⁺ was high. Therefore, the Hg⁰ reemission rate decreased in the solution as the pH value decreased. From Figure 4(a), it can be seen that the pH seems to have no effect on the mercury partitioning in the byproducts.

(a)

(b)

Figure 4: (a) Effect of the pH on Hg⁰ reemission. (b) Relationship between the proportion of mercury retained in the solid and liquid fraction of the slurry and the pH.

3.4. Effect of the Cl⁻ Concentration on Hg⁰ Reemission

Figure 5 presents the effect of Cl⁻ concentration on Hg⁰ reemission. The experiments were carried out at the pH value of 5.5 and the temperature of 55°C. It can be seen that Cl⁻ concentration has an evident effect on the Hg⁰ reemission. The Hg⁰ reemission shows that the fastest reaction rate in the simulated desulfurization slurry is without chloride and the Hg⁰ reemission rate decreases with Cl⁻ increasing. From Figure 5 it can be seen that the Hg⁰ concentration in flue gas reached about 4.23 μg/m³ without Cl⁻ at 100 min while only 1.24 μg/m³ with 5000 ppm Cl⁻.

(a)

(b)

Figure 5: (a) Effect of the Cl⁻ concentration on Hg⁰ reemission. (b) Relationship between the proportion of mercury retained in the solid and liquid fraction of the slurry and the Cl⁻.

As is found, the reactions for Hg⁰ emission are as follows: the main pathway is through mercuric-sulfite complexes [11, 13]:

New mercuric-sulfite-chloride complexes and are formed through the following reactions when the chloride is added into the simulated desulfurization solutions:

can decompose to Hg⁰ through the reaction (10). But the decomposition rate of is much slower than HgSO₃ or (reactions (6) and (7)). In addition, is formed reversibly at higher chloride concentration, which does not decompose to Hg⁰ [12, 16]:

From Figure 5(b), it can be seen that the Cl⁻ seems to have a slight effect on the mercury partitioning in the byproducts. The proportion of mercury retained in the solid decreases from 76.85% to 70.31% when the Cl⁻ concentration in the slurry increases from 0 ppm to 5000 ppm.

4. Conclusions

An evaluation of the influence of the operating conditions, which included the pH, temperature, Cl⁻ concentrations, and oxygen concentrations, on Hg⁰ reemission from wet flue gas desulfurization slurry was carried out. The experimental results indicated that the Hg⁰ reemission rate from WFGD slurry increased as the operational temperatures and pH values increased. However, the Hg⁰ reemission rates decreased as the O₂ concentration of flue gas and Cl⁻ concentration of WFGD slurry increased. So the Hg⁰ reemission from WFGD system can be reduced or slowed by decreasing the temperature and pH or by using forced oxidation. The results of mercury partitioning behavior in the solid and liquid byproducts show that mercury retention in the solid fraction increased with the concentrations of O₂ in flue gas decreasing and slightly decreased in mercury retention in the solid fraction with the temperature and Cl⁻ concentration in the slurry rising. And there is no evident relation between mercury retention in the solid byproducts and the pH. The present findings could be valuable for industrial application of characterizing and optimizing mercury control in wet FGD systems.

Conflict of Interests

The authors declare that there is no conflict of interests regarding the publication of this paper.

Acknowledgments

This work was financially supported by the National Natural Science Foundation of China (51076045), Hebei Provincial Natural Science Foundation of China (E2012502043), and Fundamental Research Funds for the Central Universities.

References

R. K. Srivastava, N. Hutson, B. Martin, F. Princiotta, and J. Staudt, “Control of mercury emissions from coal-fired electric utility boilers,” Environmental Science and Technology, vol. 40, no. 5, pp. 1385–1393, 2006.

J. H. Pavlish, E. A. Sondreal, M. D. Mann et al., “Status review of mercury control options for coal-fired power plants,” Fuel Processing Technology, vol. 82, no. 2-3, pp. 89–165, 2003.

R. Ochoa-Gonzalez, P. Córdoba, M. Diaz-Somoano et al., “Differential partitioning and speciation of Hg in wet FGD facilities of two Spanish PCC power plants,” Chemosphere, vol. 85, no. 4, pp. 565–570, 2011.

R. Ochoa-Gonzalez, M. Diaz-Somoano, M. R. Martinez-Tarazona, et al., “The capture of oxidized mercury from simulated desulphurization aqueous solutions,” Journal of Environmental Management, vol. 120, pp. 55–60, 2013.

J. Wang, W. Wang, W. Xu, X. Wang, and S. Zhao, “Mercury removals by existing pollutants control devices of four coal-fired power plants in China,” Journal of Environmental Sciences, vol. 23, no. 11, pp. 1839–1844, 2011.

Y. Wang, Y. Liu, Z. Wu, J. Mo, and B. Cheng, “Experimental study on the absorption behaviors of gas phase bivalent mercury in Ca-based wet flue gas desulfurization slurry system,” Journal of Hazardous Materials, vol. 183, no. 1–3, pp. 902–907, 2010.

A. Stergaršek, M. Horvat, J. Kotnik et al., “The role of flue gas desulphurisation in mercury speciation and distribution in a lignite burning power plant,” Fuel, vol. 87, no. 17-18, pp. 3504–3512, 2008.

T. Tang, J. Xu, R. Lu, J. Wo, and X. Xu, “Enhanced Hg²⁺ removal and Hg⁰ re-emission control from wet fuel gas desulfurization liquors with additives,” Fuel, vol. 89, no. 12, pp. 3613–3617, 2010.

N. Omine, C. E. Romero, H. Kikkawa, S. Wu, and S. Eswaran, “Study of elemental mercury re-emission in a simulated wet scrubber,” Fuel, vol. 91, no. 1, pp. 93–101, 2012.

J. Wo, M. Zhang, X. Cheng, X. Zhong, J. Xu, and X. Xu, “Hg²⁺ reduction and re-emission from simulated wet flue gas desulfurization liquors,” Journal of Hazardous Materials, vol. 172, no. 2-3, pp. 1106–1110, 2009.

J. C. Chang and S. B. Ghorishi, “Simulation and evaluation of elemental mercury concentration increase in flue gas across a wet scrubber,” Environmental Science & Technology, vol. 37, no. 24, pp. 5763–5766, 2003.

Y. Liu, Y. Wang, Z. Wu, S. Zhou, and H. Wang, “A mechanism study of chloride and sulfate effects on Hg²⁺ reduction in sulfite solution,” Fuel, vol. 90, no. 7, pp. 2501–2507, 2011.

L. van Loon, E. Mader, and S. L. Scott, “Reduction of the aqueous mercuric ion by sulfite: UV spectrum of HgSO₃ and its intramolecular redox reaction,” Journal of Physical Chemistry A, vol. 104, no. 8, pp. 1621–1626, 2000.

R. Ochoa-gonzalez, M. Diaz-somoano, M. R. Martinez-tarazona, et al., “Control of Hg⁰ re-emission from gypsum slurries by means of additives in typical wet scrubber conditions,” Fuel, vol. 105, pp. 112–118, 2013.

C. L. Wu, Y. Cao, C. C. He, Z.-B. Dong, and W.-P. Pan, “Study of elemental mercury re-emission through a lab-scale simulated scrubber,” Fuel, vol. 89, no. 8, pp. 2072–2080, 2010.

D. W. Deberry, G. M. Blythe, S. Pletcher, et al., Bench-Scale Kinetics Study of Mercury Reactions in FGD Liquors, Air and Waste Management Association, Baltimore, Md, USA, 2006.